# ID: 6111

## Title: The September Sweet Spot: Do This In August To Beat The October Commercial HVAC Maintenance Rush

## Type: blog_post

## Author: Ben Reed

## Publish Date: 2025-08-07T14:34:35

## Word Count: 1088

## Categories: HVAC Maintenance, Commercial Systems, Heating Systems

## Tags: carbon monoxide safety, fall heating maintenance, furnace inspection, heat exchanger inspection, HVAC business planning, HVAC maintenance, HVAC revenue optimization, maintenance agreements, preventive maintenance, seasonal HVAC planning, September scheduling, small business HVAC, technician burnout, technician training, winter emergency prevention, work-life balance

## Permalink: https://hvacknowitall.com/blog/the-september-sweet-spot-commercial-hvac-maintenance

## Description:
Key Takaways

- September maintenance prevents common winter HVAC failures including circulation pump seizures, heat exchanger cracks, and ignition problems that typically manifest in December/January
- Scheduling maintenance in September offers technical advantages (equipment accessibility, thorough inspections) and business benefits (increased profit margins, efficient routing)
- Customers avoid the October/November maintenance bottleneck when wait times stretch to 2 weeks and parts availability becomes limited
- Implementing September maintenance programs reduces technician burnout by spreading workload evenly throughout the year, reducing 60+ hour winter weeks

```
Working in residential HVAC? Read this complimentary article!
```

## The October Problem: Why Waiting Costs Everyone

Once the first cold snap hits in October, the phone starts ringing with heating emergency calls. Suddenly, everyone needs their heating systems operational *yesterday*. This creates a cascade of familiar challenges:

- Building managers discover major heat exchanger issues when they need heat most
- Parts availability plummets as suppliers can’t keep up with the surge in demand
- Emergency service rates kick in, costing clients 50-100% more than scheduled maintenance
- Technician workloads become unmanageable, creating a work-life imbalance during the heating transition

When these problems are discovered late, the consequences create legitimate safety hazards.

## The September Sweet Spot: Why It’s Ideal Timing

September offers unique advantages that make it the perfect time for commercial heating maintenance:

- Moderate weather allows system shutdowns without disrupting building occupants
- Technicians are transitioning from peak AC season to a more balanced workload
- Parts suppliers still have healthy inventory before the October/November depletion
- Building managers typically have fiscal year budget available for necessary repairs

This timing sweet spot creates a win-win situation for both service providers and clients. Technicians can work more methodically without emergency pressure, while building managers avoid the premium costs and disruption of mid-winter failures.

## The Business Case for September Maintenance in Commercial Buildings

Well-planned maintenance is essential for commercial buildings to keep critical infrastructure running smoothly and generating ROI for all stakeholders:

- Preventive maintenance delivers a 545% return on investment compared to reactive emergency repairs
- Buildings with proper heating maintenance experience 40-60% fewer winter heating failures
- Emergency repairs during peak heating season cost 50-100% more than scheduled maintenance
- Well-maintained commercial heating equipment lasts 14+ years versus just 9 years for neglected systems

As an HVAC tech, if you’re aware of the impacts to a business and can present this data effectively, you can position yourself as business partners rather than just service providers.

## Critical Commercial Systems That Can’t Wait

### Rooftop Units (RTUs)

RTUs demand specialized attention before heating season begins. This includes:

- Heat exchanger inspection using proper techniques to identify hairline cracks and corrosion
- Thorough burner inspection and cleaning to prevent carbon monoxide issues
- Control system recalibration to ensure proper heating sequences and prevent short cycling

Our detailed guide on [Gas Manifold Pressure Testing](https://www.hvacknowitall.com/blogs/blog/231593-hvac-tip----checking-manifold-gas-pressure) provides step-by-step procedures for ensuring your gas-fired RTUs operate safely and efficiently. This critical test often reveals issues that can be addressed easily in September but become emergency calls by November.

### Boiler Systems

Commercial boilers benefit tremendously from September attention:

- Comprehensive combustion analysis to optimize efficiency before the heating season demands
- Safety control verification to identify potential failure points before they become critical
- Water treatment analysis to prevent mid-winter scale buildup and efficiency losses

As covered in our [Seasonal Changeover Guide](https://hvacknowitall.com/blog/changeover-from-cooling-to-heating), proper glycol concentration verification is essential for hydronic systems to ensure freeze protection during the coming winter months. This simple step performed in September prevents catastrophic pipe failures when temperatures plummet.

### Building Automation Systems

[The brain of your commercial building](https://hvacknowitall.com/blog/bms-basics-hvac-technician-guide) requires specialized attention:

- Schedule updates to optimize heating mode operation and prevent energy waste
- Sensor calibration verification to ensure accurate temperature readings and prevent comfort complaints
- Control sequence testing to identify programming issues before occupants require consistent heating

## Immediate Action Plan: What to Do In Early August

1. **Create a targeted outreach strategy**: Develop a list of commercial clients prioritizing those with critical operations or aging equipment.
2. **Develop a streamlined inspection checklist**: Create a September-specific checklist that focuses on heating components most likely to fail during the first cold snap.
3. **Implement a prioritization system**: Schedule the most critical systems first—hospitals, elder care facilities, schools, and buildings with previous heating issues.
4. **Set up a parts inventory plan**: Coordinate with suppliers to ensure availability of commonly needed heating components.

When discussing flame rectification systems, reference our guide on [Why Flame Rod Failures Happen and How To Prevent Them](https://hvacknowitall.com/blog/why-flame-rod-failures-happen-and-how-to-prevent-them), which provides technical insights that can help you identify potential issues before they cause no-heat conditions.

## Long-Term Strategy: Building a September Maintenance Program

To truly differentiate your commercial service, develop a systematic September maintenance program:

- Create an annual reminder system to book commercial clients specifically for September heating checks
- Develop educational materials explaining the September advantage for building managers
- Implement technician training focused on efficient heating system inspections
- Build performance tracking that documents reduced winter emergency calls after September maintenance

For comprehensive maintenance of specialized systems, our guide on [Make Up Air Units](https://hvacknowitall.com/blog/make-up-air-units-explained) provides detailed procedures for both direct-fired and indirect-fired systems, which are often overlooked during standard maintenance but critical to proper building operation.

## Communication Strategies for Building Managers

The success of September maintenance often relies on effective communication with building managers:

- Frame conversations around budget protection rather than maintenance costs
- Address the “it’s still hot outside” objection with data on equipment lead times
- Present tenant satisfaction benefits of avoiding mid-winter heating emergencies
- Provide documentation that helps justify maintenance expenditures to upper management

These conversations build trust and position you as a proactive partner rather than a reactive vendor.

## The September Advantage

Implementing September heating maintenance sets commercial HVAC technicians apart as true professionals in an industry often driven by reactive service. This approach delivers multiple benefits:

- Peace of mind from addressing issues before they become emergencies
- Balanced workload that prevents the October/November service chaos
- Higher client satisfaction and stronger long-term relationships
- Increased revenue through more efficient service delivery

By embracing the September advantage, you position yourself as a strategic asset to your clients rather than just another service provider.

```
Important Note: As our guide on Carbon Monoxide Testing emphasizes, safety must remain the top priority in all heating maintenance. September inspections provide the time needed to thoroughly evaluate combustion safety without the pressure of freezing occupants or emergency conditions.
```

--------------------------------------------------

# ID: 6104

## Title: The September Sweet Spot: Why Smart Residential Techs Schedule HVAC Maintenance In August

## Type: blog_post

## Author: Ben Reed

## Publish Date: 2025-08-07T13:28:12

## Word Count: 1541

## Categories: HVAC Maintenance, Heating Systems

## Tags: carbon monoxide safety, fall heating maintenance, furnace inspection, heat exchanger inspection, HVAC business planning, HVAC maintenance, HVAC revenue optimization, maintenance agreements, preventive maintenance, seasonal HVAC planning, September scheduling, small business HVAC, technician burnout, technician training, winter emergency prevention, work-life balance

## Permalink: https://hvacknowitall.com/blog/the-september-sweet-residential-spot-hvac-maintenance

## Description:
Key Takeaways

- September maintenance prevents common winter HVAC failures including circulation pump seizures, heat exchanger cracks, and ignition problems that typically manifest in December/January
- Scheduling maintenance in September offers technical advantages (equipment accessibility, thorough inspections) and business benefits (increased profit margins, efficient routing)
- Customers avoid the October/November maintenance bottleneck when wait times stretch to 2 weeks and parts availability becomes limited
- Implementing September maintenance programs reduces technician burnout by spreading workload evenly throughout the year, reducing 60+ hour winter weeks

```
Working in commercial HVAC? Read this complimentary article!
```

## Why Timing Matters for Shoulder Season Maintenance

Are you ready for the October maintenance rush. Probably not.

Data shows October and November rank as the busiest maintenance months for HVAC contractors, creating a bottleneck that leaves customers waiting up to two weeks for service.

By the time most customers think about heating maintenance, it’s already too late. They call when the first cold snap hits, and suddenly everyone wants their furnace checked at once. This creates a scheduling nightmare that forces you to rush through jobs, miss important safety checks, and work overtime that could have been avoided.

[Changing over from cooling to heating](https://hvacknowitall.com/blog/changeover-from-cooling-to-heating) is a process that requires careful inspection and preparation. When systems sit dormant for months, problems develop that only manifest when they’re first fired up – usually on the coldest day of the year.

## What’s Breaking Down This Winter (And Why)

After sitting dormant all summer, heating systems develop predictable failure points that smart technicians check before problems occur. Here are the top components to inspect during September maintenance:

1. **Circulation Pumps**: These top the failure list after summer inactivity. Pump seizure due to 3-4 months of dormancy is a primary breakdown cause. A simple manual rotation during September can prevent an expensive mid-winter replacement.
2. **Induced Draft Motors**: These critical components often seize after months of inactivity due to moisture infiltration and bearing lubricant thickening. The bearings in these motors are particularly vulnerable to corrosion when the system isn’t running regularly. A preventative check includes testing for smooth operation, proper amperage draw, and inspecting wheel clearance before winter demand pushes these motors to failure.
3. **Ignition Systems**: Ignitors frequently fail due to exhaust gas recirculation during startup. Testing spark location and conductivity now prevents no-heat calls later.
4. **Burners**: Summer humidity causes rust and corrosion on burner surfaces, leading to improper flame patterns and inefficient combustion when winter arrives. Carefully inspect burners for warping, rust, and proper alignment, then clean thoroughly with appropriate brushes and compressed air. Many techs skip this step, but it’s essential for preventing carbon monoxide issues and ignition failures.
5. **Flame Sensors**: These develop contamination buildup during the off-season that leads to system failures. A quick cleaning in September ensures reliable ignition when temperatures drop.
6. **Heat Exchangers**: Heat exchanger inspection deserves special attention during September maintenance. Even small cracks can release deadly carbon monoxide into living spaces when systems activate for winter. CO is known as the [silent killer](https://hvacknowitall.com/blog/carbon-monoxide-the-silent-killer-every-tech-should-know-how-to-handle) because it’s odorless, colorless, and dangerous at just 70 ppm, with 400 ppm potentially causing death within hours. Professional-grade testing equipment allows technicians to check ambient air, mechanical rooms, and flue gas during maintenance visits – any reading above 200 ppm in flue gas or detection in the air stream indicates an immediate safety hazard requiring system shutdown.
7. **Condensate Drains**: One of winter’s most overlooked failure points is condensate drainage systems in high-efficiency furnaces. After months without operation, organic growth, debris accumulation, and trap evaporation create perfect conditions for water backups that trigger pressure switches and shut systems down. Many emergency “no heat” calls are simply condensate issues that could have been prevented with September maintenance. Thoroughly flush these lines, verify proper trap depth, and consider adding condensate treatment tablets as preventative maintenance
8. **Control Boards**: The “brain” of modern furnaces often fails after power surges during summer thunderstorms. Testing all functions during the mild weather allows for planned replacement rather than emergency service. [Learn more about control board components here.](https://hvacknowitall.com/blog/guide-to-hvac-pcb-components)

January experiences the highest breakdown rate at 15% of annual heating system failures, followed by December at 12%. [By addressing these components during September’s maintenance sweet spot](https://hvacknowitall.com/blog/the-truth-about-furnace-tune-ups), you’re preventing the most common emergency calls while protecting your customers’ comfort and safety.

## Immediate Actions in August

The time to act is now, not when the rush hits. Here are the concrete steps you can take in early august to leverage the September sweet spot:

### Customer Communication Templates

Start with your existing customer base. Send a simple email with this message:

> *“Beat the October rush! Schedule your heating system maintenance in September and receive priority scheduling, our thorough 21-point safety inspection, and peace of mind before the cold weather hits. Plus, mention this email for $25 off when you book this week.”*

For text messages, keep it even simpler:

> *“HVAC Alert: Book your heating maintenance in September to avoid the October rush and potential parts delays. Reply YES for priority scheduling.”*

These templates have produced open rates of 20% for email and 98% for text messages, significantly outperforming industry averages.

### How to Pitch September Maintenance During AC Calls

Every summer service call is an opportunity to book fall maintenance. Here’s a script that works:

> *“While I’ve got your AC running great today, I noticed your heating system hasn’t been checked since last year. Most of our customers book their heating maintenance in September to avoid the October rush when everyone calls at once. Would you prefer a morning or afternoon appointment in the second week of September?”*

This approach uses the psychology of choice rather than yes/no questions, increasing booking rates by up to 35%. By presenting it as something “most customers do,” you’re establishing a social norm that makes the decision easier.

## The Business Case for September

As a solo technician or small shop owner, September maintenance offers a direct path to more stable income and better work-life balance. While emergency calls might seem more profitable at $950 versus $250 for maintenance, consider the hidden value: maintenance calls take half the time, create repeat customers, and can be scheduled on your terms. This means you can complete 6-8 maintenance visits daily compared to 3-4 emergency calls, with less stress and more predictable hours.

For small operations, simple maintenance agreements don’t need fancy software or complicated contracts. Start with a basic one-page agreement offering two seasonal checks (fall and spring), priority emergency service, and a 10% discount on repairs. Price it reasonably at $199-299 annually, and begin by offering it to your most satisfied customers. Even securing just 25 maintenance agreements creates a reliable $5,000-7,500 revenue base that helps smooth seasonal income fluctuations.

The beauty of September maintenance for small shops is that it transforms your business model from “waiting for the phone to ring” to proactively scheduling your workload. While we recommend you use a proper fleet management solution (like Housecall Pro), you can use a simple spreadsheet to track customer equipment age and maintenance history, then group appointments by neighborhood to maximize efficiency.

Many successful one-person operations report that maintenance agreements eventually represent 30-40% of their total revenue while requiring only 20% of their labor hours – making them the most profitable aspect of their business.

## Building Long-Term Strategy

September’s calmer pace creates the perfect opportunity for training newer technicians before emergency season hits. Pairing experienced professionals with apprentices during maintenance calls allows for hands-on learning without the pressure of emergency situations. Companies report technicians trained through structured September maintenance programs experience 40% lower error rates during their first heating emergency season, building the reliability and discretionary effort that distinguish successful HVAC professionals.

Perhaps most importantly, strategic September scheduling dramatically improves technician quality of life by spreading workload more evenly throughout the year. This approach helps professionals avoid the 60+ hour weeks that contribute to our industry’s troubling 18-22% first-year turnover rate. Companies implementing structured September maintenance programs report a 35% reduction in technician overtime hours during winter months and corresponding 27% decrease in turnover. This creates space for both excellent customer service and technician [work-life balance](https://anchor.fm/hvacknowitall/episodes/Work-Life-Balance-And-Why-Its-Important-e1tjt0e), essential for long-term career satisfaction.

## Your September Action Plan

Here’s your action plan to make it happen:

1. **Early August**: Set up a simple email and text campaign to existing customers promoting September maintenance.
2. **During Every AC Call**: Pitch September heating maintenance using the choice-based script.
3. **Create Your Packages**: Develop tiered maintenance offerings that provide clear value while maintaining healthy margins.
4. **Train Your Team**: Ensure all technicians understand the technical and business benefits of September maintenance so they can confidently communicate them to customers.
5. **Document Everything**: Use digital documentation tools to thoroughly record all findings during September maintenance, creating a baseline for future service.

The difference between a good technician and a great one often comes down to [five minutes of extra attention](https://hvacknowitall.com/blog/five-minutes-to-be-a-better-tech). September maintenance gives you the time to be thorough, catch problems before they become emergencies, and build relationships that last beyond a single service call.

Your customers get reliable heating when they need it most. You get a more predictable schedule and income stream. Everyone wins in the September sweet spot.

--------------------------------------------------

# ID: 6068

## Title: Bi-Flow TXVs in Heat Pumps: How They Work &amp; Why They Matter

## Type: blog_post

## Author: Julian Finbow

## Publish Date: 2025-07-23T16:56:02

## Word Count: 1032

## Categories: Components, Heat Pumps

## Tags: bi-flow TXV, condenser, cooling mode, Danfoss TGE, discharge gas, evaporator, external equalization, heat pump, heat pump troubleshooting, heating mode, HVAC components, metering device, refrigerant flow, refrigeration cycle, reversing valve, suction line, system design, thermostatic expansion valve, TXV, valve sizing

## Permalink: https://hvacknowitall.com/blog/bi-flow-txvs-in-heat-pumps-how-they-work-why-they-matter

## Description:
## Understanding Heat Pump Refrigerant Flow Challenges

The **Thermostatic Expansion Valve** (TXV) remains one of the most reliable metering devices in HVAC systems, but heat pump applications present unique challenges. Unlike standard air conditioning systems, heat pumps must accommodate refrigerant flow in both directions during heating and cooling cycles.

![A 3D cross section of a Danfoss TR6 Bi-Flow TXV](https://hvacknowitall.com/wp-content/uploads/2025/07/Screenshot-2025-07-24-at-15.14.37.png)

*A 3D cross section of a Danfoss TR6 Bi-Flow TXV*

This is where specialized “**Bi-Flow” TXVs** become crucial to system performance. While some systems use standard TXVs with separate check valve bypasses or even dual TXV configurations, bi-flow TXVs offer an elegant solution by handling refrigerant flow in both directions with a single component.

In this article, we’ll explore how these specialized valves work, focusing on the Danfoss TR6 Bi-Flow TXV, and why understanding their operation is essential for any HVAC professional working with heat pump systems.

**Note**: Understanding [TXV operation](https://hvacknowitall.com/blog/adaptive-vs-fixed-expansion-valves) and [Heat Pump Reversing Valves](https://hvacknowitall.com/blog/reversing-valves-and-their-control-designation) is important to obtain the key takeaways from this article.

## How Bi-Flow TXVs Solve the Reversing Problem

![Simplified air conditioning / heat pump system (bi-flow)](https://hvacknowitall.com/wp-content/uploads/2025/07/Screenshot-2025-07-24-at-15.20.35.png)

*Simplified air conditioning / heat pump system (bi-flow)*

Referencing the above image, we will focus on the function of the [**Danfoss TR6 Bi-Flow TXV**](https://www.danfoss.com/en/products/dcs/valves/thermostatic-expansion-valves/thermostatic-expansion-valves/tr-6-thermostatic-expansion-valves/#tab-overview). This drawing from the valve’s [**Data Sheet**](https://assets.danfoss.com/documents/407758/AI246186497192en-001002.pdf) highlights the operation of the system in Cooling Mode.

```
Note: As mentioned, there are different ways to achieve heat pump operation with TXVs (this is also outlined in the TR6 Data Sheet). Our example will focus on the use of a single Bi-Flow TXV with no check valves.
```

## Cooling Mode Operation Explained

Cooling mode operation is similar to any other **Air Conditioning** or **Refrigeration** System. Through the Reversing Valve, the **Compressor’s Discharge Gas** is allowed to flow into the **Outdoor Coil** to reject heat and **Condense**. Liquid is then fed through the Bi-Flow TXV in its *Conventional Flow Direction* (more on this later). The liquid refrigerant absorbs heat and **Evaporates** in the Indoor Coil before returning to the Compressor.

**Note:** The TXV has its **Sensing Bulb** and **External Equalization Tube** installed in the Compressor **Suction Line**, instead of on the “Evaporator Outlet” like it would be in a plain AC System. This will allow proper TXV Control during the **Heating Cycle** as well. When mounting the sensing bulb, position it at the 10 or 2 o’clock position for suction lines 7/8″ or smaller, and at the 4 or 8 o’clock position for suction lines larger than 7/8″. This specific positioning is critical because refrigerant tends to stratify differently depending on line size.

## Heating Mode Operation Explained

In Heating Mode, the piston in the Reversing Valve moves to allow system flow to reverse. This directs hot Discharge Gas to the Indoor Coil for heating, and the Condensed refrigerant now feeds the Bi-Flow TXV in the *Reverse Flow Direction*. The refrigerant is then able to feed the Outdoor Coil, and absorb heat from the outdoors while Evaporating.

![ TR6 Static/opening superheat graph](https://hvacknowitall.com/wp-content/uploads/2025/07/TR6-Staticopening-superheat-graph.png)

*TR6 Static/opening superheat graph*

**Note:** The above image from the [TR6 Data Sheet](https://assets.danfoss.com/documents/407758/AI246186497192en-001002.pdf) shows a setback of a Bi-Flow TXV. The setback of this set-up for a Heat Pump is that the TR6 has a slight capacity reduction (how much heat transfer it can support) in the Reverse Flow Direction. In this example, we are “Bias towards Cooling”, as we have more capacity in the Cooling Mode. This is made up for in this design by fewer total components and gained system simplicity.

## The Danfoss TR6 Bi-Flow TXV Design

In the Danfoss TR6 Manual (below), the design of the valve internals and pin is explained to give this TXV the characteristic to support refrigerant flow in both directions.

[AI318728845972en-000407](https://hvacknowitall.com/wp-content/uploads/2025/07/AI318728845972en-000407.pdf)[Download](https://hvacknowitall.com/wp-content/uploads/2025/07/AI318728845972en-000407.pdf)

With the valve’s External Equalization Port (and Sensing Bulb) installed in the Compressor Suction Line (instead of one of the coil’s outlets), this allows the valve to reference “Evaporator” Outlet Pressure accurately, regardless of which mode it operates in or the current outdoor/indoor conditions.

## Performance Considerations: Capacity in Reverse Flow

One important consideration when working with bi-flow TXVs is their performance in reverse flow mode. As shown in the Danfoss TR6 documentation, there’s typically a slight capacity reduction when the valve operates in the reverse flow direction. System designers account for this when selecting components, often biasing the system toward cooling performance where maximum capacity is most critical.

This trade-off is generally acceptable because the simplified system design (fewer components, less potential leak points) outweighs the small capacity reduction. Additionally, modern heat pump systems often include supplementary heating for extreme cold conditions when maximum heating capacity would be needed.

## Common Troubleshooting Issues

When working with heat pump systems using bi-flow TXVs, be aware of these common issues:

1. **Improper sensing bulb mounting**: The sensing bulb must be securely attached to the suction line with good thermal contact
2. **External equalization line restrictions**: Any kinks or blockages will cause improper valve operation
3. **Valve sizing issues**: An undersized valve can restrict flow and reduce system capacity
4. **Refrigerant charge problems**: Proper charge is critical for optimal valve operation in both directions

***Related: In a recent podcast, Jamie breaks down how these valves work in both heating and cooling modes and why they need to handle refrigerant flow in two directions. They discuss the parts of a TX valve, how pressure and temperature control the flow, and why Danfoss uses stainless steel in their design.***

## Key Takeaways

When working with heat pump systems using bi-flow TXVs, remember these key points:

- Bi-flow TXVs allow refrigerant to flow in both directions without additional check valves
- External equalization and sensing bulb placement are critical for proper operation
- Some capacity reduction in reverse flow is normal and accounted for in system design
- TXV selection should match the specific heat pump application requirements
- The simplified system design typically outweighs the minor capacity reduction in reverse flow

As the industry continues to evolve toward more electronic expansion valves (EEVs) and inverter-driven compressors, the principles of bi-directional flow control remain important. For technicians working on conventional heat pump systems, understanding bi-flow TXV operation is a valuable skill that leads to better diagnostics and more efficient system performance.

--------------------------------------------------

# ID: 5994

## Title: HVAC Design Heat Load Factors: Finding the Shortcuts

## Type: blog_post

## Author: Drew Towzer

## Publish Date: 2025-07-10T14:54:12

## Word Count: 1516

## Categories: Heat Pumps, HVAC Installation

## Tags: accurate equipment sizing, AFUE rating, energy consumption data, gas consumption sizing, heat load factor, heat pump sizing guide, home heating requirements, HVAC contractor tools, HVAC rule of thumb, HVAC sizing shortcut, oversized equipment, performance-based heat load, quick heat load calculation, right-sized heat pumps, virtual quotes

## Permalink: https://hvacknowitall.com/blog/hvac-design-heat-load-factors-shortcut

## Description:
[![](https://hvacknowitall.com/wp-content/uploads/2025/07/Feel-Good-Homes-640x1024.jpg)](https://www.amazon.ca/dp/1781339163/)

*This article is **Part 3** of a 3-part series on heat load calculations and proper HVAC sizing by Drew Tozer for HVAC Know It All. Read [**Part 1**](https://hvacknowitall.com/blog/heat-load-factors-a-simplified-method-for-10-second-load-calculations) & **[Part 2](https://hvacknowitall.com/blog/heat-loads-in-the-real-world-precision-versus-accuracy).*** Drew’s book “**[Feel-Good Homes](https://www.amazon.ca/dp/1781339163/)**: How to choose the right heat pump for a comfortable, healthy, sustainable home” is available for purchase now. *NOTE: This information is tailored towards cold climates / heating-dominated regions.*

## A Common Factor, Then a Theory

When I was completing energy assessments for homeowners, I noticed that the modelled energy consumption was frequently *20x* the gas consumption.

I assumed it was a coincidence, and I didn’t dig into the data.

I also didn’t have a way to check the numbers on a bigger scale. But heat load calculators that were based on the same methodology started to be released, which gave me the opportunity to test my theory (~20x the gas consumption).

I used [thermalpoint.ca](http://thermalpoint.ca/) (developed as a collaboration in Toronto between TRCA, STEP, and TAF). It’s a calculator for Ontario homeowners–it follows the same process but it does the HDD lookup in the backend.

See the image below. I recorded heat loads (output) for different scenarios:

- 200 m³ increments from 1,000 – 3,000 m³
- Compared 90% and 95% AFUE (efficiency rating)
- Compared Toronto, Ottawa, and Thunder Bay (not shown)

Look at the results!

![Table of inputs and outputs for various scenarios in the thermalpoint.ca heat load calculator.](https://hvacknowitall.com/wp-content/uploads/2025/07/1745455192131-826x1024.jpeg)

*Figure 2. Summary table of inputs and outputs for various scenarios in the [thermalpoint.ca](http://thermalpoint.ca/) heat load calculator.*

The “load factor” is 19 across every scenario. I adjusted the results to exclude AFUE, so the heat load calculation would be: gas usage \* 19 \* AFUE.

Assuming AFUE of the existing equipment is *around* 92%, we get the magic 17.5 **heat load factor** for Toronto.

I ran the test in reverse, using the **heat load factor** to calculate heating loads, and comparing it to the output from the calculator. The results were +/- 1,000 BTU/hr.

The results were similar in Toronto, Ottawa, and Thunder Bay. That surprised me, given the difference in design temperatures (4°F, -7°F, and -16°F, respectively).

My best guess is that the two temperature metrics roughly cancel out. The calculation includes “heating degree days” in the numerator and “indoor set point minus design temperature” in the denominator. I expect they’re strongly correlated within a climate zone.

## Next Steps: Calculate Your Heat Load Factor

Let’s talk about a shortcut for the quoting process. Do the *full calculation* for the next 10 projects. Choose projects with common AFUE ratings like 90-96%.

Once you have all 10, write them in an Excel sheet with three columns: gas usage, heat load, and heat load factor. You already have gas usage and heating load. To get the **heat load factor**, divide heating load by gas usage (therms or m³).

How does it look?

Are the numbers in the third column consistent? You can check for outliers, but otherwise take the average.

That’s your local **Heat Load Factor (HLF).**

Now you have a shortcut for accurate heat loads.

## **A method to do accurate heat load calculations in 10 seconds or less.**

Ask the homeowner for their annual gas usage, adjust for gas water heating (minus 300 m³ or 100 therms), and multiply by your calculated **HLF**.

I added “annual gas usage” and “water heat fuel type” to my company’s *Homeowner Intake Form*, so I get the information upfront. Now I confidently give virtual quotes for right-sized heat pumps.

![Foundry Heat Pumps Homeowner Intake Form](https://hvacknowitall.com/wp-content/uploads/2025/07/Screenshot-2025-07-10-at-11.11.12.png)

*Foundry Heat Pumps Homeowner Intake Form*

And if you don’t have a dynamic *Homeowner Intake Form*, get one!

## Real-World Application

Let’s look at an example. A Toronto homeowner who wants a heat pump to replace their furnace and AC. From their *Homeowner Intake Form* we know:

1. Annual gas usage: 1,300 m³ (460 therms)
2. Does the furnace have plastic exhaust pipes or metal? Plastic (i.e. it’s likely 90-97% efficient)
3. Water heating fuel? Electric

Take a second. What equipment do we quote?

The **heat load factor** in Toronto is 17.5x (50x), it’s a high-efficiency furnace, and there’s no adjustment needed for water heating (it’s electric, not gas).

**Answer:** I’d confidently quote a 2-ton heat pump to cover the ~23,000 BTU/hr heat load (1,300 x 17.5 or 460 x 50 = 23,000).

Yes, I copied the gas usage from the story in the introduction. The one where the contractor quoted a 7-ton gas furnace. We got a slightly different answer (23 KBTU versus 26 KBTU), but it’d lead to the same equipment. Again, the goal is *close enough*.

Even if you don’t use **heat load factors** as your *only* sizing criteria (note: you shouldn’t), it’s extremely useful as a sizing rule-of-thumb for HVAC in cold climates. You’ll immediately know that a Toronto house with 1,300 m³ (460 therms) of gas heating needs a 2-ton heat pump, *not* a 7-ton furnace.

## Why This Matters for System Performance

Traditional rules-of-thumb for sizing (like 1 ton per 400 sqft) are useless because they’re based on data that doesn’t directly impact heat loads. A modern, well-built 3,000 sqft house that’s airtight and well-insulated may need less heat than an old 1,000 sqft bungalow that’s leaky and uninsulated.

A rule-of-thumb based on square footage won’t reflect that—but gas usage will reflect how the house performs under real-world conditions.

This illustrates perfectly why right-sized equipment matters, especially when transitioning to heat pumps. The solution, as Gary suggests, is to “size closer to the cooling load but as close to the heating load as possible” and supplement with auxiliary heat when needed.

## Limitations and Adjustments

![IECC North America Climate Zones](https://hvacknowitall.com/wp-content/uploads/2025/07/IECC-Climate-Zone-Map-1024x713.jpg)

*IECC North America Climate Zones*

First, this works best for heating-dominated climates. Warm climates have an extra variable that complicates everything: **humidity**.

Second, pay attention to indoor setpoints. Homeowners that keep the thermostat at 65°F all winter will throw off the calculation. You can adjust the HDD baseline to account for extreme setpoints.

And third, gas consumption directly correlates to winter temperatures, so we need to adjust the **heat load factor** annually based on the *coldness* of each winter. The amount of cold that the house had to fight against to stay warm all winter. We can use heating degree days to assess “coldness”.

The **heat load factor** for Toronto is 17.5x (50x) for 2024 gas consumption. If 2025 is 10% colder (i.e. 10% more heating degree days), adjust the **heat load factor** down by 10%.

Notice that it’s an inverse relationship because *more* HDD means *colder*. A 10% *increase* in HDD results in a 10% *decrease* in the HLF—a colder winter naturally forces every house to use more energy for heating, so the same gas usage in a colder winter means a higher performing house (i.e. lower heat load).

## Avoiding Common Heat Pump Sizing Mistakes

This approach helps avoid one of the most common mistakes in HVAC: oversizing equipment. As explained in the HVAC Know It All article on [heat pump oversizing](https://hvacknowitall.com/blog/heat-pump-oversizing-what-every-hvac-tech-needs-to-know), “Many oversizing issues stem from incorrectly performed load calculations. A concerning practice involves deliberately ‘manipulating’ Manual J calculations to justify larger equipment.”

Using real-world energy consumption data provides a reality check against these inflated calculations. The Heat Load Factor method gives you a realistic starting point that can be validated with other assessment methods during your site visit.

For a deeper dive into proper heat pump sizing and installation considerations, check out the podcast below where Gary and I discuss how systems should be sized with care, not guesswork, so homes stay comfy, air stays clean, and systems last longer without costly breakdowns.

## Final Thoughts

Now that you know all the shortcuts to load calculations, put it into practice in your HVAC business:

- **Integrate With Existing Processes** – Ask about gas consumption in your intake forms to gather the data needed for Heat Load Factor calculations upfront.
- **Provide Confident Virtual Quotes** – Leverage performance-based calculations to deliver accurate equipment sizing recommendations remotely, but a disclaimer on virtual quotes that final pricing requires a site visit to confirm measurements and logistics.
- **Pre-Qualify Customers** – Use the Heat Load Factor method and virtual quotes to quickly identify and avoid price-shopping customers seeking the lowest bid regardless of proper sizing.
- **Streamline Premium Service** – Position yourself as a premium contractor by offering accurate heat pump sizing quotes without time-consuming initial site visits.
- **Assess Infrastructure Limitations** – During the site visit, measure existing ductwork and static pressure during your final site assessment to validate your heat load factor calculations. And confirm that the electrical panel can support the recommended setup.

By consistently using this approach, you’ll avoid the comfort issues associated with oversized equipment while ensuring your heat pump installations perform as designed. Your customers will appreciate the improved comfort, and you’ll build a reputation for installing systems that actually work as intended.

---

*This article is **Part 3** of a 3-part series on heat load calculations and proper HVAC sizing by Drew Tozer for HVAC Know It All. Read [**Part 1**](https://hvacknowitall.com/blog/heat-load-factors-a-simplified-method-for-10-second-load-calculations) & **[Part 2](https://hvacknowitall.com/blog/heat-loads-in-the-real-world-precision-versus-accuracy).***

--------------------------------------------------

# ID: 5984

## Title: HVAC Design Heat Loads in the Real World: Precision Versus Accuracy

## Type: blog_post

## Author: Drew Towzer

## Publish Date: 2025-07-10T02:27:22

## Word Count: 1213

## Categories: Heat Pumps, HVAC Installation

## Tags: accurate heat loads, AFUE, BTU calculation, degree days, design temperature, energy consumption data, energy modeling, gas usage analysis, heat load calculation, heat pump sizing, heating degree days, HVAC sizing, oversized equipment, performance-based sizing, runtime data

## Permalink: https://hvacknowitall.com/blog/hvac-design-heat-loads-precision-versus-accuracy

## Description:
[![](https://hvacknowitall.com/wp-content/uploads/2025/07/Feel-Good-Homes-640x1024.jpg)](https://www.amazon.ca/dp/1781339163/)

*This article is Part 2 of a 3-part series on heat load calculations and proper HVAC sizing by Drew Tozer for HVAC Know It All. Read **[Part 1](https://hvacknowitall.com/blog/hvac-design-heat-load-factors-shortcut)** & [**Part 3**](https://hvacknowitall.com/blog/hvac-design-heat-load-factors-shortcut). Drew’s book “**[Feel-Good Homes](https://www.amazon.ca/dp/1781339163/)**: How to choose the right heat pump for a comfortable, healthy, sustainable home” is available for purchase now.* *NOTE: This information is tailored towards cold climates / heating-dominated regions.*

## Modelled Versus Performance-Based Heat Load Calculations

There are three types of heat load calculations:

1. Traditional rules of thumb (“1 ton per 400 sq ft”)
2. Energy models (theoretical)
3. Performance-based (real-world data)

Within performance-based heat load calculations, you can use energy consumption or runtime data. Energy consumption (also called energy usage or gas usage) looks at how much gas (or another fuel) is used to heat the house. Unlike rules of thumb and energy models, energy consumption is based on how the house performs under real-world conditions.

![](https://hvacknowitall.com/wp-content/uploads/2025/07/Thermostat-Runtime-Data-Example-1024x768.png)

*Thermostat Runtime Example. Image Credit: AS Air Home*

Runtime data is simply looking at *how long* the equipment operates at specific outdoor temperatures. If a 60,000 BTU/hr furnace runs for 30 minutes in an hour that matches outdoor design conditions, then the heating load is 30,000 BTU/hr (30 minutes / 60 minutes \* 60,000 BTU/hr = 30,000 BTU/hr).

![](https://hvacknowitall.com/wp-content/uploads/2025/07/Monthly-Gas-Bill-Example.png)

*Monthly Gas Bill Example.*

My preference is energy consumption because **it’s easier to get a monthly gas bill than thermostat data**. Runtime data can also be difficult to interpret for multiple-stage or variable furnaces.

## Why Traditional Methods Fall Short

Traditional rules of thumb are crude guesses. They’re quick but unreliable and unlikely to provide the right answer.

Energy models aren’t much better—whether it gets you *close enough* depends on the accuracy of the model, the underlying assumptions, and the complete and accurate collection of household data like insulation levels, orientation, shading, air leakage, etc.

Models are **conservative** (they overestimate) and we often input conservative values to *play it safe*. That’s margin on margin.

The biggest issue with a modelled heat load is that **it might be right—or wildly wrong. There’s no way to tell.**

To prove my point, here’s a thought experiment: a homeowner gets an energy assessment completed. They give the report to you (the contractor) and it includes a 32,000 BTU/hr heating load. Is it an overestimate, underestimate, or *close enough*?

![](https://hvacknowitall.com/wp-content/uploads/2025/07/Example-Energy-Assessment-Report-791x1024.jpg)

*Energy Assessment Report. Image Credit: City of Nanaimo*

***How would you know?***

You could double check the report and confirm basic metrics like square footage, number of floors, location, and window count. But you won’t know the exact measurements, air leakage, insulation levels, etc. And since air leakage is the biggest source of heat loss, **you *can’t* know if it’s accurate or not.**

But if that same homeowner (located in Toronto, for my convenience) tells me they used 1,500 m³ (530 therms), I know their heating load is *about* 26,000 BTU/hr. Then I can recommend a [2-ton or 2.5-ton heat pump](https://hvacknowitall.com/blog/heat-pump-oversizing-what-every-hvac-tech-needs-to-know) based on other factors.

Most HVAC systems are oversized because the heat loads were overestimated (with margins on margins) and the equipment has been replaced like-for-like for the life of the house. An *old* oversized furnace gets replaced with a *new* oversized furnace.

## Gas Usage for Heat Loads: The Long Way

The idea is simple: a house with a furnace burns gas for heat. The more heat the house needs, the more gas it burns. So, we can look at the amount of gas *used* to assess how much heating the house *needs*.

For this heat load method, we need four things:

1. Gas consumption
2. Equipment efficiency
3. Outdoor temperatures
4. The 99% design temperature.

For outdoor temperatures, we’ll use a metric called **heating degree days**. It’s a combination of time and temperature that reflects how much heating or cooling was needed to keep an indoor temperature constant.

![](https://hvacknowitall.com/wp-content/uploads/2025/07/heating-and-cooling-degree-days-visualization.jpg)

*Image Credit: Weatherbit*

Outdoor temperatures are compared to a baseline temperature (usually 60°F or 65°F). If the mean temperature is 64°F for a day…well, that’s 1 degree day. While heating degree days can be counted in Celsius, we’ll need to use Fahrenheit because BTU and BTU/hr are based in Fahrenheit.

For context, Toronto has ~7,000 heating degree days with a 65°F baseline. A colder city like Edmonton has 10,000+. In US terms, think Portland, Maine (7,000 HDD) versus Anchorage, Alaska (10,000+).

Here are the steps for the heat load calculation:

1. Calculate annual BTUs of heating (from m³/therms and equipment AFUE)
2. Lookup heating degree days (HDD) for the time period
3. Divide BTU by HDD (BTU per degree-day)
4. Divide by 24 (BTU per degree-hour)
5. Multiply by design/thermostat differential
6. **That’s your heating load!**

We take the full amount of heating used (convert gas usage to millions of BTUs), taking into account equipment efficiency. Then we look up the heating degree days for our area and time period ([degreedays.net](http://degreedays.net/) is easy).

Now we divide BTU by HDD to understand how much heat (BTU) we need per degree-day. Divide again by 24 to get BTU per degree-hour.

We’re aiming for a heating load (BTU/hr), so intuitively it feels close that we have a BTU per degree-hour number. We just need to eliminate the “degree” unit—and we do that with the design temperature. Or rather, the difference between the indoor setpoint (70°F) and the design temp.

For Toronto, the 99% design temperature (found on [ASHRAE](https://ashrae-meteo.info/v2.0/index.php)) is 4°F, so the *difference* between indoor and outdoor temperatures will be 66°F (70 minus 4 equals 66).

If our Toronto house needed 360 BTU per degree-hour, then the heating load is ~24,000 BTU/hr (360 \* 66 = 23,760).

That’s the *long* way of doing it (although significantly faster than energy modelling). Tools like [thermalpoint.ca](http://thermalpoint.ca/), [knowyourload.ca](http://knowyourload.ca/), and [thermentor.com](http://thermentor.com/) are making it easier and faster.

## How This Affects Your Heat Pump Sizing

Getting the heat load right is critical for properly sizing heat pumps. As Gary notes in his [heat pump installation guide](https://hvacknowitall.com/blog/central-heat-pump-install-considerations), ductwork constraints often limit how large your heat pump can be. If you size strictly to an overestimated heat load, you may encounter airflow problems.

> “If a home has a heat loss of 60k BTU and a heat gain of 24k BTU, how do we size? A heat pump will need 400-450 CFM per ton to run effectively. If we size to the heating load, we need 2000-2250 CFM. In most retrofit applications, we’ll find ductwork only designed to carry 800-1200 CFM.”

The solution is to size closer to the cooling load but as close to the heating load as possible, then supplement with auxiliary heat as needed. This is exactly why accurate heat load calculations are so important.

## Simplifying the Process

For contractors and homeowners who want to skip the manual calculations, several online tools make this process much simpler. But the principle remains the same: **using actual energy consumption data will generally give you a more accurate heat load estimate than theoretical models alone.**

Accurate heat loads lead to [properly sized heat pumps](https://hvacknowitall.com/blog/heat-pump-oversizing-what-every-hvac-tech-needs-to-know), which avoid the comfort issues, short cycling, and poor dehumidification that come with oversized equipment.

---

*This article is Part 2 of a 3-part series on heat load calculations and proper HVAC sizing by Drew **Tozer** for HVAC Know It All.* *Read [**Part 1**](https://hvacknowitall.com/blog/heat-load-factors-a-simplified-method-for-10-second-load-calculations) & **[Part 3.](https://hvacknowitall.com/blog/hvac-design-heat-load-factors-shortcut)***

--------------------------------------------------

# ID: 5974

## Title: HVAC Design Heat Load Factors: A Simplified Method for 10-Second Load Calculations

## Type: blog_post

## Author: Drew Towzer

## Publish Date: 2025-07-09T22:16:53

## Word Count: 1040

## Categories: Heat Pumps, HVAC Installation

## Tags: accurate heat loads, duct capacity, energy efficiency, energy modeling, F280, heat load calculation, heat pump sizing, heating requirements, HOT2000, HVAC comfort, HVAC design, HVAC Know It All, HVAC professionals, HVAC sizing, load matching, Manual J, oversized equipment, performance-based calculation, right-sized HVAC, short cycling

## Permalink: https://hvacknowitall.com/blog/hvac-design-heat-load-factors-simplified-method-load-calculations

## Description:
[![](https://hvacknowitall.com/wp-content/uploads/2025/07/Feel-Good-Homes-640x1024.jpg)](https://www.amazon.ca/dp/1781339163/)

*This article is **Part 1** of a 3-part series on heat load calculations and proper HVAC sizing by Drew Tozer for HVAC Know It All. Read **[Part 2](https://hvacknowitall.com/blog/heat-loads-in-the-real-world-precision-versus-accuracy)** & **[Part 3](https://hvacknowitall.com/blog/hvac-design-heat-load-factors-shortcut).** Drew’s book “**[Feel-Good Homes](https://www.amazon.ca/dp/1781339163/)**: How to choose the right heat pump for a comfortable, healthy, sustainable home” is available for purchase now.* *NOTE: This information is tailored towards cold climates / heating-dominated regions.*

## HORSESHOES, HAND GRENADES, AND HEAT LOADS: THE ART OF GETTING CLOSE ENOUGH

Heat pump sizing comes in intervals of 6,000 BTU/hr (half-ton) so *close enough* is the only reasonable goal for heat load calculations. Calculating heat loads down to a single BTU/hr won’t change equipment selection.

Heat loss calculations like Manual J, F280, and HOT2000 (H2K) have a long list of inputs that can be adjusted and manipulated in minute detail. This level of control gives the illusion of accuracy but you’re actually getting its cousin: precision.

> ***NOTE**: H2K is the energy modelling software developed by National Resources Canada and used by energy advisors (the Canadian equivalent of HERS Raters). For simplicity, I’ll refer to H2K, but the concepts and criticisms apply to other modelling software and methodologies like Manual J and F280.*

![The difference between accuracy and precision](https://hvacknowitall.com/wp-content/uploads/2025/07/accuracy-vs-precision-1024x768.png)

**Accuracy means getting close to the right answer.** It’s about being *correct*. But precision is about being *exact*, whether it’s correct or not.

### A Real-World Example

Let’s look at an example from 2023. I was helping a homeowner in Toronto (as a third-party consultant, not as an HVAC contractor). It was a hundred-year-old double-brick row house connected to neighbouring houses on both sides. It was leaky because of an issue in the converted attic. An energy advisor assessed the house, completed an energy model, and created a full report with recommendations.

The report included a heating requirement of 83,052 BTU/hr (6.92 tons) and estimated the house would use 3,971 m³ of gas (1,400 therms) per year for heating. Because of the report, the contractor recommended a 7-ton gas furnace.

Such precision.

**Here’s the problem**: over the previous twelve months, the house only used 1,300 m³ (460 therms) of gas for heating—67% less than the modelled amount. I confirmed that the homeowner hadn’t taken any winter vacations that would’ve skewed the data.

I did a performance-based heat load calculation based on actual gas consumption, and the heat load was 26,000 BTU/hr.

One of the best ways to improve the accuracy of models like H2K is to calibrate the results based on real-world performance data like thermostat runtime or energy consumption. H2K has a **very** strong correlation between modelled gas consumption and heat loss (see figure 1).

![H2K Heat Load vs H2K Gas Usage](https://hvacknowitall.com/wp-content/uploads/2025/07/Screenshot-2025-07-03-at-12.43.06 PM-1024x470.png)

**Figure 1. Correlation between modelled gas usage and modelled heat loss for 200 houses in Canada, modelled in HOT200 (H2K) from 2022-2023 under the EnerGuide Rating System (ERS).**

For this house, you can use the *actual* gas consumption and prorate the heat load. The house used 33% of the modelled gas consumption, so the heat load is closer to 33% of 83,052 BTU/hr (27,000 BTU/hr).

It’s not perfect, but it’s getting closer—and *close* is the goal.

## WHY ACCURATE HEAT LOADS MATTER

You can’t get right-sized HVAC without an accurate heat load calculation.

Sure, but why do we want right-sized HVAC?

Comfort, mostly.

But it also has serious implications for heat pumps. [Central ducted heat pumps](https://hvacknowitall.com/blog/central-heat-pump-install-considerations) are often constrained by duct capacity because they need to push more air to move the same amount of heat.

The industry tends to overestimate heating loads, so improving accuracy generally leads to smaller equipment, which reduces the risk of high static pressure.

Smaller equipment will perform better within existing infrastructure, it’ll dehumidify better than oversized equipment, it’ll be quieter and require less maintenance than systems with high duct pressure, and it reduces the odds that the outdoor units will need to be 50% bigger (2 fans instead of 1).

### The Comfort Factor

Let’s talk briefly about **comfort**.

**Oversized HVAC is the underlying cause of many comfort problems.** Traditional contractors oversize equipment as a way to reduce risk: *if it’s too big, it’s not too small*. Or so the thinking goes.

We talk about heating loads like they’re a constant, but it’s an ever-changing state. A house needs a different amount of heating or cooling every hour as outdoor conditions change.

The heat load that we calculate using the 99% design temperature is just a tool to size HVAC systems—but it represents a tiny fraction (by definition, 1%) of the year. The rest of the year has heating and cooling needs too.

And when an HVAC system is oversized, it serves the 0.1% at the expense of the 99.9%. During those hours, the system can’t match the needs of the house.

That means short-cycling equipment, which leads to hot and cold rooms on the top floor of the house because the system isn’t running long enough to provide conditioned air to those floors. The thermostat on the main floor tells the furnace to turn off, long before that happens.

Right-sized HVAC is better at **load matching**, so it can provide the right amount of heating or cooling during more hours of the year. The system can *match* the needs of the house.

In most cases, [right-sized HVAC needs to include a heat pump](https://hvacknowitall.com/blog/heat-pump-oversizing-what-every-hvac-tech-needs-to-know) (either fully electric or installed as a hybrid with a furnace for backup heat—the right option depends on the local climate and the specific house). Even the smallest furnace on its lowest setting is too big for an average house.

Check out this podcast where Gary and I demystify how properly sized heat pumps eliminate hot and cold spots in homes, debunking outdated myths while explaining how modern systems deliver superior comfort and efficiency even in cold climates without requiring oversized equipment or always needing gas backup.

---

*This article is Part 1 of a 3-part series on heat load calculations and proper HVAC sizing by Drew **Tozer** for HVAC Know It All. Read **[Part 2](https://hvacknowitall.com/blog/heat-loads-in-the-real-world-precision-versus-accuracy)** & **[Part 3](https://hvacknowitall.com/blog/hvac-design-heat-load-factors-shortcut).***

*For more on heat pump sizing considerations, check out Gary’s article on [Important Considerations for Heat Pumps](https://hvacknowitall.com/blog/central-heat-pump-install-considerations), where he discusses the critical balance between heating load, cooling load, and duct capacity.*

--------------------------------------------------

# ID: 5951

## Title: Heat Pump Reversing Valves Explained: How They Work in HVAC Systems

## Type: blog_post

## Author: Julian Finbow

## Publish Date: 2025-06-17T17:27:05

## Word Count: 1238

## Categories: Heat Pumps, Components

## Tags: bi-directional components, cooling mode, defrost cycle, differential pressure, discharge gas, heat pump, heat pump diagnosis, heat pump maintenance, heating mode, HVAC components, HVAC troubleshooting, O/B terminal, pilot lines, refrigerant flow, refrigeration cycle, residential HVAC, reversing valve, reversing valve failure, seasonal changeover, solenoid coil

## Permalink: https://hvacknowitall.com/blog/heat-pump-reversing-valves-explained-how-they-work-in-hvac-systems

## Description:
## Introduction

**Heat Pumps** have become increasingly prevalent in the HVAC industry, and they’re not going anywhere. I remember learning about the Reverse Refrigeration Cycle, and wanting it to go away until I was more confident with the “Forward Refrigeration Cycle”. With most everyone working with Heat Pumps, being comfortable with their operating premise and their unique component, the **Reversing Valve** is of paramount importance.

![Detailed image of a reversing valve found in HVAC applications](https://hvacknowitall.com/wp-content/uploads/2025/06/1-Reversing-Valve-882x1024.jpg)

If you’re looking to deepen your understanding of heat pump systems, check out our [General Guide to HVAC Troubleshooting](https://hvacknowitall.com/blog/hvac-troubleshooting) where we cover fundamental diagnostic approaches that apply to heat pump systems.

## Heat Pump Terminology

Instead of saying “**[Evaporator](https://hvacknowitall.com/blog/understanding-evaporator-coils-types-function-troubleshooting-tips)**” and “**[Condenser](https://hvacknowitall.com/blog/refrigeration-ac-condensers-the-critical-heat-dissipaters-in-hvac-systems)**“, a Heat Pump’s Coils are referred to as Indoor, and Outdoor. The **Indoor Coil** is made cool in the summer to provide air conditioning, and it is made warm in the winter to provide heating. The **Outdoor Coil** is opposite to this.

This function is obtained simply by redirecting the refrigerant flow to be “opposite” of normal air conditioning, when the unit runs in heating mode. This is possible by the use of a **Reversing Valve**. There are some specialized components, such as **[Bi-Directional Driers](https://hvacknowitall.com/blog/driers-and-sight-glasses),** which allow this to work, but will not be described in this writing for simplicity.

> 🎧 **LISTEN:** Want to hear more about heat pump operation? Check out our [How TX Valves Adapt to Multiple Refrigerants and Improve Heat Pumps podcast with Jamie Kitchen](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/How-TX-Valves-Adapt-to-Multiple-Refrigerants-and-Improve-Heat-Pumps--Jamie-Kitchen--Part-1-e2ut22g) where Gary explores heat pump components and operation.
>
> https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/How-TX-Valves-Adapt-to-Multiple-Refrigerants-and-Improve-Heat-Pumps–Jamie-Kitchen–Part-1-e2ut22g

## System Layout

The **Basic Refrigeration Cycle** gets some bells and whistles for a Heat Pump with a Reversing Valve.

![Reversing valve operation - An energized vs non-energized coil](https://hvacknowitall.com/wp-content/uploads/2025/06/2-System-Operation-1024x568.png)

The left side represents cooling (normal), and the right side represents heating, where the cycle is reversed. The **[Compressor](https://hvacknowitall.com/compressor-issues)** and other components continue to run during a changeover, while the Reversing Valve changes position.

For example, if the system is running in Cooling, and a call for Heating is required, the Reversing Valves’ Solenoid Coil is energized. This causes the Reversing Valve’s Solenoid Valve to change positions, allowing discharge gas to be sent to the indoor coil to heat the space. In the meantime, the Outdoor Coil extracts the **Enthalpy** available from the outdoors.

**Note:** in the heating cycle, a defrost must occur to free the Outdoor Coil of frost. This is done by simply again “Reversing” the system flow so that Discharge Gas temporarily provides its heat to the Outdoor Coil. For proper heat pump installation in cold climates, consider adding a drain pan heater as demonstrated in our [How To Install A Drain Pan Heater On A Cold Weather Heat Pump](https://www.youtube.com/watch?v=atiXmN2swgA) video.

## How the Reversing Valve Works

The Reversing Valve utilizes differential pressure to get the “Valve” to move. This is achieved through utilizing High Pressure Discharge gas to flow through the valve’s “**Pilot Lines**“, to influence the movement of the Valve.

![Illustration of Discharge Gas (red) and Suction Gas (blue) through Reversing Valve](https://hvacknowitall.com/wp-content/uploads/2025/06/3-Reversing-Valve-1024x405.png)

On the left side of the above image, Discharge gas is shown routing through the Pilot Line to push the Reversing Valves’ cylinder towards the left. This orientation allows for Discharge Gas (red) and Suction Gas (blue) through the Valve in the shown path. This state could realize the Solenoid Coil being deenergized.

On the right side of the above image, think of the Solenoid Coil being energized. This causes the Solenoid Valve to change positions, and provide a new Discharge Gas Path within the Pilot Lines. The new path pushes the cylinder towards the right side of the Reversing Valve. This allows the second orientation of Discharge and Suction Gas through the valve.

In cooling, the Discharge gas goes through the Reversing Valve, and to the Condenser. When the solenoid is energized, the reversing valve pushes Discharge Gas to the indoor coil for heating.

## Control Designation and Regional Considerations

Different manufacturers use different control strategies for their reversing valves. As explained in our article on [Heat Pump Reversing Valves and Their Control Designation](https://hvacknowitall.com/blog/reversing-valves-and-their-control-designation), most manufacturers default to heat (O terminal is energized for cooling), though some still default to cooling (B terminal is energized for heating).

**Note:** Different areas (Toronto vs. Miami) have different failure modes for the Heat Pump/Reversing Valve. In a market with cold winters such as Toronto, the unit will fail to Heating. In a warmer market (Miami), the unit will fail to provide Cooling. The common failure is the Solenoid Coil burning out, so failure occurs with the Solenoid Coil deenergized.

Some manufacturers that use B terminal designation (energize for heating) include:

- Rheem
- Ruud
- Weathermaker
- Ameristar
- Bosch Air Source

Always consult the manufacturer’s documentation for specific wiring information, as incorrect terminal connections can cause the system to operate in the opposite mode than intended.

## Common Reversing Valve Issues and Troubleshooting

For practical troubleshooting guidance, you can also check out our [Quick Heat Pump Troubleshooting and Diagnosis](https://www.youtube.com/watch?v=nQ3toZhtMZM) video that demonstrates common issues.

### Valve Stuck in One Position

- **Symptoms:** System runs in only heating or only cooling mode regardless of thermostat setting
- **Diagnosis:**
  - Verify proper voltage to the solenoid coil (typically 24V)
  - Check temperature difference across the valve in both modes
  - Listen for the distinctive “click” when the valve should change over
- **Solution:**
  - If solenoid receives proper voltage but doesn’t activate, replace the coil
  - If solenoid activates but valve doesn’t shift, valve may need replacement
  - In some cases, rapidly cycling between heating and cooling can free a stuck valve

### Leaking or Bypassing Valve

- **Symptoms:** Poor performance in one or both modes, inability to maintain temperature
- **Diagnosis:**
  - Listen for hissing sounds indicating internal leakage
  - Check for abnormal temperature readings across valve ports
  - Monitor system pressures for irregularities
- **Solution:**
  - Replacement is typically required as internal repair is not practical in the field

### Solenoid Coil Failure

- **Symptoms:** System operates in default mode only
- **Diagnosis:**
  - Test coil resistance (typically 50-80 ohms for 24V coils)
  - Check for voltage at the coil terminals when mode change is called for
  - Inspect for physical damage or burn marks on the coil
- **Solution:**
  - Replace the solenoid coil if failed
  - Check control wiring and thermostat settings after replacement

> 🎧 **LISTEN:** For more on heat pump component troubleshooting, listen to our [Refrigeration Side Troubleshooting podcast with Jamie Kitchen](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/Refrigeration-Side-Troubleshooting-wJamie-Kitchen-e2d9u0q) where they discuss refrigeration system diagnostics.
>
> https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/Refrigeration-Side-Troubleshooting-wJamie-Kitchen-e2d9u0q

## Summary

Heat Pumps are everywhere, and understanding their operating principle is very important. Reversing Valves are an integral part of a Heat Pump, and they are important to understand. Many Heat Pump operational, troubleshooting, and repair scenarios relate directly to it.

The Reverse Refrigeration Cycle is demystified when its operation and the Reversing Valves’ function are understood. Being comfortable with the operating principle of the Reversing Valve allows a technician to be successful when diagnosing issues with Heat Pump Systems.

To learn more about related components in heat pump systems, check out the discussion on expansion devices in our podcast episode with Jamie Kitchen on [How Europe is Beating North America in HVAC Innovation](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/How-Europe-is-Beating-North-America-in-HVAC-Innovation--Jamie-Kitchen--Part-2-e2v4e48).

https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/How-Europe-is-Beating-North-America-in-HVAC-Innovation–Jamie-Kitchen–Part-2-e2v4e48

> 📺 **WATCH:** For a visual demonstration of heat pump operation in different building applications, watch our [Water Cooled Heat Pumps, Air Conditioners and Coaxial Coils video](https://www.youtube.com/watch?v=LHJjDfZXUOM) where Gary explains heat pump components in building loops.

--------------------------------------------------

# ID: 5941

## Title: BMS User Interfaces: From Graphics to Mobile Dashboards

## Type: blog_post

## Author: Ben Reed

## Publish Date: 2025-06-05T13:48:46

## Word Count: 1395

## Categories: Automation

## Tags: alarm management, BMS interface, BMS navigation, BMS workstation, building automation dashboards, building automation software, building controls visualization, graphical user interface, HVAC dashboard shortcuts, HVAC graphics, HVAC user interfaces, mobile BMS apps, trend analysis

## Permalink: https://hvacknowitall.com/blog/bms-user-interfaces-dashboards

## Description:
Picture this: You’re called to troubleshoot a hot complaint on the fifteenth floor. You arrive at the mechanical room, sit down at the BMS workstation, and… freeze. The screen is filled with animated graphics, flashing icons, and enough data to make your head spin. Where do you even click first? How do you find the VAV box serving that space? And why does this interface look like it was designed by someone who’s never actually fixed an HVAC system?

If you’ve ever felt overwhelmed by a BMS interface, you’re not alone. Many technicians receive extensive training on mechanical systems but minimal instruction on navigating the digital dashboards that control them. Yet in today’s world, your ability to efficiently use these interfaces directly impacts how quickly you can diagnose problems and keep tenants comfortable.

Let’s demystify BMS interfaces—from their humble beginnings to today’s mobile apps—and give you the confidence to navigate any system you encounter.

## From Green Screens to Glass Screens: The Evolution of BMS Interfaces

Understanding where BMS interfaces came from helps explain why they work the way they do today. Each generation built upon the last, carrying forward both improvements and legacy quirks.

### The Command Line Era (1980s)

Early BMS interfaces were text-based, requiring operators to type commands like:

```
DISPLAY AHU1.SAT
SET AHU1.STPT = 55
TREND AHU1.SAT INTERVAL=5MIN DURATION=24HR
```

These systems were powerful but required memorizing commands and syntax. Technicians needed to know exact point names and command structures to get anything done. The learning curve was steep, but once mastered, experienced operators could work quickly.

### The Graphic Revolution (1990s-2000s)

As computing power increased, graphical interfaces became the norm. System integrators created animated schematics of equipment with live data overlays. Suddenly, operators could see a visual representation of the systems they managed.

This era introduced the familiar elements we still see today:

- Equipment graphics showing real-time status
- Color-coding to indicate alarms and state changes
- Navigation trees to browse building systems
- Point-and-click access to commands and setpoints

While more intuitive than command lines, these interfaces often suffered from clutter, inconsistent design, and hardware limitations. Many were custom-built for each installation, meaning no two systems looked quite the same.

### The Web-Based Transition (2000s-2010s)

As internet technologies matured, BMS interfaces moved to web browsers. This brought several advantages:

- Access from any computer on the network
- No specialized software installation required
- Easier updates and maintenance
- More standardized user experience

However, early web interfaces were often slow and limited by browser capabilities of the time. Security concerns also emerged as systems became accessible remotely.

### The Mobile Revolution (2010s-Present)

Today’s BMS interfaces extend beyond desktop computers to tablets and smartphones. Modern systems offer:

- Responsive designs that adapt to any screen size
- Touch-optimized controls for field use
- Location awareness that shows nearby equipment
- Push notifications for critical alarms
- Cloud-based access from anywhere

For examples of how different BMS systems handle core control functions, check out our article on [BMS Control Fundamentals](https://hvacknowitall.com/blog/bms-control-fundamentals).

## Critical Interface Elements: What to Look For

Despite variations between manufacturers, all modern BMS interfaces share common elements. Understanding these components helps you navigate unfamiliar systems quickly.

### System Navigation

The navigation structure is your map through the building’s systems. Typically organized as a hierarchical tree, it might be arranged by:

- Building → Floor → Zone → Equipment
- System Type → Equipment → Components
- Mechanical Systems → Electrical Systems → Security

The navigation panel is usually on the left side of the screen. Look for expand/collapse icons (+ or -) to reveal deeper levels.

### Equipment Graphics

These visual representations show the status of mechanical systems. Look for:

- Animated components (spinning fans, opening valves)
- Color-coded status indicators (green = normal, red = alarm)
- Real-time data values overlaid on equipment
- Interactive elements you can click for more detail

In most systems, right-clicking on components reveals additional options like commanding, trending, or viewing properties.

### Alarm Management

Alarm displays show current and historical issues requiring attention. Key features include:

- Severity indicators (critical, warning, notification)
- Acknowledgment status (new, acknowledged, returned to normal)
- Filtering options to focus on specific systems or alarm types
- Detailed descriptions and recommended actions

Effective alarm management is crucial—when everything becomes an “alarm,” technicians develop alarm fatigue and start ignoring notifications.

### Trend Analysis

Trend graphs display how values change over time, essential for diagnosing intermittent issues and identifying patterns. Look for:

- Multi-variable graphing capabilities
- Flexible time range selection
- Export options for further analysis
- Comparison features for similar equipment

To understand how these interfaces connect to the underlying network infrastructure, see our article on [BMS Network Architecture](https://hvacknowitall.com/blog/bms-network-architecture-communication).

## Interface Efficiency Tips for HVAC Technicians

The difference between a BMS novice and expert isn’t just knowledge—it’s efficiency. Here’s how to navigate interfaces like a pro:

### 1. Master the Search Function

Most modern BMS interfaces include powerful search capabilities. Instead of clicking through nested menus, search for specific:

- Room numbers or names
- Equipment tags
- Point types (temperature, pressure, etc.)
- Alarm conditions

Example: Rather than navigating through Building → Floor 3 → East Wing → VAV-3-12, simply search for “VAV-3-12” or “Room 315 temp.”

### 2. Learn Keyboard Shortcuts

Power users rely on keyboard shortcuts to work quickly:

- F5 to refresh data
- Ctrl+F to find text on the current page
- Tab to move between fields
- Esc to cancel operations or close dialogs

Each system has its own shortcuts—look for a “Help” section that lists them.

### 3. Use Multi-Window Techniques

Open multiple windows or tabs to compare different systems simultaneously:

- View the AHU and its VAV boxes side-by-side
- Compare similar equipment performance
- Keep alarm lists visible while troubleshooting

Most web-based systems support this natively; older applications might require specific “new window” commands.

### 4. Create Personalized Views

Many systems allow customized dashboards showing your most-used information:

- Group frequently accessed equipment
- Configure multi-trend graphs for key parameters
- Save custom filter settings for alarms
- Create shortcut links to common tasks

Spending time setting up these dashboards pays dividends in daily efficiency.

### 5. Leverage Mobile Features

When using tablet or smartphone interfaces:

- Use QR codes or NFC tags to quickly access equipment pages
- Take advantage of location-based filtering
- Configure notifications for critical systems
- Save offline documentation for areas with poor connectivity

## Mastering Any Interface

Regardless of the specific BMS you encounter, these strategies will help you quickly become proficient:

1. **Start with Navigation**: Spend 10 minutes exploring the menu structure. Where are alarms? Trends? Graphics? Schedules?
2. **Find the Search**: Almost every modern BMS has search functionality. It’s often faster than clicking through menus.
3. **Learn the Nomenclature**: Every building has a point naming convention. Decode it early. (AHU1.SAT = Air Handler 1, Supply Air Temperature)
4. **Master Right-Click**: Many functions hide in right-click context menus. Try right-clicking on graphics, point names, and values.
5. **Use Help Functions**: Most systems have built-in help. F1 is your friend when stuck.
6. **Take Screenshots**: Document complex navigation paths or useful screens for future reference.
7. **Ask Questions**: Building operators often know shortcuts and tricks not found in manuals.

## Your Interface Journey

BMS interfaces have evolved from cryptic command lines to intuitive mobile apps, yet each generation builds upon the last. Understanding this evolution helps you adapt to any system—whether it’s a 30-year-old text-based interface or cutting-edge AI-powered dashboard.

Remember, the interface is just a window into the mechanical systems you already understand. The same troubleshooting logic applies whether you’re reading a gauge on a pipe or a value on a screen. The difference is that modern interfaces provide more data, more quickly, from more locations than ever before.

As interfaces continue evolving, stay curious. Each new feature—from mobile access to voice control—is designed to help you work more efficiently. Embrace these tools while maintaining your fundamental HVAC knowledge, and you’ll thrive in an increasingly digital trade.

The next time you sit down at an unfamiliar BMS workstation, take a breath. You understand HVAC systems. You understand troubleshooting. The interface is just another tool in your toolkit—one that becomes more powerful as you master its capabilities.

For a comprehensive introduction to building automation systems, check out our [BMS Basics](https://hvacknowitall.com/blog/bms-basics-hvac-technician-guide) article.

--------------------------------------------------

# ID: 5940

## Title: BMS Network Architecture: How Complex HVAC Control Systems Communicate

## Type: blog_post

## Author: Ben Reed

## Publish Date: 2025-06-05T13:36:17

## Word Count: 1298

## Categories: Automation

## Tags: BACnet protocol, BMS architecture, BMS networks, building automation networks, building level controllers, Ethernet BMS, field controllers, HVAC communication protocols, LonWorks, Modbus communication, network troubleshooting, protocol analyzers, RS-485 troubleshooting

## Permalink: https://hvacknowitall.com/blog/bms-network-architecture-communication

## Description:
You’re standing in front of a BMS workstation, watching as hundreds of data points update in real-time. Temperature readings from VAV boxes, valve positions from the chiller plant, fan speeds from air handlers—all flowing seamlessly across the screen. But when something goes wrong and those numbers stop updating, where do you even begin troubleshooting?

For many HVAC technicians, the network side of building automation feels like black magic. You’re comfortable with sensors, actuators, and control logic, but when someone mentions “MS/TP trunk” or “IP backbone,” your confidence wavers. The truth is, understanding BMS network architecture isn’t just for IT specialists—it’s becoming essential knowledge for modern HVAC technicians.

Let’s demystify how building control systems communicate, giving you the confidence to troubleshoot network issues and understand the digital highways that connect your mechanical systems.

## The Three-Tier Architecture: Understanding the Hierarchy

Think of a BMS network like a corporate organization chart. Just as a company has executives, managers, and workers, a building automation system has three distinct levels, each with specific responsibilities.

### Supervisory Level: The Executive Suite

At the top sits the supervisory level—the CEO of your building automation system. This layer includes:

- **Servers and Workstations**: The main computers running BMS software, storing historical data, and providing user interfaces
- **Web Servers**: Enabling remote access through browsers
- **Database Servers**: Storing trends, alarms, schedules, and configuration data
- **Integration Servers**: Connecting to enterprise systems and third-party applications

When you’re sitting at the BMS computer changing schedules or viewing graphics, you’re interacting with the supervisory level. This is where the big decisions happen—energy optimization algorithms, demand response strategies, and system-wide coordination.

**Common Issues at This Level:**

- Server crashes or software freezes
- Database corruption
- Network connectivity to the building level
- User authentication problems

### Building Level: Middle Management

The building level controllers are your middle managers. Also called primary controllers or automation engines, these devices coordinate operations across multiple pieces of equipment. An automation engine might manage several air handlers, a central plant, or an entire floor of VAV boxes.

**Key Characteristics:**

- More powerful processors and memory than field controllers
- Advanced programming capabilities
- Multiple communication ports supporting different protocols
- Often include local I/O for critical equipment

These controllers can make complex decisions like determining optimal start times, coordinating economizer operation, or implementing demand limiting strategies.

### Field Level: The Front Lines

Field controllers are your worker bees. A VAV controller manages one box, an AHU controller manages one air handler, and a chiller controller manages one chiller. They execute their specific control sequences based on commands from above and local sensor inputs.

**Key Characteristics:**

- Limited memory and processing power
- Focused on specific equipment or zones
- Can operate independently if communication is lost
- Direct physical connection to sensors and actuators

## Understanding Communication Protocols: The Languages of BMS

If the three-tier architecture is the organizational structure, protocols are the languages these devices use to communicate. Let’s examine the three most common protocols you’ll encounter.

### BACnet: The Universal Translator

Building Automation and Control Network (BACnet) was developed by ASHRAE specifically for building automation. Think of it as the “common tongue” of the BMS world.

**How BACnet Works:**

- Uses “objects” to represent data points (like Analog Input for temperature)
- Each object has standard properties (present value, status, alarms)
- Devices “speak” using standard services (read property, write property)

**BACnet Variants You’ll See:**

- **BACnet IP**: Runs over Ethernet networks, fast and IT-friendly
- **BACnet MS/TP**: Master-Slave/Token-Passing over RS-485, common for field devices
- **BACnet/SC**: Secure Connect, the newest variant with built-in cybersecurity

**Practical BACnet Troubleshooting:** When a BACnet device won’t communicate:

1. Check physical connections (wires, polarity, termination resistors)
2. Verify network settings (device ID, baud rate, MAC address)
3. Use discovery tools to see if the device is visible on the network
4. Check for duplicate device IDs (a common issue)

### Modbus: The Industrial Veteran

Modbus is an older protocol but remains widely used, especially for integrating equipment like boilers, chillers, and VFDs. It’s simple but effective.

**How Modbus Works:**

- Uses “registers” to store data values
- Operates on a master-slave basis, where one device polls the others
- Minimal overhead, making it efficient for simple devices

**Modbus Variants:**

- **Modbus RTU**: Serial communication over RS-485
- **Modbus TCP**: Runs over Ethernet networks

**Practical Modbus Troubleshooting:**

1. Verify register addresses (they vary by manufacturer)
2. Check communication settings (baud rate, parity, stop bits)
3. Ensure proper termination on RS-485 networks
4. Look for address conflicts (each device needs a unique address)

### LonWorks: The Comprehensive Alternative

LonWorks (or LON) is a comprehensive protocol developed by Echelon Corporation. Though less common in new installations, many existing buildings use LonWorks.

**How LonWorks Functions:**

- Uses “Standard Network Variable Types” (SNVTs) for data exchange
- Peer-to-peer architecture allows any device to communicate with any other
- Devices use “service pins” for addressing and configuration

**Practical LON Troubleshooting:**

1. Check Neuron IDs and addresses
2. Verify proper network termination
3. Use network management tools to check device status
4. Look for channel traffic issues (overloaded networks)

## Physical Network Infrastructure: The Highways and Byways

Now that we understand the languages, let’s look at the physical infrastructure carrying these communications.

### Ethernet: The Information Superhighway

Modern BMS systems increasingly use standard Ethernet for communication. This is the same technology used for office networks.

**Key Characteristics:**

- High speed (typically 100Mbps to 1Gbps)
- Star topology with switches and routers
- Can carry multiple protocols simultaneously (BACnet IP, Modbus TCP, etc.)
- Compatible with standard IT infrastructure

**Common Applications:**

- Supervisory level communication
- Building level controllers
- IP-based field controllers
- Integration with other building systems

### RS-485: The Reliable Back Road

RS-485 is a robust serial communication standard used extensively in building automation, especially for field-level devices.

**Key Characteristics:**

- Multi-drop bus topology (devices connected in series)
- Typically runs at lower speeds (9600 to 76800 baud)
- Requires proper termination at each end
- Can span long distances (up to 4000 feet)

**Common Applications:**

- BACnet MS/TP networks
- Modbus RTU communication
- Connecting field controllers to building level controllers

For a deeper dive into the user interfaces that sit on top of these networks, check out our article on [BMS User Interfaces](https://hvacknowitall.com/blog/bms-user-interfaces-dashboards).

## Practical Network Troubleshooting for HVAC Techs

When network issues arise, follow this systematic approach:

1. **Determine the scope**: Is it affecting one device, a group of devices, or the entire system?
2. **Check physical connections**: Look for loose wires, improper terminations, or damaged cables.
3. **Verify power**: Ensure all network devices have proper power.
4. **Check network settings**: Verify addresses, baud rates, and other configuration parameters.
5. **Use diagnostic tools**: Network analyzers can help identify communication errors.
6. **Isolate the problem**: Disconnect segments of the network to locate the issue.
7. **Consult documentation**: System architecture diagrams are invaluable for troubleshooting.

For more details on BMS control fundamentals that rely on these networks, read our [BMS Control Fundamentals](https://hvacknowitall.com/blog/bms-control-fundamentals) article.

## Building Your Network Troubleshooting Toolkit

Every BMS technician should have these essential tools:

- **Multimeter**: To check power, continuity, and termination resistors
- **Network Analyzer**: To monitor network traffic and identify errors
- **Protocol Analyzer**: To decode and inspect messages on the network
- **Laptop with BMS Software**: To access and configure devices
- **Network Documentation**: Keep updated diagrams of your system architecture

Understanding BMS network architecture might seem daunting at first, but it follows logical principles that build on your existing HVAC knowledge. By mastering these concepts, you’ll be able to troubleshoot problems more effectively and provide more comprehensive service to your customers.

For those just starting with building automation systems, our [BMS Basics](https://hvacknowitall.com/blog/bms-basics-hvac-technician-guide) article provides an excellent foundation for understanding the entire ecosystem.

--------------------------------------------------

# ID: 5939

## Title: BMS Control Fundamentals: How to Navigate the Backend of Building Automation

## Type: blog_post

## Author: Ben Reed

## Publish Date: 2025-06-05T13:22:40

## Word Count: 1040

## Categories: Automation

## Tags: analog inputs, BMS controls, BMS programming, building automation troubleshooting, control logic, control sequences, digital outputs, HVAC automation, HVAC control fundamentals, PID loops, sequence of operations, smart building controls, VAV troubleshooting

## Permalink: https://hvacknowitall.com/blog/bms-control-fundamentals

## Description:
You’ve mastered the mechanical side of HVAC—compressors, motors, refrigerant circuits, and airflow. But when it comes to the digital brains controlling these systems, things get fuzzy. What exactly happens behind those colorful graphics on the BMS screen? How do control sequences actually work? And most importantly, how can you troubleshoot them when things go wrong?

In this article, we’ll peek behind the curtain of building automation and break down the fundamental control concepts in language that makes sense to HVAC technicians. Once you understand these basics, you’ll be able to approach any BMS system with confidence—whether it’s a brand-new installation or a 20-year-old legacy system.

## The Core Building Blocks of BMS Control

Every BMS, regardless of manufacturer, operates on the same core principles. Think of these as the fundamental “HVAC laws” of the digital world:

### 1. Inputs and Outputs: The Controller’s Senses and Muscles

Just like a technician uses their senses to gather information and their hands to make adjustments, a BMS controller has inputs and outputs:

**Inputs (The Senses)**:

- **AI (Analog Input)**: Reads variable values like temperature, humidity, pressure, or CO2. These are your temperature sensors, pressure transducers, etc.
- **DI (Digital Input)**: Reads binary (on/off) states like switch positions, alarms, or status indicators. These are your filter switches, high-limit cutouts, etc.

**Outputs (The Muscles)**:

- **AO (Analog Output)**: Controls modulating devices like valve positions, damper positions, or fan speeds.
- **DO (Digital Output)**: Controls binary devices like relays, contactors, or on/off valves.

Here’s a practical example: A VAV box controller might have an AI for space temperature, a DI for occupancy sensor, an AO for damper position, and a DO for the reheat valve. The controller reads the inputs, runs its control logic, and adjusts the outputs accordingly.

### 2. Control Loops: Making Decisions

Once a controller has information from its inputs, it needs to decide how to adjust its outputs. This is where control loops come in—the decision-making algorithms that maintain setpoints.

The most common type is the **PID loop** (Proportional, Integral, Derivative). Don’t let the technical name scare you. Here’s what it means in practical terms:

- **Proportional (P)**: How strongly should the system react to the current error? If the space is 5°F too warm, how much should we open the cooling valve?
- **Integral (I)**: How should the system handle persistent errors over time? If the space has been 2°F too cool for the last hour, we need to reduce heating output.
- **Derivative (D)**: How should the system react to rapid changes? If the temperature is rising quickly, we need to increase cooling before we overshoot.

Think of P as the present, I as the past, and D as the future trend. Together, they provide responsive, stable control that can handle most HVAC applications.

### 3. Sequences of Operation: The Playbook

A sequence of operation is exactly what it sounds like—a step-by-step playbook for how the system should behave under different conditions. It’s like a detailed job plan for your BMS.

For example, a simple AHU sequence might read:

1. On a call for heating (space temp  cooling setpoint):

- Check outdoor air temperature
- If suitable for economizing, modulate outdoor air damper to maintain setpoint
- If mechanical cooling required, open chilled water valve
- Increase fan speed as needed to maintain setpoint

For more advanced BMS applications, sequences get much more complex, handling multiple operating modes, various failure scenarios, and optimization strategies. In large buildings, you might see thousands of lines of sequence documentation.

## Practical Application: Troubleshooting Control Issues

Now let’s apply these fundamentals to real-world troubleshooting:

### Scenario 1: Zone Temperature Won’t Reach Setpoint

1. **Check Inputs**: Is the temperature sensor reading correctly? Compare BMS reading with a calibrated thermometer.
2. **Check Outputs**: Is the system commanding the correct output? Check valve/damper positions or stages of heating/cooling.
3. **Check Control Loop**: Is the PID loop tuned properly? An aggressive loop might cause hunting, while a sluggish one might never reach setpoint.
4. **Check Sequence Logic**: Is the system in the correct mode? Verify that it’s calling for heating or cooling as expected.

### Scenario 2: System Hunting or Oscillating

If a system constantly overshoots and undershoots its setpoint, the control loop is likely poorly tuned:

1. Reduce the proportional gain to make the system less aggressive
2. Adjust the integral time to slow down the accumulation of error
3. Check for delays in the mechanical system that might be causing feedback issues

For more advanced troubleshooting techniques and detailed BMS network architecture, see our article on [BMS Network Communications](https://hvacknowitall.com/blog/bms-network-architecture-communication).

## Beyond Basic Control: Smart Building Features

Modern BMS systems go well beyond simple control loops, incorporating advanced features like:

- **Trend Logging**: Recording historical data for analysis and troubleshooting
- **Fault Detection and Diagnostics**: Automatically identifying potential issues
- **Demand Response**: Adjusting operation based on utility grid demands
- **Predictive Maintenance**: Using data patterns to predict equipment failures
- **Energy Optimization**: Dynamically adjusting setpoints and schedules to minimize energy use

These advanced features build upon the fundamental control principles we’ve discussed. To dive deeper into the user interface side of BMS, check out our guide on [BMS User Interfaces](https://hvacknowitall.com/blog/bms-user-interfaces-dashboards).

## Bridging Your HVAC Knowledge to BMS

The best BMS technicians combine deep HVAC knowledge with control system understanding. When you encounter a new BMS, focus on these questions:

1. What are the inputs? (What is the system measuring?)
2. What are the outputs? (What can the system control?)
3. What is the sequence? (How should it behave?)
4. What are the setpoints? (What is it trying to achieve?)

Your HVAC knowledge already helps you understand how the equipment should operate. BMS control fundamentals simply add the layer of how that operation is automated. Once you bridge this gap, you’ll find that BMS work becomes much more intuitive, allowing you to apply your existing expertise to this growing field.

For an introduction to building automation systems, start with our [BMS Basics](https://hvacknowitall.com/blog/bms-basics-hvac-technician-guide) article to get a complete overview of the industry.

--------------------------------------------------

# ID: 5929

## Title: BMS Basics: Essential Building Management Systems Guide for HVAC Technicians

## Type: blog_post

## Author: Ben Reed

## Publish Date: 2025-06-05T12:44:37

## Word Count: 960

## Categories: Automation

## Tags: BAS, BMS basics, BMS terminology, building automation systems, building controls introduction, building management system, DDC systems, EMCS, energy management, HVAC automation, HVAC career advancement, HVAC controls, HVAC technician skills

## Permalink: https://hvacknowitall.com/blog/bms-basics-hvac-technician-guide

## Description:
So, you can diagnose a faulty compressor with your eyes closed, and you’ve replaced more capacitors than you can count. But then you walk into a mechanical room and see a wall full of controllers, sensors, and network cables—the building management system. Your stomach drops. Where do you even start?

![A BMS Control panel for mechanical systems. Source: Sander Mechanical](https://hvacknowitall.com/wp-content/uploads/2025/06/image.png)

If this sounds familiar, you’re not alone. The jump from traditional HVAC work to building automation can feel like learning a new language. But here’s the truth: BMS work isn’t just different—it’s a whole new way of thinking about HVAC systems. Instead of reacting to problems, you’re preventing them. Instead of working on one unit at a time, you’re orchestrating an entire building.

Let’s bridge that gap and explore what daily life looks like when you add building automation to your skillset.

## Decoding the Alphabet Soup: BMS, BAS, DDC, and EMCS

First, let’s clear up the confusion around terminology. When you step into the controls world, you’ll hear these acronyms thrown around interchangeably, but there are subtle differences worth understanding:

- **BMS (Building Management System)**: Think of this as the master control center. It’s typically the software interface that building operators use to monitor and control multiple building systems—not just HVAC, but also lighting, security, and fire alarms. When someone says “check the BMS,” they’re usually referring to the computer screen showing all the pretty graphics.
- **BAS (Building Automation System)**: This is the physical network of controllers, sensors, and actuators that actually do the work. While BMS is the brain (software), BAS is the nervous system (hardware). In the HVAC world, BAS focuses specifically on automating heating, cooling, and ventilation.
- **DDC (Direct Digital Control)**: This refers to the computerized control method that replaced old pneumatic systems. Instead of air pressure controlling dampers and valves, microprocessors make decisions based on digital inputs. It’s the “how” of modern control systems.
- **EMCS (Energy Management Control System)**: This is essentially a BAS with a focus on energy optimization. You’ll see this term more in government and military facilities where energy monitoring is critical.

![Overview of building automation components](https://hvacknowitall.com/wp-content/uploads/2025/06/BMS-Simple-Overview-1024x512.png)

Here’s the practical takeaway: whether your customer calls it BMS, BAS, or “that computer thing,” they’re all talking about the same concept—automated building control. Don’t get hung up on the terminology; focus on understanding what the system does.

## A Day in the Life: Traditional HVAC vs. BMS Work

Let me paint you a picture of how your workday changes when you transition into building automation.

**Traditional HVAC Morning**: You check your service calls for the day. First stop: an office building where the tenant says it’s too hot. You arrive, check the thermostat, test the unit, find a bad capacitor, replace it, and move on to the [next call](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/A-General-Guide-To-HVACR-Troubleshooting-en165r). Physical work, clear problems, straightforward solutions.

**BMS Technician Morning**: You arrive at the same office building, but instead of going to the hot office, you head to the control room. You pull up the BMS and see that VAV box 3-14 isn’t responding to commands. The space temperature is 78°F, but the cooling valve shows 0% open. You check the trend logs—this started happening Tuesday at 2:47 PM. You head to the VAV box, find a failed actuator, but before replacing it, you notice three other VAV boxes showing similar patterns. You dig deeper and discover the building had a power surge Tuesday afternoon. Now you’re preventing three future service calls, not just fixing one.

![A building Control panel](https://hvacknowitall.com/wp-content/uploads/2025/06/Building-Control-Panel-With-Laptop-768x1024.png)

See the difference? Traditional HVAC work is often reactive—fix what’s broken. BMS work is detective work—understand the whole story and prevent future problems.

## The Mental Shift: From Standalone to System Thinking

The biggest adjustment when moving into BMS work isn’t learning new tools—it’s changing how you think about HVAC systems.

**Traditional Thinking**: “This rooftop unit isn’t cooling properly.”

**BMS Thinking**: “This rooftop unit isn’t cooling properly. How is this affecting the other four units? Is the building pressure going negative? Are we wasting energy trying to condition air that’s immediately being exhausted?”

This system-level thinking becomes second nature, but it takes time to develop. You start seeing buildings as living organisms where everything is connected, not just a collection of individual equipment.

## Your New Daily Routine: What BMS Techs Actually Do

Let’s break down what you’ll actually be doing day-to-day as a BMS technician:

**Morning Routine (30-45 minutes):**

- Review overnight alarm reports
- Check trend logs for anomalies
- Respond to any urgent tenant complaints
- Plan your day based on preventive maintenance schedules

**Field Work (4-5 hours):**

- Calibrate sensors (temperature, humidity, CO2, pressure)
- Test and adjust control sequences
- Troubleshoot communication issues between controllers
- Commission new equipment into the existing BMS
- Train building operators on system changes

**Computer Work (2-3 hours):**

- Modify control programming for seasonal changes
- Create or adjust graphic interfaces for building operators
- Analyze trend data to identify energy-saving opportunities
- Generate reports for building management

## Making the Transition: Your Next Steps

Ready to expand your skills into building automation? Here’s where to start:

1. **Learn the fundamentals of [BMS control systems](https://hvacknowitall.com/blog/bms-control-fundamentals)** – understanding control loops, sequences, and logic is essential
2. **Dive into [network communications](https://hvacknowitall.com/blog/bms-network-architecture-communication)** – discover how all these systems talk to each other
3. **Familiarize yourself with [BMS interfaces](https://hvacknowitall.com/blog/bms-user-interfaces-dashboards)** – learn to navigate the software side effectively
4. **Ask to shadow experienced BMS technicians** – nothing beats [hands-on learning](https://creators.spotify.com/pod/profile/hvacknowitall/episodes/HVAC-Training-Implementation-wLenny-Diaddario-and-Chris-Harris-e2khoav)

BMS work isn’t just a skill addition—it’s a [career enhancement](https://www.youtube.com/watch?v=fvEeWDgEWUE) that can open doors to higher-paying positions and more interesting problems to solve. The transition requires patience and persistence, but the payoff is worth it: you’ll be at the cutting edge of [where HVAC technology is heading](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/Whats-To-Come-In-2025-For-HVAC-Professionals-e2sng6o).

--------------------------------------------------

# ID: 5907

## Title: Refrigeration &amp; AC Condensers: The Critical Heat Dissipaters in HVAC Systems

## Type: blog_post

## Author: Julian Finbow

## Publish Date: 2025-05-20T18:12:26

## Word Count: 1491

## Categories: Air Conditioning

## Tags: adiabatic condensers, air-cooled condensers, coaxial, Commercial Refrigeration, condenser maintenance, condenser pressure, condenser splitting, condensers, cooling tower, de-superheating, discharge line, ECM motors, evaporative condensers, flash gas, fluid coolers, forced convection, glycol-cooled, head pressure control, heat dissipation, heat transfer, HVAC, industrial refrigeration, liquid line, microchannel, natural convection, plate heat exchanger, refrigerant flow, refrigeration, refrigeration cycle, shell and tube, subcooling, water-cooled condensers

## Permalink: https://hvacknowitall.com/blog/refrigeration-ac-condensers-the-critical-heat-dissipaters-in-hvac-systems

## Description:
The **Condenser** is one of the Four main Components of Refrigeration and Air Conditioning. The other three Components are the **[Evaporator](https://hvacknowitall.com/blog/understanding-evaporator-coils-types-function-troubleshooting-tips)**, **[Compressor](https://hvacknowitall.com/blog/the-inverter-compressor)**, and **[Metering Device](https://hvacknowitall.com/blog/adaptive-vs-fixed-expansion-valves)**.

The Condenser’s job is to dissipate both the heat absorbed in the Evaporator and the heat gained in the Compressor during compression.

In the refrigeration cycle, superheated refrigerant vapor enters the Condenser from the Discharge Line. The Condenser then performs three primary functions:

1. **De-superheating**: Cooling the superheated vapor to its saturation temperature
2. **Condensation**: Changing the refrigerant from vapor to liquid state while maintaining constant temperature and pressure
3. **Subcooling**: Further cooling the liquid refrigerant below its condensing temperature

Note: Subcooling (at the Condenser’s outlet/Liquid Line) increases Refrigeration Effect, helps mitigate Flash Gas, and assists in providing a full column of Liquid Refrigerant to the Metering Device.

Condensers usually have their Refrigerant inlet physically at their top from the Discharge Line and have their outlet at the bottom to the Liquid Line or Condensate Line (for systems that employ Receivers). Some Condensers, however, have their inlet at the bottom, side, or other orientation to assist with equal Condenser circuit distribution.

## Condenser Accessories

To assist with Condenser Operation, there are different accessory devices that are commonly used to help regulate its operation. The target with any type of Condenser control is maintaining the system’s intended Condensing Pressure.

Condensers often employ a fan, and methods to control this include Fan Cycling Controls, and Variable Speed Drives or ECM’s (Electronically Commutated Motors). Condenser fans can also simply be on/off. Condensers may have a single fan or multiple which can be staged.

To assist with maintaining sufficient Condenser Pressure during varying loads and reduced Outdoor Ambient Temperature during Winter in cold climates, Air Louvres, or Condenser Flooding Valves may be used.

Note: Condenser Splitting is a method used in Supermarket Refrigeration that utilizes “Valving” to split the Condenser’s physical size based on load and ambient conditions.

![Condenser Cooling Medium](https://hvacknowitall.com/wp-content/uploads/2025/05/refigeration-ac-condensers-2.png)

Condensers that are Liquid Cooled can utilize a spring-actuated “Water” Pressure regulator to vary the flow of the Condenser Cooling Medium to maintain Head Pressure.

## Air-Cooled Condensers

Air-Cooled Condensers employ Ambient Air (usually outdoor air), which is at a lower temperature than the temperature at which the Refrigerant Condenses. Air-Cooled Condensers often have a fan to assist with increasing the heat transfer rate.

Note: all types of Condenser Coils may be manufactured from Copper, Aluminum, Steel, or Stainless Steel, depending on their application.

### Natural Convection

The Condenser on most home fridges is a Natural Convection Air-Cooled Condenser, which does not use a fan to expedite heat transfer. With not too much heat to get rid of, applications like this are a good candidate for manufacturers to save costs on a part, while eliminating the potential failure of a fan motor.

Note: on Domestic appliances, Condensers may be bare tubes joined to thin steel wires. The wires stabilize the coil and increase its Surface Area.

## Forced Convection

**Forced Convection** is by far the most common type of Air-Cooled Condenser. It can utilize a single or multiple fans, which can be controlled by the methods mentioned above in “*Condenser Accessories*”. **Note**: Forced Convection Condensers almost always have their tubes joined to **Fins**, which increases their surface area. The increased surface area allows for better heat dissipation from the coil. The article’s first image and the image below both show Condensing Units which utilize **Finned Tubes** on their Condensers.

![A typical Forced Convection Condenser](https://hvacknowitall.com/wp-content/uploads/2025/05/refigeration-ac-condensers-3.png)

## Water-Cooled Condensers

Water-Cooled Condensers have the benefit of being cooled by “Two Mediums”: water and air. Depending on their Construction, water usually transfers its energy somewhere “Inside” of the refrigerant passage, while the surrounding air allows heat transfer on the “Outside” surface of the refrigerant.

Note: instead of water, any Water-Cooled Condenser could instead be cooled with Glycol, depending on the application.

### Coaxial Tube-in-Tube

The Tube-in-Tube part of this name refers to the Water Coil being physically inside the Refrigerant Coil. The air surrounding the Refrigerant Coil’s ambient provides additional heat transfer for the Condenser. The Coaxial part of this Condenser’s name comes from the Water Coil following the Refrigerant Coil on the same axis. These are commonly run in a circular shape and installed on smaller Condensing Units. Their application is often for systems which serve Low Temperatures, and are required to rid much Enthalpy from a high Heat of Compression.

Note: most Water-Cooled Condensers use “Countercurrent Flow”. The Refrigerant and Water will flow in opposite directions to maximize heat transfer.

### Plate Condensers

Plate Condensers have a large number of channels where there is heat exchange between the refrigerant and the water. This Condenser type is also known as a brazed plate heat exchanger (BPHX).

When [charging refrigeration systems](https://hvacknowitall.com/blog/charging-refrigeration-systems) with plate condensers, special care must be taken to avoid freezing the heat exchanger.

![An example of a Shell and Tube Condenser](https://hvacknowitall.com/wp-content/uploads/2025/05/refigeration-ac-condensers-4.png)

### Shell and Tube Condensers

Large-capacity condensers typically found in chillers, featuring a cylindrical shell holding liquid Refrigerant, which surrounds the Condenser’s Tubes. The Tubes are filled with water, which flows in and out of the chiller. The usual way in which this “Condenser Water” is cooled is with a Cooling Tower (an accessory to this Water-Cooled Condenser).

Note: a Shell and Tube Condenser also functions as a refrigerant Receiver, with its large capacity to store Liquid Refrigerant.

## Other Condenser Types

### Evaporative Condensers

Evaporative Condensers are a hybrid between Air and Water-Cooled condensers. They are unique in that both the air and water are cooling the Refrigerant Condenser from its outside. The image below shows both existing and mid-construction (on the right: not yet tied into the system) Evaporative Condensers. The Refrigerant Piping’s inlet is at the top, and its Condensate Drain is at the bottom (yellow on the left). The Water Inlet is at the top (in green on the left) and feeds spray nozzles to distribute the water over the coil. This water partially Evaporates as it falls, which assists with its cooling effect. The water collects in the “Sump” at the Condenser’s bottom, and follows a drain pipe back towards the Condenser Water Tank and Condenser Water Pump.

This Condenser type often employs a fan to assist in heat transfer. Their common application is Ammonia Systems. This [evapco Piping Guide](https://www.evapco.com/sites/evapco.com/files/2018-02/EvapcoPiping%20EvapCond131A.pdf) offers more information on Evaporative Condensers (this article’s second image is from this document).

For more detailed information on evaporative condensers in industrial applications, refer to the [HVAC Know It All podcast episode on industrial refrigeration](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/Industrial-Refrigeration-wJoshua-Rees-eocn0a).

![An example of a CO2 system with Adiabatic Condensers](https://hvacknowitall.com/wp-content/uploads/2025/05/refigeration-ac-condensers-5.png)

### Adiabatic Condensers

Adiabatic Condensers are commonly used on CO2 systems. Since CO2’s Refrigerant States are unique, this Condenser may instead function as a Gas Cooler depending on outdoor and system conditions.

The Adiabatic Condenser is unique in utilizing a Wetted Pad to “Pre-Cool” the entering air. This gives the Condenser function an added efficiency while allowing good results in high ambient conditions. Further details can be found in [evapco’s product guide for their Adiabatic Condensers](https://www.evapco.com/products/condensers-air-cooled/eco-air-series-v-configuration-adiabatic-condenser).

These systems are becoming more common in commercial refrigeration applications, particularly in [supermarket installations](https://hvacknowitall.com/blog/hvac-retrofits-a-guide-to-commercial-system-upgrades).

### Glycol-Cooled Condensers

Instead of water, a Refrigerant Condenser may be cooled by Glycol. Since Glycol has a lower rate of heat transfer compared to water, the use of a Glycol-Cooled Condenser occurs for sites with limited availability of water supply.

After serving the Condenser (usually indoors), the Glycol will be pumped to a Dry Cooler (usually outdoors) to allow the Glycol to cool down in a coil that is commonly of a finned type, and assisted by fans.

Note: depending on the manufacturer, Dry Coolers may instead be referred to as Fluid Coolers.

## Common Types Of Condensers

Common Types Of Condensers include:

- Traditional copper coil with aluminum fins
- Micro Channel Condenser
- Condenser Bundle
- Coaxial Coil
- Brazed Plate Heat Exchanger

Microchannel condensers represent one of the most significant advancements in condenser technology, featuring multiple flat tubes with small channels for improved heat transfer efficiency and reduced refrigerant charge requirements.

## Practical Applications and Maintenance Considerations

Proper condenser maintenance is essential for system efficiency and longevity. Key maintenance tasks include:

1. Keeping air-cooled condenser coils clean and free of debris
2. Ensuring adequate airflow around the condenser
3. Maintaining proper water treatment for water-cooled systems
4. Monitoring subcooling to verify proper condenser operation
5. Checking for [non-condensable gases](https://hvacknowitall.com/blog/non-condensables-in-a-refrigeration-circuit) that can reduce efficiency

Proper [condensate management](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/Condensate-Management-wSean-Holloway-e1nfm3l) is also critical, particularly in high-humidity environments where condensation rates are significant.

## Summary

Condensers, in basic principle, are a simple Component of the Refrigeration System. There are, however, many different types, so it is helpful to be knowledgeable of this when working on a variety of equipment. Awareness of unique Condenser applications assists in setting up to perform Service, Maintenance, and Construction on Refrigeration and AC Systems.

For hands-on professionals, developing expertise in condenser technology is critical as we continue to see advancements in [HVAC technology and efficiency standards](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/HVAC-Knowledge-Gaps-wKen-Perkins-e2cgtpm).

--------------------------------------------------

# ID: 5723

## Title: HVAC Belt Replacement: A Comprehensive Technical Guide for Service Professionals

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2025-04-17T14:24:04

## Word Count: 1973

## Categories: Components, HVAC Maintenance

## Tags: belt deflection, belt inspection, belt installation, belt tensioning, Commercial HVAC, HVAC belt replacement, HVAC maintenance, HVAC repairs, HVAC safety, HVAC service, HVAC troubleshooting, mechanical systems, motor pulleys, preventative maintenance, pulley alignment, rooftop units, sheaves, system efficiency, technical guide, V-belts

## Permalink: https://hvacknowitall.com/blog/hvac-belt-replacement-a-step-by-step-guide-for-technicians

## Description:
I remember the first time I was told to replace a belt on an exhaust fan as a new apprentice. When the journeyman handed me the belt and walked away, I couldn’t figure out how to remove the old one. Between you and I, I ended up using red tin snips to cut it off. I managed to install the new one but never admitted my struggle to my superior.

This common challenge faces many techs early in their careers. Without proper training on belt removal and installation techniques, what should be a straightforward task becomes unnecessarily complicated. This guide will solve that problem by teaching you the correct methods for removing, replacing, aligning, and tensioning belts in HVAC systemsno tin snips required.

The key to removing most HVAC belts without frustration lies in technique, not force. Here’s what experienced technicians know: many belts can be removed by pushing inward at the middle of the belt while simultaneously directing it toward the larger pulley. This simple method works effectively on equipment like rooftop units, exhaust fans, and make-up air units.

For situations where the above technique doesn’t work, you’ll need to loosen the motor mount and adjust it toward the fan housing to create sufficient slack for removal.

Before attempting any belt work, follow these essential safety protocols:

1. Turn off all power to the HVAC system completely
2. Follow proper [lockout tagout procedures](https://hvacknowitall.com/blog/general-guide-to-hvac-troubleshooting) to prevent accidental activation
3. Wear appropriate safety gear, including gloves and safety goggles
4. Wait until the belt is at a complete stop before attempting removal

This last point cannot be overstatedeven slight movement of a belt can catch your fingers and pull them through the pulley, resulting in serious injury.

### 1. Locate the Belt

Open the access panel of the HVAC unit to locate the belt. These components typically connect the motor pulley to the blower pulley and are found on blower motors or compressors.

Most access panels have labels indicating fans or moving parts are behind them. The belt will almost certainly be located there.

### 2. Inspect the Existing Belt

Before proceeding with removal, thoroughly examine the belt for:  
– Visible cracks along the edges or inner surfaces  
– Fraying or separation of material  
– Glazing (shiny surfaces indicating heat damage)  
– Excessive wear or stretching

For cogged belts, it’s often necessary to remove the belt first for proper inspection, as cracks between the cogs aren’t easily visible when installed.

### 3. Remove the Old Belt

Loosen the belt by adjusting the motor mounts or tensioning mechanism. This usually involves loosening motor mounting bolts and moving the motor toward the fan housing.

Once loosened, gently slide the belt off the pulleys. Take careful note of the belt routing patternthis is crucial for correct installation of the replacement.

When possible, consult the manufacturer’s manual for the specified belt routing diagram. If the manual isn’t available, take a photo before removal.

### 4. Understanding HVAC Belt Types

HVAC systems utilize several belt types, each with specific applications:

- **V-Belts**: Most common in HVAC equipment, with a trapezoidal cross-section that wedges into pulley grooves
- **Cogged V-Belts**: Similar to standard V-belts but with notches along the inner surface to improve flexibility and reduce heat buildup
- **Multi-Ribbed Belts**: Feature multiple small V-shaped ribs, providing better power transmission in compact spaces
- **Synchronous Belts**: Toothed belts that engage with matching grooved pulleys, eliminating slippage

Knowing which type you’re working with ensures proper replacement and performance.

### 5. Choose the Correct Replacement Belt

Ensure the replacement belt matches the original in:  
– Size code (e.g., BX50)  
– Length  
– Width  
– Type (V-belt, cogged, etc.)

However, don’t automatically assume the existing belt was correct. Verify against the unit’s specifications if possible. The wrong belt might have been installed previously, leading to premature wear or performance issues. Cross-reference the belt code with the manufacturer’s specifications when available.

### 6. Install the New Belt

Place the new belt over the motor pulley first, then work it onto the blower pulley. Ensure it’s properly seated in the grooves of both pulleys.

Exercise extreme caution during this process, especially when sliding the belt onto the blower pulley. Keep your fingers clear of the space between the belt and pulley to prevent crushing injuries.

Proper alignment is critical for preventing premature belt wear and ensuring smooth operation. Follow these steps:

![A pulley commonly found in an HVAC system](https://hvacknowitall.com/wp-content/uploads/2025/04/91cgtnCmzEL-1002x1024.jpg)

1. **Check Pulley Alignment**: Use a straight edge (like a high-quality aluminum ruler) or laser alignment tool (such as the Gates DriveAlign or Browning Laser Alignment Tool) to verify that the motor and blower pulleys are aligned. The edges of both pulleys should be parallel and in line with each other.
2. **Consider Adjustable Pulleys**: When working with an adjustable drive (motor) pulley, the outer edges sometimes won’t align with the blower pulley if the adjustment is turned out too far. In these cases, align down the center of the pulley groove rather than along the outside edge.
3. **Adjust Pulley Position**: If misalignment is detected, adjust one or both pulleys as needed. Most HVAC systems have set screws or bolts that allow you to shift the pulley along the shaft. Loosen these fasteners, reposition the pulley, and retighten securely.
4. **Verify Alignment**: After adjustments, recheck alignment with your straight edge or laser tool. The belt should lie flat and straight between the pulleys with no twists or misalignment.

Proper tensioning is essential for efficient performance and avoiding unnecessary strain on the system. Here’s how to achieve optimal tension:

### Determining and Applying Correct Tension

- Refer to the HVAC unit’s manual for specific tension requirements. If the manual isn’t available, follow this general rule: the belt should deflect approximately 1/2 inch when pressed with moderate force at its midpoint.
- Most belt manufacturers provide tensioning charts that can be referenced for precise specifications. Use a proper tensioning tool like a Gates Krikit Tension Gauge or Browning Tension Checker for accurate measurement. This precision is just as important as having the [proper diagnostic tools](https://hvacknowitall.com/blog/general-guide-to-hvac-troubleshooting) for system evaluation.

Here’s a valuable reference guide on belt tension which you can download:

[Greenheck Product Application Guide FA:127-11](https://hvacknowitall.com/wp-content/uploads/2025/04/Greenheck-Product-Application-Guide-FA127-11.pdf)[Download](https://hvacknowitall.com/wp-content/uploads/2025/04/Greenheck-Product-Application-Guide-FA127-11.pdf)

Check this video demonstration of proper belt tensioning techniques:

### Finalizing the Belt Installation

1. **Adjust Motor Position**: To increase or decrease tension, adjust the motor mounts accordingly. Loosen the motor mounting bolts slightly, then slide the motor away from the blower pulley to increase tension or closer to it for less tension.
2. **Test the Deflection**: Press the belt at its midpoint with moderate force to assess the deflection. Make adjustments until reaching the recommended deflection (typically 1/2 inch or per manufacturer specs).
3. **Secure the Motor**: Once achieving proper tension, tighten all motor mounting bolts securely to maintain the position.
4. **Run the System**: Reconnect power and run the HVAC system for a few minutes. Observe the belt operation, checking for smooth running with no slipping or excessive vibration.

After installation, measure the motor’s amperage draw to verify it falls within specifications. This crucial check, similar to those performed during [motor troubleshooting procedures](https://hvacknowitall.com/blog/troubleshooting-and-replacing-an-hvac-motor), confirms the belt isn’t causing excessive load on the motor.

Even with proper installation, belts can develop problems over time. Here’s how to diagnose and address common issues:

1. **Belt Slipping**
2. *Symptoms*: Squealing noise, reduced airflow, irregular movement
3. *Causes*: Insufficient tension, worn pulleys, oil contamination
4. *Solution*: Increase tension to specifications, replace damaged pulleys, clean oil from belts and pulleys
5. **Excessive Noise**
6. *Symptoms*: Squeaking, chirping, or rumbling sounds
7. *Causes*: Misalignment, improper tension, worn bearings
8. *Solution*: Realign pulleys, adjust tension, replace bearings if necessary
9. **Premature Wear**
10. *Symptoms*: Belt showing wear after short service period
11. *Causes*: Misalignment, incorrect tension, pulley damage, environmental factors
12. *Solution*: Check and correct alignment, verify proper tension, inspect pulleys for damage
13. **Belt Turnover**
14. *Symptoms*: Belt flips or twists in operation
15. *Causes*: Severe misalignment, incorrect belt type
16. *Solution*: Correct alignment issues, ensure proper belt type for application
17. **Routine Checks**: Inspect belts regularly for wear, damage, and proper tension. Early detection prevents unexpected failures and system downtime.
18. **Clean Pulleys**: Periodically remove dirt, debris, and oil from pulleys. Contamination accelerates belt wear and can cause slippage.
19. **Monitor Alignment**: Check alignment during maintenance visits, as vibration and normal operation can gradually shift components.
20. **Lubrication**: While belts themselves never require lubrication, keep the system’s bearings and other moving parts properly lubricated to reduce strain on the belt.
21. **Seasonal Inspections**: Make comprehensive belt inspections part of your [heating system safety checks](https://hvacknowitall.com/blog/carbon-monoxide-the-silent-killer-every-tech-should-know-how-to-handle), especially before winter when systems run continuously.
22. **Environmental Considerations**: In areas with extreme temperatures or high dust/humidity, increase inspection frequency and consider belts specifically designed for those conditions.

Precision matters in HVAC from belt tension to business intelligence. Property.com’s exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool delivers critical homeowner insights like permit history and upgrade potential right to your fingertips. Impress clients, work smarter, and secure your spot in our limited network of certified Pros. Learn more about boosting your credibility and ROI with Property.com.

Proper belt replacement, alignment, and tensioning are fundamental skills every HVAC professional should master. Following the techniques outlined in this guide will help you perform these tasks efficiently and effectivelywithout resorting to emergency tin snips.

Remember that belts are critical components in HVAC systems. Without proper belt function, there’s no airflow, which means no cooling or heating, or improper ventilation in essential spaces. By implementing these best practices, you’ll extend equipment life, improve system efficiency, and reduce callbacks.

The ability to properly handle belt replacement demonstrates the difference between an apprentice and a seasoned professionalit’s a skill worth perfecting.

],
"step": [
]

},
"mentions": [
],
"description": "Discover what's driving the DIY HVAC trend and learn effective strategies for HVAC professionals to respond, educate customers, and showcase your value in a changing market."

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/driers-and-sight-glasses"
},
"articleSection": "HVAC Components",
"keywords": "filter-drier, sight glass, HVAC components, refrigeration system, moisture indicator, desiccant, moisture removal, system contamination"

},
"datePublished": "2025-03-15T08:00:00+00:00",
"dateModified": "2025-03-15T08:00:00+00:00",
"description": "Discover how technological advances are creating opportunities for women in HVAC, the business benefits of diverse teams, and strategies for integrating female technicians into your workforce.",
"image": "https://hvacknowitall.com/wp-content/uploads/2025/03/Brandi-LadyTradies-2-770x1024.png",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/tools-tech-and-the-rise-of-lady-tradies"
},
"mentions": [
]

},
"mainEntity": {
"@type": "ItemList",
"itemListElement": [
]

--------------------------------------------------

# ID: 5604

## Title: Carbon Monoxide Testing: The Essential Guide for HVAC Technicians

## Type: blog_post

## Author: Ben Reed

## Publish Date: 2025-02-25T23:17:31

## Word Count: 2215

## Categories: Heating Systems

## Tags: carbon monoxide safety, combustion efficiency, HVAC safety, HVAC technicians

## Permalink: https://hvacknowitall.com/blog/carbon-monoxide-the-silent-killer-every-tech-should-know-how-to-handle

## Description:
## The Life-Saving Art of Carbon Monoxide Testing

Carbon monoxide (CO) kills silently. As HVAC professionals, we stand between our customers and this invisible threat. While we often focus on system efficiency and comfort, our most critical responsibility is ensuring that the equipment we service doesn’t endanger lives.

This comprehensive guide will equip you with the knowledge, protocols, and technical understanding needed for proper CO testinga skill that literally saves lives.

- CO is colorless, odorless, and deadly – just 70 ppm can be harmful
- Every HVAC tech should test for CO on ALL service calls
- Three types of CO testers: ambient testers (~$200), pump-driven analyzers (~$450), and full combustion analyzers ($600+)
- Always test: ambient air, mechanical room, appliance area, supply air, and flue gas
- CO action limits: 400 ppm (red tag)
- Document all readings for legal protection and customer safety
- Proper combustion analysis helps optimize efficiency AND safety
- Calibrate your equipment annually – uncalibrated tools put lives at risk

You don’t need massive amounts of CO to create a dangerous situation. While air normally contains about 200,000 parts per million (ppm) of oxygen, just 70 ppm of CO can start causing problems for healthy adults. At 400 ppm, you’re looking at potential unconsciousness and death within a couple of hours of exposure.

Carbon monoxide (CO) is a colorless, odorless, tasteless, and highly toxic gas that’s produced during incomplete combustion. As professional HVAC technicians, we need to understand that even at low concentrations, CO binds to hemoglobin in the blood with an affinity 200-250 times greater than oxygen, preventing oxygen from being transported throughout the body.

Here’s a quick breakdown of CO exposure effects:

- **9 ppm:** Maximum allowable concentration for short-term exposure in living environments ([ASHRAE standard 62.2](https://www.ashrae.org/technical-resources/bookstore/standards-62-1-62-2))
- **35 ppm:** Maximum allowable concentration for continuous exposure in any 8-hour period (US federal law)
- **200 ppm:** Maximum allowable concentration at any time according to [OSHA](https://www.osha.gov/laws-regs/regulations/standardnumber/1917/1917.24) (can cause headaches, fatigue, and nausea after 2-3 hours)
- **800 ppm:** Nausea and convulsions within 45 minutes and death within 2-3 hours
- **3,200 ppm:** Headaches and nausea within 5-10 minutes and death within 30 minutes

Every combustion appliance you servicefurnaces, boilers, water heaterscould potentially produce carbon monoxide. Unlike other dangers in our field, CO provides no sensory warnings. You can’t see it, smell it, or taste it, earning it the “silent killer” nickname.

The stark reality is sobering: an oversight during your service call could lead to tragedy. When a heat exchanger cracks, venting becomes compromised, or fuel/air mixtures go wrong, deadly CO can seep into living spaces where families sleep. As [professional HVAC technicians](https://hvacknowitall.com/blog/the-truth-about-furnace-tune-ups), we don’t just provide comfortwe safeguard lives.

This isn’t about upselling services or covering liability. This is about fundamental professional ethics: leaving a home safer than you found it. Every single service call, regardless of the original complaint, creates an opportunityand obligationto verify CO safety.

Having the right equipment isn’t just convenientit’s critical. Seitron’s lineup, particularly the Novo analyzer, is designed specifically for techs like us who need accurate, reliable readings.

Here’s what you should look for in your CO testing equipment:

### 1. Ambient CO Detection

- Built-in ambient monitor for immediate safety checks
- Alerts you to dangerous conditions before you even start working
- Should be carried and used on *every* service call, not just heating system repairs

### 2. Combustion Analysis Capabilities

- Measures O, CO, and CO simultaneously
- Helps you dial in that perfect combustion setup
- Calculates combustion efficiency to optimize system performance

### 3. Data Recording

- Keeps track of your readings for documentation
- Provides evidence of your proper testing procedures
- Covers you legally if questions come up later

### Comparing CO Testing Equipment

| Equipment Type | Price Range | Best For | Limitations |
| --- | --- | --- | --- |
| **Ambient Testers** | ~$200 | Quick safety checks, personal protection | Cannot test raw flue products or warm air streams |
| **Pump-driven Single Gas CO Analyzers** | $450-500 | Ambient testing, supply air testing, basic flue analysis | Limited combustion analysis capabilities |
| **Full Combustion Analyzers** | $600-2,000+ | Complete combustion analysis, efficiency optimization, comprehensive testing | Higher initial investment, requires more training |

All three types have their place in the industry, but for comprehensive safety and optimization, a full combustion analyzer provides the most complete picture of system operation.

Tools are only valuable when used correctly and consistently. Before beginning any testing, always zero your CO instrument in fresh outdoor air to establish an accurate baseline.

### 1. Initial Ambient Air Assessment

Walk into the home with your CO meter on and actively sampling. Any measurement above zero warrants investigation, as CO is only present as a byproduct of combustion. In homes where occupants smoke or burn scented candles, readings between 2-6 ppm are common but anything above 6 ppm should be thoroughly investigated.

### 2. Mechanical Room Evaluation

- Check ambient CO levels in the mechanical room before operating equipment
- Look for signs of backdrafting or improper venting
- Compare mechanical room readings with general living space readings

### 3. Appliance-Specific Testing

#### Water Heaters:

- Check combustion readings (O, CO, CO)
- Verify stack temperature
- Measure draft pressure

#### Standard Efficiency Furnaces (80%):

- Test gas pressure
- Check limit and pressure switches
- Verify proper combustion parameters
- Monitor static duct pressure
- Check mechanical room CO levels
- Test appliance vestibule and burner area (readings should match ambient air)
- Test supply air stream in the plenum (any increase indicates potential heat exchanger issues)

#### High-Efficiency Units (90%+):

- All the above, plus
- Verify condensate drainage
- Check inducer operation
- Inspect venting system for proper installation and operation

### 4. Documentation Requirements

Record all readings during your testing procedure, noting:  
\* Ambient CO levels before equipment operation  
\* Mechanical room CO levels during equipment operation  
\* Flue gas readings for each appliance  
\* Supply air CO readings  
\* Any corrections or adjustments made

Here’s your quick reference guide for flue gas measurements:

- **Under 50 ppm:** Normal for most modern gas appliances
- **Up to 175 ppm:** Acceptable for some high-efficiency boilers
- **200 ppm:** Your absolute maximum before requiring adjustment
- **400+ ppm:** Red tag territory – shut it down immediately

For different heating systems, here are the typical acceptable combustion results (always follow manufacturer’s specifications):

### Gas Fired Power Burners:

- **Oxygen (O):** 3-6%
- **Carbon Monoxide (CO):**  [View this post on Instagram](https://www.instagram.com/reel/C5rSJvWrefA/?utm_source=ig_embed&utm_campaign=loading)
>
> [A post shared by Gary McCreadie HVAC/R Tech/Business Owner (@hvacknowitall1)](https://www.instagram.com/reel/C5rSJvWrefA/?utm_source=ig_embed&utm_campaign=loading)

**The majority of walk-in coolers will utilize a TXV to maintain proper superheat in the system**. Here’s what you need to know:

- Superheat is measured by taking suction vapor pressure converted to temperature minus saturation temperature
- You ideally want to measure superheat at the outlet of the evaporator
- For a walk-in cooler, superheat at the evaporator should be 6 to 10 degrees
- Don’t adjust superheat until the box is close to normal operating temperatures

Adjusting the TXV is a slow process. A small adjustment can make a huge change. It is best to make a small adjustment and give it time to settle out before making another change.

Also, once the cooler superheat is properly set, I like to check it at the suction inlet at the condensing unit. This also is vital to ensure you are not allowing liquid to return to the compressor and possibly cause damage.

Walk-in coolers may utilize different control methods:

**Pump-Down Systems:**  
\* Use a liquid line solenoid valve controlled by the thermostat  
\* When satisfied, the solenoid closes, and the compressor pumps refrigerant out of the evaporator until the low-pressure switch opens  
\* Provides additional compressor protection  
\* More common in larger or critical refrigeration applications

**Direct Control Systems:**  
\* Thermostat directly controls the condensing unit contactor  
\* Simpler design with fewer components  
\* Typically found in smaller walk-in coolers  
\* May require additional protection devices for the compressor

Each system requires different troubleshooting approaches, particularly when diagnosing electrical control issues.

## Closing Thoughts

In conclusion, troubleshooting a walk-in cooler requires a systematic approach and attention to detail. Understanding the fundamentals of refrigeration and airflow is key to diagnosing and resolving issues effectively. Always start with the basicsensuring proper airflow, checking for blockages, and confirming system components are operational. From there, methodically work through the control systems, evaporator, and condensing unit.

Remember that walk-in coolers are designed with specific operational parameters in mind. They maintain cold products rather than rapidly chill hot items, and their refrigeration systems are calibrated accordingly. Tools like pressure-temperature charts, superheat, and subcooling measurements are your best allies in ensuring the cooler operates efficiently and safely.

By applying the systematic diagnosis techniques outlined in this guide, you’ll minimize customer downtime, reduce unnecessary parts replacements, and establish yourself as a trusted refrigeration professional. Stay curious, stay safe, and keep learningthere’s always more to master in the world of refrigeration!

},
"image": "https://hvacknowitall.com/wp-content/uploads/2024/12/image-2.png",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/walk-in-cooler-troubleshooting-back-to-basics"
},
"datePublished": "2024-12-15",
"dateModified": "2024-12-15",
"articleSection": "HVAC Troubleshooting",
"keywords": "walk-in cooler troubleshooting, refrigeration diagnosis, HVAC, superheat adjustment, TXV, systematic diagnosis"

],
"tool": [
]

],
"keywords": "HVAC, compressor failure, refrigeration systems, HVAC maintenance, compressor troubleshooting, shorted windings, seized compressor",
"mainEntity": {
"@type": "HowTo",
"name": "How to Prevent Premature Compressor Failure",
"step": [
]

--------------------------------------------------

# ID: 5337

## Title: Non-Invasive System Testing: The Future of HVAC/R Troubleshooting

## Type: blog_post

## Author: Unknown

## Publish Date: 2024-11-08T15:39:20

## Word Count: 2438

## Categories: None

## Tags: None

## Permalink: https://hvacknowitall.com/blog/a-technicians-guide-to-non-invasive-system-testing

## Description:
## The Future of HVAC/R Troubleshooting: Non-Invasive System Testing

Imagine the traditional image of an HVAC technician: coverall-clad, hunched over a set of refrigerant gauges beside a condenser, interpreting readings to determine system health. What if this familiar scene became increasingly rare, with gauges only appearing twice in a system’s entire lifecycle? Welcome to the world of **non-invasive system testing (NIST)** the future of HVAC/R diagnostics.

NIST represents a paradigm shift in how we approach system troubleshooting and maintenance. By leveraging temperature measurements, airflow diagnostics, and a deep understanding of refrigerant cycle relationships, technicians can now accurately diagnose even complex system issues without breaking the sealed refrigerant circuit. This revolutionary approach not only preserves system integrity but also protects our environment and improves service efficiency.

Non-invasive system testing is what we call the act of testing and troubleshooting a system’s performance without ever connecting gauges. With the use of temperature clamps, thermistors, basic equations, and airflow diagnostic tools; paired with a deep understanding of the refrigerant cycle and pressure temperature relationships we are capable of diagnosing even intricate issues within a system using a less intrusive process than we’ve been known to use in the past.

There are several established methods for non-invasive testing, each with its own strengths:

### 1. The ANSI/ACCA 310 Method

[Standard 310](https://www.acca.org/qa/ansi-standard-310) is a new installation standard for unitary HVAC systems, mostly applicable for new installations. You can find their NIST protocol in [Section 8.4 of the official standard document](https://www.resnet.us/wp-content/uploads/ANSIRESNETACCA_310-2020_v7.1.pdf). This standardized approach uses normalized blower CFM and temperature measurements to verify proper system operation. It requires:

- Return air dry bulb and wet bulb temperatures
- Condenser entering temperature
- Suction line temperature
- Liquid line temperature

*Chris Morin explains ACCA’s approach to NIST*

### 2. The Mowris Non-Invasive Temperature Diagnostic (NTD) Method

Recently outlined in the [2024 ACEEE study on Lifecycle Refrigerant Management](https://www.aceee.org/sites/default/files/proceedings/ssb24/pdfs/Lifecycle%20Refrigerant%20Management.pdf), this method focuses on a non-invasive temperature diagnostic (NTD) testing technique which was patented by [Robert Mowris](https://www.verified.co/who-we-are#:~:text=of%20global%20warming.-,Robert%20Mowris,-earned%20a%20bachelor) in 2023. This approach factors in:

- Design Temperature Differences (DTD)
- Temperature relationships between components
- Power consumption verification
- Comprehensive system benchmarking

### 3. The measureQuick “Benchmarking” Approach

[This method](https://youtu.be/wFJSx2ZkaNk) combines the best of both worlds. [Pioneered by Jim Bergmann, measureQuick’s “benchmarking”](https://www.youtube.com/watch?v=Al2_IWJHA3c) feature allows you to save a “known good” snapshot of the system performance in the cloud, which then saves time and resources in every future site visit. Here’s some of the highlights of measureQuick’s Benchmarking process:

- System-specific snapshots get saved to the cloud
- Real-time performance analysis
- Automated calculations based on system profile
- Historical tracking of system performance

I was fortunate enough to interview about NIST on the measureQuick YouTube Channel:

*Watch the extended interview on measureQuick’s approach to NIST*

| Method | Key Features | Best For | Required Tools |
| --- | --- | --- | --- |
| **ANSI/ACCA 310** | Standardized approach using normalized blower CFM and temperature measurements | New installations, standard verification | Temperature probes, CFM measurement tool, psychrometer |
| **Mowris NTD** | Focuses on Design Temperature Differences and power consumption | Comprehensive performance benchmarking | Temperature probes, power analyzer, airflow measurement |
| **measureQuick Benchmarking** | System-specific snapshots saved to cloud, historical tracking | Ongoing maintenance, performance trending | Temperature probes, smartphone app, airflow measurement |

### 1. Refrigerant Loss

One of the primary advantages of non-invasive testing is the ability to identify problems without the risk of losing refrigerant. In an average service call, a **residential system typically loses 5% of its charge just from connecting gauges**! *(Note: this percentage will be less for larger systems)*

This may not seem like a lot but when we factor in how many visits a system will need in its lifetime, and a technician gauging up each time that number certainly adds up. Loss of refrigerant affects the performance, health and efficiency of a system leading to more frequent service calls, and customer discomfort. Thus, we must do what we can to keep as much of our charge within the closed system as possible.

### 2. Environmental Protection

How we service HVAC systems has a major impact on the environment, and **“gauging up” accounts for 50% of all refrigerant venting**. This excerpt from the “Refrigeration Lifecycle Management” Study linked above was an eye-opening read:

> *From the There are about 2 billion AC and HP systems in the world or approximately 1 system for every 4 people. Total refrigerant in cooling equipment worldwide (“installed refrigerant bank”) is 24 billion MTCO2e equivalent to annual emissions of 5 billion gas-powered cars (CCL 2022). Refrigerant venting damages the ozone layer and produces approximately one ton of equivalent carbon dioxide (CO2) emissions per pound of hydrochlorofluorocarbon (HCFC) refrigerant R-22 and hydrofluorocarbon (HFC) R-410a. Reducing refrigerant venting will help reduce global warming from 0.5C to 0.04C by year 2100 (DNV GL. 2021)*

### 3. Minimal Disruption

Traditional HVAC diagnostics often require significant downtime, leading to discomfort for occupants in residential or commercial settings. Non-invasive checks can be performed with minimal disruption, allowing systems to remain operational while evaluations are conducted.

### 4. Enhanced Safety

There are a lot of safety risks that technicians face each day in our field. It’s important to take as many of those risks out of the equation as possible to improve the quality of work and life of technicians. Non-invasive methods protect technicians from potentially dangerous exposure to harmful chemicals and allow us to perform servicing of the system in a low-danger work zone.

Elevate your diagnostics game. Property.com’s exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool provides homeowner insights like permit history and home value, helping you diagnose issues faster and recommend upgrades confidently. Secure your limited spot in our network, boost your SEO with a custom subdomain, and access advanced financing options. Become a Property.com certified pro today early adopter rates available!

One key to successful non-invasive testing is understanding basic temperature relationships. For a typical system at 400 CFM per ton:

- The evaporator coil should be about 35F colder than the return air
- Modern condensers typically run about 20F above ambient temperature
- Target superheat or subcooling can be calculated based on these relationships

For example, if your return air is 75F: 75F – 35F = 40F evaporator coil temperature Add your target superheat (let’s say 13F) = 53F expected suction line temperature If you’re within 5F of this target, you’re likely in good shape.

To effectively implement non-invasive system checks, HVAC professionals should follow the following steps, in this approximate order:

### 1. Invest in Advanced Diagnostic Tools

- Quality temperature clamps and probes
- Airflow measurement devices
- Digital power meters for amp and watt readings
- Smart probe systems when possible

### 2. Proper Training

Regular training on non-invasive techniques ensures technicians can perform thorough evaluations without defaulting to connecting gauges. Understanding pressure-temperature relationships is crucial.

### 3. Establishing a NIST Routine

Making non-invasive checks part of every service call helps build confidence in the process. The more we perform these checks, the more we learn about system behavior without breaking the sealed system.

### 4. Benchmarking for Future Reference

As we’ve discussed in previous articles about proper system commissioning ([like Jamie Kitchen’s piece on adaptive vs. fixed expansion valves](https://hvacknowitall.com/blog/adaptive-vs-fixed-expansion-valves)), establishing baseline readings during installation is crucial. This data becomes invaluable for future non-invasive diagnostics.

While non-invasive testing should be your first approach, there are specific situations when connecting gauges becomes necessary:

1. **Initial System Commissioning**
2. For establishing baseline performance metrics
3. When performing manufacturer-required startup procedures
4. To verify proper initial charge levels within 2% of specification
5. **Major Repairs Requiring Refrigerant Recovery**
6. Component replacements (compressor, evaporator, condenser)
7. Repairing refrigerant leaks
8. Converting to alternative refrigerants
9. **When Non-Invasive Tests Indicate Significant Issues**
10. Suction line temperature more than 8F from calculated target
11. Liquid line temperature deviation exceeding 5F from expected
12. System running but with minimal or no cooling effect
13. Abnormal power consumption (20% from manufacturer specifications)
14. Unusual operating sounds suggesting pressure problems
15. **System Disposal and Decommissioning**
16. For proper refrigerant recovery and recycling
17. To meet EPA regulations for system retirement
18. **Manufacturer Warranty Requirements**
19. When documentation of specific pressure readings is required
20. For warranty claim validation

Remember: Even when gauges are necessary, minimize connection time and always use low-loss fittings to reduce refrigerant emissions.

Let me walk you through a real-world example of non-invasive testing on a 3-ton residential split system with a TXV. I’ll show you exactly what I look for and how I interpret the readings.

### Before We Start: The Setup

- Outdoor temperature: 85F (measured in the shade near condenser)
- System: 3-ton residential split system, R410A, TXV
- Tools needed: Temperature clamps, psychrometer (for wet/dry bulb), airflow measurement tool

### Step 1: Verify Airflow

First Always start with airflow – it’s the foundation of everything else. I use my TrueFlow grid to measure actual CFM:

- Target: 1200 CFM (400 CFM/ton 3 tons)
- Actual measured: 1150 CFM
- This is within 5% of target, so we’re good to proceed

### Step 2: Check Your Design Temperature Differences

For a 13-14 SEER system, we expect:

- Evaporator DTD: 35F
- Condenser CTOA (Condensing Temperature Over Ambient): 20F (If you’re working on a higher SEER system, that CTOA might be closer to 15F)

### Step 3: Take Your Measurements

Here’s what I measured:

- Return air (dry bulb): 75F
- Return air (wet bulb): 63F
- Supply air: 55F
- Liquid line temperature: 95F
- Suction line temperature: 53F
- Condenser discharge air: 95F

### Step 4: Do The Math

Let’s analyze what these numbers tell us:

#### For the evaporator:

1. Calculate expected coil temperature
   - Return air (75F) – DTD (35F) = 40F expected coil temp
2. Add target superheat for TXV (10F +/- 5F)
   - 40F + 10F = 50F expected suction line temp
3. Compare to actual suction line (53F)
   - We’re within 3F of target – looking good!

#### For the condenser:

1. Calculate expected condensing temperature
   - Outdoor temp (85F) + CTOA (20F) = 105F
2. Subtract target subcooling (10F)
   - 105F – 10F = 95F expected liquid line temp
3. Compare to actual liquid line (95F)
   - We’re right on target!

### Step 5: Temperature Split Check

- Actual split: Return (75F) – Supply (55F) = 20F
- At 63F wet bulb return air, this split indicates proper operation *(Remember: target split varies with return air wet bulb – it’s not always 20F!)*

### Step 6: Additional Verification

I always take one more measurement – power consumption. For this 3-ton unit:

- Nameplate RLA (Rated Load Amps): 14.2
- Actual measured: 13.8 amps Running slightly under RLA on an 85F day is exactly what we want to see.

### What This Tells Us

All our measurements indicate this system is:

- Properly charged (liquid line temp matches target)
- Has correct superheat (suction line within range)
- Moving the right amount of air (proper temperature split)
- Operating efficiently (amp draw appropriate for conditions)

### Red Flags to Watch

For If you see any of these, you might need to break out the gauges:

- Suction line temp more than 5F from target
- Liquid line temp more than 3F from target
- Temperature split way off from expected
- Amp draw significantly higher or lower than expected
- Supply air temperature higher than 60F when return is 75F

Remember: This is just one example with one set of conditions. The exact numbers will vary based on equipment efficiency, outdoor conditions, and indoor load. The key is understanding the relationships between these temperatures and what they tell us about system operation.

## Conclusion

Non-invasive system testing represents a significant advancement in HVAC service methodology. By facilitating accurate diagnostics without compromising system integrity, NIST delivers substantial benefits to property owners, technicians, and our environment. As technology continues to evolve and environmental regulations become more stringent, the importance of non-invasive diagnostics will only increase, cementing its place as an industry best practice.

By adopting these methods, you’ll not only improve system performance and reduce callbacks but also develop more advanced technical skills and environmental responsibility. Remember that just as we wouldn’t connect gauges to check a home refrigerator, we should strive to treat all HVAC systems with the same respect for their sealed integrity. The future of our industry depends on adapting our practices to protect both our customers’ systems and our environment.

-Jennifer Manzo

This article was a collaboration between [Jennifer Manzo](https://www.linkedin.com/in/hvachicks-jennifer-206832280/) of [HVAChicks Coalition](https://www.facebook.com/groups/812323020341191/?_rdr) & [Ben Reed](https://www.linkedin.com/in/ben-reed-/) of [Teal Maker](https://tealmaker.com/).

],
"publisher": {
"@type": "Organization",
"name": "HVAC Know It All"
},
"about": {
"@type": "Thing",
"name": "HVAC Troubleshooting"
},
"keywords": "HVAC, non-invasive system testing, NIST, refrigerant, troubleshooting, temperature measurement, environmental protection",
"hasPart": {
"@type": "HowTo",
"name": "Non-Invasive System Check",
"description": "Step-by-step guide for performing a non-invasive system check on an HVAC system",
"step": [
],
"tool": [
]

--------------------------------------------------

# ID: 5319

## Title: Utility Overvoltage: How It Damaged a Rheem Proterra Heat Pump Water Heater

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2024-10-30T10:29:46

## Word Count: 1045

## Categories: Heat Pumps, Heating Systems, HVAC Installation, HVAC Maintenance, Safety

## Tags: None

## Permalink: https://hvacknowitall.com/blog/utility-over-voltage-is-a-killer

## Description:
![The Rheem Professional Prestige Proterra Hybrid heat pump water heater.](https://hvacknowitall.com/wp-content/uploads/2024/10/Professional-Prestige-ProTerra-Hybrid-396x1024.png)

One of my customers had a problem with his [Rheem Proterra heat pump water heater](https://www.rheem.ca/product/ProTerra-Hybrid-Electric-Water-Heater/) – it was tripping the breaker on a daily basis. What initially seemed like a potential equipment failure turned out to be an important lesson in thorough electrical diagnostics and utility supply issues.

The Proterra is a hybrid water heater system that utilizes a combination of heat pump technology and electric resistive heating elements to ensure domestic hot water stays at the set point temperature. The system can operate in various modes: Heat Pump Only (most efficient), Hybrid (balances efficiency and recovery), Electric (uses only the resistive elements), or Vacation (maintains minimal temperature during extended absences).

The heat pump extracts heat from surrounding air, making it up to 4 times more efficient than standard electric water heaters, while the resistive elements provide backup heating when demand increases or ambient temperatures drop. But we’re not here to discuss its operation in detail – we’re here to find out why this particular unit was tripping its breaker.

After a quick visual inspection, everything looked okay, except for signs of overheating on the upper resistive element – a clue that something wasn’t right.

Upon testing the electrical supply, I discovered the incoming voltage was 255.4 volts, despite the tank being rated for 240V. Even more concerning, after an hour or two, the voltage had increased further.

For context, standard North American residential voltage should typically be 240V nominal, with acceptable tolerances of +/- 5% (228-252V) according to ANSI C84.1 standards. Voltages consistently above this range can cause significant damage to appliances.

I informed the customer about the overvoltage condition, and he promptly contacted the utility company. They showed up within an hour and corrected the situation. After the voltage reduction to appropriate levels, the breaker did not trip again.

[Check out this Instagram post and conversation on this topic.](https://www.instagram.com/p/C684L_3OAXW/?igsh=c2I3bWlubGpkZHM4)

[![Follow Gary on Instagram for daily tips & memes.](https://hvacknowitall.com/wp-content/uploads/2024/10/Check-Out-Garys-Post-On-Instagram-1024x1024.png)](https://www.instagram.com/p/C684L_3OAXW/?igsh=c2I3bWlubGpkZHM4)

The utility company’s swift response demonstrates how seriously they take these voltage issues, as excessive voltage can cause widespread problems beyond just one appliance:

- Premature failure of electronic components
- Overheating of resistive elements
- Nuisance breaker tripping
- Reduced lifespan of appliances and equipment
- Potential fire hazards in severe cases

This case serves as an excellent reminder of why taking multiple voltage readings over time, rather than a single snapshot measurement, can reveal developing problems that might otherwise go unnoticed.

Voltage fluctuations often occur throughout the day as grid demand changes, so what appears normal during one visit might be problematic hours later.

For more details about this diagnostic challenge, listen to the following short podcast where this call is described in detail:

[Listen on Spotify](https://open.spotify.com/episode/02bGsr30n83exGH9DTFitn?si=SlFPMU94SsO12zDueT8FqA&context=spotify%3Ashow%3A6LCBJGw0EHG03rdWHxUMce)

![253V may damage appliances. Contact your utility immediately.](https://hvacknowitall.com/wp-content/uploads/2024/10/Im-Not-In-Danger-I-Am-the-Danger-25102024120311.jpg)

Voltage in the 253V range can cause a slow death for sensitive electronics. When faced with an equipment failure, resist the urge to immediately blame the unit itself. Be thorough and check your incoming voltage first.

This is where permanent voltage monitoring can be particularly valuable:

- Continuous monitoring devices can track voltage fluctuations over time
- Systems can be set up to shut down equipment automatically if voltage becomes too high or too low (brown out)
- These monitors can be paired with surge protection devices for comprehensive electrical protection
- Some advanced models offer remote monitoring capabilities via smartphone apps

Products like the Intermatic IG1240RC3, Functional Devices RIBXGFA, or Emerson 460 series provide various monitoring options depending on your specific needs and budget.

Avoid surprises on the job site. Property.com’s exclusive ‘Know Before You Go’ tool gives certified HVAC Pros critical homeowner insights like permit history and property details *before* you arrive. Stand out with Property.com certification and access tools designed for elite contractors. Limited spots available per region secure yours today at [Property.com](https://mccreadie.property.com).

I recorded a podcast with this particular customer about why he chose to go the electrification route for his heating, cooling, and water heater. If you’re interested in learning more about real-world experiences with home electrification:

[Listen on Spotify](https://open.spotify.com/episode/3zjhnM9AYBe3CcEbshOSqK?si=_bOoi056Rpeqhh6wsHJrxQ)

## For more exclusive, educational HVAC/R content, subscribe to our newsletter.

Top Tech Tips, Twice A Month.

(function() {
window.mc4wp = window.mc4wp || {
listeners: [],
forms: {
on: function(evt, cb) {
window.mc4wp.listeners.push(
);

},
"mainEntity": {
"@type": "HowTo",
"name": "Diagnosing Circuit Breaker Tripping in Heat Pump Water Heaters",
"step": [
]
},
"about": [
],
"knowsAbout": [
"HVAC",
"Water Heaters",
"Electrical Troubleshooting",
"Voltage Monitoring"
]
);

},
"datePublished": "2024-10-16",
"image": "https://hvacknowitall.com/wp-content/uploads/2024/10/image-edited.png",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/an-hvac-technicians-guide-to-wireless-communications"
},
"articleSection": "Technical Guides",
"keywords": "HVAC, wireless communications, RF, antennas, Wi-Fi, Bluetooth, troubleshooting",
"definedTermSet": [
]

},
"image": "https://hvacknowitall.com/wp-content/uploads/2024/08/1\_analog\_refrigeration\_gauges-1024x424.png",
"datePublished": "2024-08-01",
"proficiencyLevel": "Expert",
"articleSection": "Refrigeration",
"keywords": [
"pressure testing",
"refrigeration systems",
"nitrogen",
"TSSA inspection",
"HVAC procedures",
"PSIG",
"small refrigeration systems",
"large refrigeration systems"
]

},
"about": {
"@type": "Thing",
"name": "HVAC diagnostics and measurements"
},
"educationalUse": "Technical Reference",
"audience": {
"@type": "Audience",
"audienceType": "HVAC Professionals"

--------------------------------------------------

# ID: 4827

## Title: Understanding Refrigerant Gas Volume: Key Concepts for HVAC Professionals

## Type: blog_post

## Author: Julian Finbow

## Publish Date: 2024-05-27T19:07:36

## Word Count: 1693

## Categories: None

## Tags: None

## Permalink: https://hvacknowitall.com/blog/what-size-is-your-gas

## Description:
## Understanding Refrigerant Gas Volume in HVAC Systems

When troubleshooting or optimizing mechanical cooling systems, a critical but often overlooked factor is refrigerant gas volume. This property significantly impacts system performance, efficiency, and compressor operation.

Gas volume refers to the amount of space that refrigerant occupies per pound of weight (expressed in ft/lb). In professional terms, this is known as **Specific Volume (SV)**. The “lighter and fluffier” the gas is, the more of it your compressor must pump to achieve **1 Ton of Cooling (12,000 BTU/hour)**, directly affecting system efficiency and capacity.

This concept becomes particularly important when analyzing refrigerant conditions in the suction line. Different applications require different gas volumes, and understanding these relationships is essential for proper system design, troubleshooting, and optimization.

An often overlooked consideration in a mechanical cooling system is gas volume. Gas volume can describe the cubic footage of space that a gas is taking up per pound of the gas by weight (expressed in ft/lb).

Consideration of refrigerant gas volume is most important when looking at refrigerant conditions in the suction line. The ‘lighter and fluffier’ (coined by the author) that the gas is, the more of it your compressor must pump to accomplish **1 Ton of Cooling (12,000 BTU/hour)**.

More specifically, volume is referred to as **Specific Volume (SV)**. For example, a Reciprocating Booster Compressor (1st of 2 compression stages) must have physically large cylinders to pump enough of the low temperature/high specific volume gas required to achieve its capacity.

Note that Booster Compressors pull a low **Saturated Suction Temperature (SST)** gas, perhaps -20F SST, which has a high **Specific Volume**. A gas with high Specific Volume is represented on the left side of the image below.

![Comparison between light (high specific volume) and dense (low specific volume) refrigerant gas](https://hvacknowitall.com/wp-content/uploads/2024/05/IMG-1-Light-vs-Dense-Gas-v2-1024x663.jpg "Light vs Dense Refrigerant Gas Comparison")

The opposite of specific volume is Density. **Density (D)** can be described as the weight of refrigerant in pounds per cubic foot of space the gas is taking up (expressed in lb/ft). Air conditioning compressors pull suction from a high-temperature gas around 40F SST, which is a very dense gas.

Using a Reciprocating Compressor again, its cylinders will be much smaller. This is for two reasons:

1. It needs to move less total refrigerant (since it is dense) to accomplish e.g. 1 Ton of Cooling
2. If the cylinders were large, the Compressor would easily pull a high motor current as this dense (heavy and sluggish) gas takes more work to compress

The right side of the image above represents a gas with high density. Different Compressors exist for different desired suction temperatures. When they’re represented mathematically, density and specific volume are reciprocal (image below).

![Mathematical relationship between Specific Volume and Density](https://hvacknowitall.com/wp-content/uploads/2024/05/IMG-2-V-and-D-v2-1024x387.jpg "Specific Volume and Density are reciprocal properties")

For any Compressor’s operation, the importance of gas volume can be clearly shown on a Pressure Enthalpy Diagram. The remainder of this article will take for granted that the reader understands Pressure Enthalpy Diagrams and how refrigeration systems are plotted on them.

To learn these details or brush up on them, please visit [Sporlan Pressure Enthalpy Diagram](https://www.parker.com/content/dam/Parker-com/Literature/Sporlan/Sporlan-pdf-files/Sporlan-pdf-Miscellanous/5-200.pdf). This PDF is a great resource, which I reference regularly during classes on **Pressure Enthalpy (PE)**.

### Danfoss Cool Selector 2

The PE Diagrams shown in the remaining images are from the [Danfoss Cool Selector 2](https://www.danfoss.com/en/service-and-support/downloads/dcs/coolselector-2/) application. This free tool can be downloaded or viewed online.

[Here is a video](https://www.youtube.com/watch?v=IFBlnoDeeeg) that shows (at 1:32) how to access PE Diagrams from Cool Selector. Within the application, they are referred to as “p-h” diagrams, with “h” representing enthalpy. You can also plot Compressors/systems within the app (shown later in the video), select equipment, perform heat load calculations, and more.

![Danfoss Cool Selector 2 interface](https://hvacknowitall.com/wp-content/uploads/2024/05/IMG-3-DCS2-1024x618.jpg "Danfoss Cool Selector 2 software interface")

Picture your customer making a request to change the operating conditions of their cooler. They instead would like to run their cooler as a freezer. Something like this can be done by reducing the **Saturated Suction Temperature (SST)** of the Compressor which pulls suction on the refrigerated space’s evaporator.

If the **Low Pressure Cut-Out (LPCO)** is the Compressor operating control, this switch could be operated to have the Compressor turn off at a lower pressure corresponding to the new desired SST. To see the ill effects this could cause, we can use the Pressure Enthalpy Diagram. In the image below, an SST of 40F and an SST of 0F are both referenced on the 100% Saturated Vapour Line.

Their Specific Volume values (expressed in ft/lb) are illustrated by the lines extending to the right side of the graph. It can be gleaned from this that a reduction in SST causes an increase in the Specific Volume of the refrigerant.

The characteristics of Saturated Vapour can be remembered by comparing them to freezing water: as the water freezes, it continues to expand. Mechanics and operators need to consider this increased gas specific volume when lowering the Compressor SST.

### Negative Effects of Reducing SST Due to Increased Specific Volume

- **Increased Specific Volume:** Must pump more refrigerant per ton of cooling
- **Increased gas entropy:** Less efficient compression
- **Reduced hermetic motor cooling:** Though the gas is ‘colder’, its large volume results in less winding cooling
- **Reduced volumetric efficiency**
- **Reduced Compressor capacity**
- **Reduced Coefficient of Performance (COP)**

If Saturated Condensing Temperature (SCT) is held constant:  
\* **Increased compression ratio**  
\* **Higher discharge gas temperatures**  
\* **Higher oil temperatures**

![Effect of SST reduction on refrigerant Specific Volume](https://hvacknowitall.com/wp-content/uploads/2024/05/IMG-4-SST-effect-on-Volume-1024x791.jpg "Lower SST results in higher Specific Volume")

A **Thermostatic Expansion Valve (TXV)** is a common, adjustable Metering Device that functions on the premise of an evaporator outlet superheat. In a basic system, a single Compressor pulls a short suction line from the evaporator.

If the TXV is adjusted incorrectly, it will constantly allow a higher-than-necessary superheat value to the Compressor during operation. Superheat is required to be added to the refrigerant to ensure the Compressor (a vapor pump) does not see refrigerant in its liquid state.

Any more Superheat returning to the Compressor than required is a system inefficiency. In the below Pressure Enthalpy Diagram, there are two plot points considered at an SST of -20F for example. The first plot point represents a suction gas which has gained 60F of Superheat.

The second plot point shows an extreme amount of Superheat added, totaling 180F of Superheat. What can be noticed is an increase in Superheat returning to the Compressor will also cause an increase in the Specific Volume of the return gas.

Characteristics of a Superheated Vapour can be remembered by comparing it to air: ‘hot’ air rises, as its volume increases. *Note that a Saturated and a Superheated Vapour’s Specific Volume react in opposite ways to temperature change.*

### How Excess Superheat Reduces System Efficiency

- Higher return gas temperatures
- Higher discharge gas temperatures
- Higher oil temperatures
- Factors due to Specific Volume increase caused by increased Superheat:
- Less hermetic motor cooling
- Higher entropy of gas
- Reduced compressor capacity
- Reduced volumetric efficiency
- Reduced COP

![Effect of increasing superheat on refrigerant Specific Volume](https://hvacknowitall.com/wp-content/uploads/2024/05/IMG-5-Superheat-effect-on-Volume-1024x791.jpg "Higher superheat results in higher Specific Volume")

Understanding refrigerant specifics like gas volume is crucial for peak performance. Elevate your diagnostic edge with Property.com’s exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool, offering deep homeowner and property insights. Join our invitation-only network of certified HVAC pros, boost your SEO with a premium subdomain, and access tools designed for top-tier contractors. Limited spots available per region. Request your invite today.

To help with the technical terms used throughout this article, here’s a quick reference guide:

- **SST (Saturated Suction Temperature)**: The temperature at which refrigerant changes from liquid to vapor at the specific pressure found in the suction line
- **SV (Specific Volume)**: The volume occupied per unit mass of refrigerant (ft/lb)
- **D (Density)**: Mass per unit volume of refrigerant (lb/ft)
- **PE (Pressure Enthalpy)**: A diagram showing refrigerant properties and system processes
- **LPCO (Low Pressure Cut-Out)**: A safety switch that stops compressor operation when suction pressure drops below a predetermined setpoint
- **TXV (Thermostatic Expansion Valve)**: A precision metering device that regulates refrigerant flow based on evaporator outlet superheat
- **COP (Coefficient of Performance)**: A measure of system efficiency (cooling output divided by energy input)
- **Superheat**: The temperature increase of refrigerant vapor above its saturation temperature

## Closing Thoughts: Practical Applications

Two different factors can put stress on a compressor by increasing the return gas specific volume: reducing SST and increasing Superheat. Both of these changes can lead to reduced system efficiency, higher operating temperatures, and potentially shortened equipment life.

A Pressure Enthalpy Diagram provides an excellent way to visualize these concepts while applying specific metrics to real-world scenarios. By maintaining appropriate superheat levels and operating within designed SST ranges, HVAC professionals can ensure optimal system performance, efficiency, and longevity.

Remember: When it comes to refrigerant gas, save “light and fluffy” for your desserts, not your HVAC systems. Dense, properly managed refrigerant flow is the key to reliable, efficient operation.

},
"datePublished": "2024-05-01",
"image": "https://hvacknowitall.com/wp-content/uploads/2024/05/IMG-1-Light-vs-Dense-Gas-v2-1024x663.jpg",
"about": [
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/central-heat-pump-install-considerations"
},
"datePublished": "2023-11-01",
"dateModified": "2023-11-01",
"proficiencyLevel": "Expert",
"about": [
],
"hasPart": {
"@type": "HowTo",
"name": "Central Heat Pump Installation Process",
"step": [
]

--------------------------------------------------

# ID: 4618

## Title: HVAC-D Systems for Cannabis Grow Facilities: Complete Environmental Control Guide

## Type: blog_post

## Author: Greg Crumpton

## Publish Date: 2023-06-30T02:44:05

## Word Count: 1983

## Categories: None

## Tags: None

## Permalink: https://hvacknowitall.com/blog/hvac-for-indoor-cannabis-growing-facilities

## Description:
## HVAC for Indoor Cannabis Growing Facilities

In the specialized world of indoor cannabis cultivation, standard HVAC (Heating, Ventilation & Air Conditioning) systems require an additional crucial component: Dehumidification. This expanded system, known as HVAC-D, addresses the unique environmental control challenges that cannabis plants present throughout their growth cycle.

Why is dehumidification so critical? The cannabis plant’s growth process revolves around its ability to absorb and release water vapor. During transpirationthe process where plants emit water vapor through their surfacescannabis plants release significant moisture into their growing environment. Without proper dehumidification, this creates excessive humidity that can lead to mold, mildew, and compromised crop quality.

Unlike traditional climate control applications, cannabis cultivation facilities face the challenge of removing vast amounts of latent heat (in the form of water vapor) at precise times during the plant’s development. This requires specialized environmental management beyond what standard HVAC systems typically provide.

![Cannabis-Growth-Cycle](https://hvacknowitall.com/wp-content/uploads/2023/06/Cannabis-Growth-Cycle-1024x1024.webp)**Cannabis Growth Cycle**

For HVAC professionals new to cannabis facility projects, understanding the plant’s basic growth cycle is essential for designing effective environmental control systems. Cannabis progresses through several distinct phases: seed germination, seedling, vegetative growth, and flowering. Each stage requires specific environmental conditions for optimal development.

The plant’s needs include proper soil, water, light (natural or artificial), and nutrition. However, as HVAC professionals, our primary responsibility lies in creating and maintaining the ideal ambient conditionsparticularly temperature and humidity controlthroughout these growth phases.

### The Critical Role of Transpiration

**Transpiration** is the process through which plants emit water vapor through their surfaces, particularly their leaves. This biological function is essential for nutrient transport and cooling. In cannabis cultivation, managing this process through proper ventilation and dehumidification is crucial for plant health and production quality.

The HVAC system must efficiently remove the water that plants release after absorption through their root systems while maintaining precise temperature control. This balance creates the optimal growing environment that maximizes both yield and quality.

![Marijuana growing under artificial light](https://hvacknowitall.com/wp-content/uploads/2023/06/Marijuana-growing-under-artificial-light-1024x683.webp)

Understanding each phase of cannabis growth helps HVAC professionals design systems that can adapt to changing environmental requirements throughout the cultivation process.

### Seeds and Seedling Phase

The cultivation process begins with seeds planted in starter mix, covered with plastic, and placed on a heat mat. Once sprouted, seedlings develop their first leaves and require careful environmental management:

- Plants focus energy on developing roots and foliage
- Roots are small and delicate, requiring careful water management
- Growth environments need 18 hours of light daily
- Consistent, moderate humidity levels are essential

### Vegetative Phase

As plants transition to the vegetative stage, they experience rapid growth and increased metabolic activity:

- Root systems and foliage expand significantly
- Plants may grow 2+ inches daily in optimized environments
- Higher humidity levels (60-70%) support this rapid growth
- Plants require more water, nutrients, and CO
- Different strains (Indica and Sativa) become distinguishable

During this stage, growers typically identify plant sex, removing males to prevent pollination of female plants, which would reduce flower quality.

### Flowering Phase

The flowering stage represents the final growth phase before harvest:

- Triggered by reducing light exposure to 12 hours on/12 hours off
- Lasts 6-10 weeks depending on cannabis strain
- Plants develop resin-covered buds containing THC and terpenes
- Lower humidity requirements (40-60%) prevent mold issues
- Different nutritional needs compared to vegetative stage

After flowering comes harvesting, curing, trimming, and packagingeach with their own specific environmental requirements that HVAC systems must accommodate.

Cannabis cultivation facilities contain multiple specialized rooms, each requiring specific temperature and humidity settings for optimal results. The HVAC-D system must be designed to maintain these distinct environments simultaneously.

### Mother Room

Mother rooms serve as genetic preservation areas, maintaining healthy plants from which cuttings are taken for propagation.

- **Temperature:** 75F
- **Relative Humidity:** 60%
- **HVAC Considerations:** Moderate dehumidification needs with consistent temperature control

### Propagation / Clone Room

These rooms house cuttings from mother plants that are developing their own root systems to become genetically identical plants.

- **Temperature:** 80F
- **Relative Humidity:** 90%
- **HVAC Considerations:** High humidity maintenance with minimal dehumidification; precise temperature control

### Veg (Vegetative) Room

Vegetative rooms house plants with established root systems that are growing to approximately 75% of their final size before flowering.

- **Temperature:** 80F
- **Relative Humidity:** 70%
- **HVAC Considerations:** Moderate dehumidification needs with significant cooling capacity

### Flowering Room

The flowering room is where mature plants produce the valuable flowers (buds) used in cannabis products.

- **Temperature:** 70-80F
- **Relative Humidity:** 40-60%
- **HVAC Considerations:** Substantial dehumidification requirements; temperature stability is critical

### Drying/Curing Room

Post-harvest, plants move to drying rooms where environmental control is crucial for preserving valuable compounds.

- **Temperature:** 65F
- **Relative Humidity:** 45%
- **HVAC Considerations:** Precise humidity control with minimal temperature fluctuation; filtration to prevent contamination

### Trim Room

The trim room is where excess plant material is removed from dried flowers.

- **Temperature:** 75F
- **Relative Humidity:** 50%
- **HVAC Considerations:** Moderate humidity control; air filtration for worker comfort

### Packaging Room

The final stage before distribution requires controlled conditions to maintain product quality.

- **Temperature:** 75F
- **Relative Humidity:** 50%
- **HVAC Considerations:** Consistent humidity control; positive pressure systems to prevent contamination

Handling complex environments like cannabis grow facilities demands expertise and the right support. Stand out in this specialized market with Property.com’s exclusive, invitation-only network. Gain instant credibility with our certification, access critical property insights before you quote using ‘[Know Before You Go](https://mccreadie.property.com)‘, and connect with valuable referral partners. Limited spots per trade/region ensure you maintain an edge. Learn how Property.com helps top HVAC pros dominate niche markets.

Selecting the right equipment for cannabis cultivation facilities requires balancing performance, efficiency, and reliability. Two primary approaches dominate the industry:

### Direct Expansion (DX) Systems

DX systems utilize the standard [vapor compression cycle](https://hvacknowitall.com/blog/the-refrigeration-cycle-explained) components (compressor, condenser, metering device, and evaporator) to provide cooling and dehumidification:

- **Advantages:** Lower initial cost, simpler installation, suitable for smaller facilities
- **Considerations:** Higher operating costs, limited zoning capabilities, may struggle with extreme humidity loads
- **Best applications:** Small to medium cultivation operations, facilities with limited budgets

### Chilled Water Systems

These systems use chilled water to cool and dehumidify the air, providing greater flexibility:

- **Advantages:** Superior zoning capabilities, more precise control, better handling of large spaces
- **Considerations:** Higher initial investment, more complex installation and maintenance
- **Best applications:** Large commercial operations, facilities with multiple grow rooms requiring different conditions

### Specialized Dehumidification Equipment

Beyond standard cooling systems, dedicated dehumidification equipment is often necessary:

- **Desiccant dehumidifiers:** Ideal for lower temperature environments like drying rooms
- **Refrigerant-based dehumidifiers:** Energy-efficient options for moderate humidity control
- **Integrated cooling/dehumidification units:** Purpose-built for cultivation facilities

The equipment selection should match the facility’s specific needs across all growth stages, with particular attention to peak loads during the flowering phase when plants release the most moisture.

Cannabis cultivation facilities are energy-intensive operations, with HVAC systems often accounting for 30-50% of total energy consumption. Implementing efficiency measures can significantly reduce operating costs:

### Heat Recovery Systems

Capturing and repurposing waste heat from cultivation equipment:  
– Redirect heat from lights and dehumidifiers to other areas requiring heating  
– Use recovered heat for water heating or supplemental space heating  
– Reduce overall energy consumption by 15-30% in appropriate climates

### Variable Frequency Drives (VFDs)

Installing VFDs on fans, pumps, and compressors:  
– Match equipment output to actual demand  
– Reduce energy consumption during lower-demand periods  
– Extend equipment life through reduced mechanical stress

### Advanced Controls and Monitoring

Implementing sophisticated control systems:  
– Automate environmental adjustments based on plant growth stage  
– Optimize equipment operation for maximum efficiency  
– Provide real-time monitoring and alerts for system performance

### Strategic Equipment Scheduling

Coordinating lighting and HVAC operation:  
– Schedule lighting during off-peak utility rate periods when possible  
– Stagger equipment startup to reduce peak electrical demand  
– Align dehumidification cycles with transpiration patterns

Properly designed efficiency measures not only reduce costs but can improve environmental control precision, benefiting both facility operators and crop quality.

Cannabis cultivation creates unique challenges for HVAC equipment, requiring specialized maintenance protocols to ensure reliable operation:

### Regular Filter Replacement

The cultivation environment produces significant airborne particles:  
– Replace filters more frequently than in standard applications  
– Consider MERV 13 or higher filtration for recirculated air  
– Inspect pre-filters weekly during heavy growth phases

### Coil Cleaning and Sanitization

Cannabis environments can accelerate coil fouling:  
– Schedule quarterly deep cleaning of all cooling and dehumidification coils  
– Use food-grade sanitizing agents compatible with cultivation  
– Monitor performance metrics to identify early signs of reduced efficiency

### Condensate Management

High dehumidification loads create substantial condensate:  
– Inspect condensate drains monthly for blockages  
– Consider chemical treatments to prevent algae growth  
– Install secondary overflow protection on all units

### Calibration and Verification

Precise environmental control requires accurate sensors:  
– Calibrate temperature and humidity sensors quarterly  
– Verify control system operation through independent measurements  
– Document set points and actual conditions for compliance requirements

### Regular System Assessments

As cultivation techniques evolve, system requirements change:  
– Conduct bi-annual comprehensive system evaluations  
– Analyze energy consumption patterns for optimization opportunities  
– Update control sequences to match current cultivation practices

Establishing these maintenance protocols helps prevent costly system failures while ensuring optimal growing conditions throughout the cultivation cycle.

## Final Thoughts

The cannabis cultivation industry presents both challenges and opportunities for HVAC professionals. Success in this specialized field requires understanding not just traditional HVAC principles, but also the unique environmental demands of the cannabis plant throughout its lifecycle.

Key takeaways for HVAC professionals entering this market include:

1. Dehumidification capacity is often more critical than cooling capacity in cannabis applications
2. Different growth stages require significantly different environmental conditions
3. System flexibility and redundancy should be prioritized to prevent crop loss
4. Energy efficiency measures can substantially reduce operating costs without compromising environmental control
5. Regular, specialized maintenance is essential for reliable system operation

As the cannabis industry continues to evolve, HVAC-D systems will play an increasingly important role in facility design and operation. By understanding the fundamental principles outlined in this guide, HVAC professionals can position themselves to succeed in this growing market segment.

*Special thanks to [InSpire Transpiration Solutions](https://inspire.ag/) for the keen insight and data points related to this article*

},
"image": "https://hvacknowitall.com/wp-content/uploads/2023/06/Cannabis-Growth-Cycle-1024x1024.webp",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/hvac-for-indoor-cannabis-growing-facilities"
},
"step": [
]
},
]
},
]
},
]
},
]
},
]
},
]

--------------------------------------------------

# ID: 4511

## Title: Understanding Dew Point: The Essential Diagnostic Tool for HVAC Technicians

## Type: blog_post

## Author: Unknown

## Publish Date: 2023-05-20T18:18:30

## Word Count: 2369

## Categories: Air Conditioning

## Tags: None

## Permalink: https://hvacknowitall.com/blog/understanding-dew-point

## Description:
## Becoming A Better Practitioner

The journey to becoming a great HVAC technician is a collection of small steps. To be a better diagnostician, you need to master foundational skills first. These include taking accurate temperature and [pressure readings](https://hvacknowitall.com/blog/pressure-testing-refrigeration-systems), calculating superheat and subcooling, and understanding [refrigeration principles](https://hvacknowitall.com/blog/the-refrigeration-cycle-explained).

While these skills form the foundation of a good technician, becoming an exceptional technician requires a deeper understanding of refrigeration cycles and psychrometric measurements. One of the most powerful yet underutilized diagnostics in your toolbox is dew point measurement.

Dew point is one of the most underrated readings a technician can take when diagnosing comfort problems. Most of us are familiar with the psychrometric chart, but many get intimidated by the complex array of lines going in every possible direction.

The dew point line simply moves from right to left on the chart. When it intersects with the dry bulb line, which runs up and down, this forms a “cross hair,” like a rifle scope. In the crosshair lies the current condition of the air you are measuring.

Simply, it is a measurement of the amount of water in the air. What it’s actually telling us, though, is *at what temperature the moisture will begin to fall out of the air* in the form of condensation.

Think of air as a sponge, which can hold a maximum amount of an exact amount of water. If you squeeze the sponge, it cannot hold as much, and the excess water will fall out. At a given temperature, air can hold an exact amount of water before it is completely saturated.

If we begin to cool the air, it is like squeezing the sponge. If we squeeze it hard enough, we make the sponge smaller and eventually, water falls out.

When we cool air, we make it “smaller,” and it eventually reaches saturation or its dew point, and condensation forms. Years ago, it was difficult to measure dew point as a technician.

The most common method was to use a sling psychrometer, in which you give your dry bulb and wet bulb, then you had to *plot* dew point on the psychrometric chart. It was nearly impossible to take these readings inside a duct.

But now, handheld electronic hygrometers (also called psychrometers) are available, affordable, and portable. They even work with Bluetooth and sync up to powerful apps like [Measurequick](https://www.measurequick.com/).

Taking an outdoor dew point measurement or knowing what the [ASHRAE](https://www.ashrae.org/) outdoor design dew point is will help you make good recommendations and design decisions.

![Testo Psychrometric chart](https://hvacknowitall.com/wp-content/uploads/2023/05/Testo-Psychrometric-chart.webp)Dry Bulb (red) and Dewpoint (blue) form a crosshair to indicate the current conditions of the air.

Let’s first understand what outdoor dew point tells us. The higher this number is, the more moisture is in the air. Humid climates like the Southern U.S. have extended periods of high dew point over 63F (17.C).

It’s not uncommon for coastal regions to experience periods of extremely high dew points of 80 (27C)!

Knowing what your outdoor dew point is can help you understand why condensation forms inside a duct, a wall, or another place where moisture droplets shouldn’t form. In fact, the ONLY place we want to see condensation form is on an evaporator coil. Anywhere else is undesirable.

Let’s say that your customer is noticing mildew in their home during humid weather. Biological growth forms as a result of condensation. You know that the outdoor dew point sometimes gets above 70F (21C), and humid air travels right through porous materials like wood and insulation.

If your customer likes to set the thermostat below 70, when the humid air hits a wall surface below its dew point temperature, condensation will form, leading to this growth. This can happen inside a wall where it can go unnoticed for a long time. Is the answer a dehumidifier?

A dehumidifier will help but only treats the symptoms, not the cause, by drying the *inside* of the building. The problem is high dew point air from *outside* is getting inside. The house needs to be air sealed. If it never had an effective water vapor barrier, such as house wrap, installed, this could be a major project.

As an HVAC technician, this is probably outside your scope of services. But understanding outdoor dew point will help you diagnose the problem correctly and point your customer in the right direction. It will also arm you with a scientific reason why your customer should not set their thermostat so low because it invites condensation to form.

![Condensation in walls](https://hvacknowitall.com/wp-content/uploads/2023/05/Condensation-in-walls.webp)Condensation in walls is caused by humid outside air leaking inside and can cause biological growth to form in the wall cavity.

Just like outdoor dew point that is above 63F (17C) is considered high, the same applies to indoor dew point. In fact, a few years ago, ASHRAE revised its [Standard 55](https://www.ashrae.org/technical-resources/bookstore/standard-55-thermal-environmental-conditions-for-human-occupancy) *Thermal Environmental Conditions for Human Comfort,* which now states that indoor dew point should not be higher than 62.2F (16.7C) to prevent mold. Prior to that, it only used relative humidity as a metric.

In Measurequick, you can change the Company Wide Settings “Air Moisture Indicators” from the default Wet bulb to the dew point. I suggest making this change if you have the authority to do so.

What can inside and return air dew point tell you? It will tell you how humid it is in the house.

If you are on a service call where the system is not running, you’ll probably find a high inside dew point, especially on a humid day with rain.Once the system is repaired, indoor dew point should return to normal.

But if you are on a maintenance, or a comfort consultation, taking an inside dew point measurement can identify a humidity problem that the occupant may not even be aware of. It will explain why there is condensation forming on the supply and even why mildew and biological growth are forming on surfaces around plumbing, duct, and electrical penetrations that are not sealed.

For the remainder of this article, I will go over various scenarios when checking dew point in 3 places:

1. Return Grille.
2. Return plenum
3. Supply Plenum.

![Condensation forming on a supply register](https://hvacknowitall.com/wp-content/uploads/2023/05/Condensation-forming-on-a-supply-register-1024x683.webp)Condensation forming on a supply register because of a high indoor dewpoint.

*The return grille* dew point and *return plenum* dew point are not always the same. And when they are drastically different, this is a huge red flag. In many places, the ducts run through unconditioned spaces like crawlspaces and attics, which generally have higher dew points.

Taking an initial indoor dew point reading at a return grille, you make find a normal dew point of 55F (13C).

Let’s say the return ducts run through an unconditioned attic to an air handler also in the attic. If you take a second dew point reading inside the return plenum at the air handler, you may find a much higher dew point, perhaps 65F (18C). That tells you that the return duct is picking up moisture!

Remember that dew point is an indicator of the *actual* moisture content in the air. How would a return duct pick up moisture? Through duct leakage! You may say: “I could’ve come to the same conclusion by measuring temperature instead of dew point.”

But if the ducts run through a very hot attic, the air is likely to pick up heat conducting through the walls of the duct, even if they are insulated, thus not proving there is leakage. Conversely, if the duct ran through a cool but humid crawlspace, you probably wouldn’t read a temperature rise (you might even read a temperature drop), but you definitely would see a dew point difference.

Remember, if fresh air is being introduced into the return plenum you would read a dew point difference at the return plenum. Understand that duct leakage is a huge source of indoor humidity problems.

![Dewpoint chart showing duct leakage](https://hvacknowitall.com/wp-content/uploads/2023/05/Dewpoint-chart-showing-duct-leakage.webp)Reading a vastly different Dewpoint between the return grille and the return plenum can indicate return duct leakage

I don’t often use the word “minutia,” but when I do, I often talk about things like supply air dew point. As warm air passes across the cold evaporator coil, the air molecules come into contact with the coil fins, and the moisture that the air contains starts falling out.

Theoretically, the air is “saturated” because it is cooled below its dew point. *When Dry Bulb and* dew point *temperatures are both the same the air is saturated.* In reality, not all the air comes into direct contact with the coil. Some of the air molecules pass through or around the coil unaffected.

This is called “coil bypass” – a condition where some air doesn’t make proper contact with the evaporator coil and therefore isn’t properly conditioned.

When that unaffected dry air then mixes back with the saturated air, the actual Dry Bulb might be 3-5 warmer than the dew point. The air is close to saturation but not quite saturated.

Let’s take an example with an air source heat pump in cooling mode. Reference the picture below.

If Supply Dry Bulb is 54F (12C) and the Supply dew point is 52F (11C) this tells us that the evaporator is cold and there is very little coil bypass. The air is close to saturation which is what we want. What if Supply is 59F (14C) but the supply air dew point is 52F (11C)?

What would cause such a large separation between Dry Bulb and dew point?

There may be a heat strip bank stuck on, reheating the air. Or there may be air bypassing the evaporator coil, mixing saturated air with unconditioned air. This can happen if the blower speed is set too high.

Sometimes the Supply air Dry bulb and dew point both read high while still being within a few degrees of each other. For example, Dry Bulb may be 58F (14C), and dew point is 56F (13C).

This usually indicates a high load on the evaporator, where coil temperature is higher than normal but leaving air is still close to saturation. The TXV is reacting to the high load. But measuring the dew point can alert a technician that there is a performance problem.

![normal-supply-air-conditions](https://hvacknowitall.com/wp-content/uploads/2023/05/normal-supply-air-conditions-1024x491.webp)Blue crosshair shows normal supply air conditions where the air is close to saturation. Purple crosshair shows an abnormal condition where the air is far from saturation.

The easiest way to get started is to get a pair of Bluetooth hygrometers that connect to Measurequick. Testo and Fieldpiece make some great products. Find a system cooling that is cooling properly and start a Non-Invasive test. Then, note the temperature and dew point at the return grille, return plenum, and supply plenum.

Think it through and be able to explain to yourself why you see these differences. Soon, you’ll get to the point where by taking the 3 dew point measurements alone, you’ll be able to quickly understand how the system is performing.

**Elevate Your Diagnostics with Property.com.** As a skilled HVAC technician mastering concepts like dew point, you know data is key. Property.com’s exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool provides critical homeowner and property insights (permit history, home value, potential savings) before you even arrive. Complement your technical expertise with unparalleled property intelligence. Join our invitation-only network, boost your credibility with a Property.com subdomain, and access tools designed for top-tier pros. Limited spots available per region. Learn more about securing your exclusive advantage.

![Measurequick app showing return and supply DP](https://hvacknowitall.com/wp-content/uploads/2023/05/Measurequick-app-showing-return-and-supply-DP-893x1024.webp)Measurequick has the ability to display Return and Supply air Dewpoint [DP].

| Measurement | What It Measures | Why It Matters for HVAC |
| --- | --- | --- |
| **Dew Point** | Actual amount of moisture in the air; temperature at which condensation forms | Directly indicates moisture content regardless of temperature; best for diagnosing humidity problems |
| **Relative Humidity** | Percentage of maximum possible moisture at current temperature | Changes with temperature even when moisture content remains the same; less reliable for diagnostics |
| **Wet Bulb** | Temperature reading affected by evaporation; used to calculate enthalpy | Important for calculating cooling loads and system capacity; used with dry bulb for psychrometric calculations |

- **Outdoor dew point above 63F (17C)** indicates high humidity conditions that can lead to moisture problems
- **Indoor dew point should not exceed 62.2F (16.7C)** according to ASHRAE Standard 55 to prevent mold growth
- **Different dew points between return grille and return plenum** often indicate duct leakage or air infiltration issues
- **Supply air dew point and dry bulb temperatures** should be close (within 3-5F) in a properly functioning system
- **Measure dew point in three key locations:** return grille, return plenum, and supply plenum for comprehensive diagnosis
- **Modern tools** like Bluetooth hygrometers with app integration make dew point measurement quick and easy

## Conclusion

Checking systems using dew point is quick and easy once mastered. It is non-invasive and does not require the use of gauges or even pipe temperature clamps. But it is not a substitute for proper commissioning and benchmarking system performance. Think of it as a quick performance screening.

If you see something abnormal, investigate further. Understanding dewpoint is a key step to becoming a better technician. Be sure to use it and become the best practitioner you can be.

### Check out our discussion with Tim DeStasio on Building Comfort

},
"datePublished": "2023-05-01",
"articleSection": "HVAC Diagnostics",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/understanding-dew-point-to-be-a-better-hvac-technician"
},
"about": [
]

},
"datePublished": "2023-02-01",
"image": "https://hvacknowitall.com/wp-content/uploads/2023/02/Fan-system-operating-point.webp",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/the-3-fan-laws-and-fan-curve-charts"
},
"about": [
],
"knowsAbout": [
"HVAC",
"Fan Laws",
"Fan Curves",
"Airflow",
"Equipment Selection"
]

},
},
},
},

--------------------------------------------------

# ID: 3385

## Title: Brazing Alternatives for HVACR Technicians: Modern Solutions for Today&#8217;s Challenges

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2022-09-21T08:00:01

## Word Count: 1917

## Categories: Education

## Tags: None

## Permalink: https://hvacknowitall.com/blog/brazing-alternatives

## Description:
## Brazing Alternatives for the Progressive HVACR Technician

Mention “brazing alternatives” to hardcore HVACR professionals, and you might get those mad face emojis in response! Understandably so – brazing provides a solid, proven connection that lasts for many years and remains a fundamental skill for all HVACR professionals.

While I don’t subscribe to the notion that “brazing is an art” (art is unique expression, while brazing should be a repeatable process with consistent results), I certainly respect its importance in our industry. Contrary to what some might think, I’m not anti-brazing – I simply enjoy exploring new technologies that can enhance our HVACR toolkit.

In this article, we’ll examine four proven brazing alternatives that every progressive technician should know about:

1. Pro Fit Quick Connect – Push-to-connect fittings for quick repairs
2. AC Smart Seal External – Leak sealant for inaccessible or difficult areas
3. FixQuick – Two-part repair system for specialized applications
4. Rapid Locking System – Press-to-connect system for comprehensive installations

I’ve personally tested these alternatives and will share my experience with each, including when and why you might choose them over traditional brazing methods. I’ve been particularly impressed with the [SolderWeld](https://solderweld.us/) products lately and how well the rods flow.

> [View this post on Instagram](https://www.instagram.com/p/CdenpUSLu2l/?utm_source=ig_embed&utm_campaign=loading)
>
> [A post shared by Gary McCreadie HVAC/R Tech/Business Owner (@hvacknowitall1)](https://www.instagram.com/p/CdenpUSLu2l/?utm_source=ig_embed&utm_campaign=loading)

There are several compelling reasons why brazing alternatives continue to be developed and adopted in our industry:

### Fire Safety Concerns

Fire hazards represent one of the most compelling reasons to explore brazing alternatives. I once worked in a facility that required a 4-hour fire watch after torch use – a time-consuming requirement in today’s fast-paced service environment. The building’s wooden beam construction made this precaution necessary but created significant workflow challenges.

“Hot work” fires occur more frequently than many realize. According to the National Fire Protection Association, [an average of 4,630 structure fires involving hot work occur each year](https://www.nfpa.org/-/media/Files/Code-or-topic-fact-sheets/HotWorkFactSheet.pdf), causing significant property damage and putting lives at risk.

As these statistics become better known, more building managers are implementing stricter rules around torch use, making brazing alternatives increasingly necessary for HVACR professionals.

### Health and Environmental Considerations

Brazing fumes contain numerous potentially harmful substances, particularly when working in poorly ventilated areas. My experience in data centers highlights this issue – these sealed environments maintain precise temperature and humidity levels, meaning fumes can linger for hours, affecting everyone in the space.

The University of Alabama’s [comprehensive guide on welding, cutting, and brazing safety](https://ehs.ua.edu/operations/occupational-safety/shop-safety/welding-cutting-brazing/) details the health risks associated with these processes.

### Specialized Environment Restrictions

Certain settings – medical facilities, pharmaceutical manufacturing plants, clean rooms, and other sensitive environments – may prohibit open flames entirely. In these locations, non-brazing alternatives aren’t just convenient; they’re mandatory.

This video provides additional perspective on when alternatives might be preferable:

RectorSeal’s [PRO-Fit Quick Connect](https://rectorseal.com/quickconnect-lp) offers a flame-free connection method that’s gaining popularity among service technicians. While my experience at the time of writing is limited to bench testing, numerous colleagues have reported excellent results in field applications.

These push-to-connect fittings excel in challenging service scenarios where:  
– Torch access is difficult (cramped attics, tight crawl spaces)  
– Fire permits would cause excessive delays  
– The environment prohibits open flames  
– Equipment or surroundings could be damaged by heat

### Installation Considerations

As with any pipe fitting method, proper preparation is crucial:  
1. Thoroughly clean the pipe to remove any debris or contaminants  
2. Use the included depth gauge to mark insertion depth on the pipe  
3. Ensure the pipe end is properly deburred and has no sharp edges  
4. Insert the pipe to the marked depth with a slight twisting motion

The PRO-Fit system particularly shines in emergency repair situations where minimizing system downtime is critical, such as in server rooms or other climate-controlled environments where temperature excursions could damage sensitive equipment.

> [View this post on Instagram](https://www.instagram.com/reel/ChlMkctPjcC/?utm_source=ig_embed&utm_campaign=loading)
>
> [A post shared by Gary McCreadie HVAC/R Tech/Business Owner (@hvacknowitall1)](https://www.instagram.com/reel/ChlMkctPjcC/?utm_source=ig_embed&utm_campaign=loading)

[AC Smart Seal External](https://www.coolairproducts.net/ac-smart-seal-external/) provides an innovative solution for addressing small external refrigerant leaks without brazing. This product has proven particularly valuable in my own service work.

My first real-world application was in a data center environment where a rub-through on a capillary line had caused a water regulator valve to lose its refrigerant charge. The environment presented multiple challenges:  
– Restricted access for bringing in torch equipment  
– Fire permit requirements that would delay repairs  
– Poor ventilation that would trap brazing fumes  
– Sensitive electronic equipment vulnerable to fire hazards

The application process is straightforward:  
1. Clean and dry the leak area thoroughly  
2. Apply the putty-like substance directly over the leak  
3. Allow proper curing time according to manufacturer specifications  
4. Pressure test the system to verify the seal  
5. Evacuate the system per standard procedures

In my case, the repair maintained system integrity for a full year until the valve could be completely replaced during scheduled maintenance. This example perfectly illustrates when an alternative to brazing isn’t just convenientit’s the superior technical solution.

For more details on proper system testing after repairs, see our guide on [pressure testing refrigeration systems](https://hvacknowitall.com/blog/pressure-testing-refrigeration-systems).

[FixQuick](https://www.coolairproducts.net/fixquick/) presents another innovative approach to leak repair without flames. In my bench testing, this system successfully maintained pressures up to approximately 400 PSIimpressive performance that suggests real-world reliability.

### How FixQuick Works

This two-component system consists of:  
1. A specialized liquid base  
2. A powder accelerant that triggers the hardening process

The chemical reaction between these components creates a durable seal capable of withstanding significant system pressures.

### Ideal Applications

FixQuick is particularly well-suited for:  
– Evaporator repairs where corrosion has weakened the metal, making heat-based repairs risky  
– Areas with restricted access where torch use would be challenging  
– Emergency repairs when minimizing downtime is critical  
– Locations where fire permits would cause significant delays

The product’s unique formulation gives it excellent adhesion properties even under challenging conditions, including the presence of oils and some contaminants (though proper cleaning is always recommended).

See FixQuick in action in this demonstration video:

The [Rapid Locking System (RLS)](https://www.rapidlockingsystem.com/) represents perhaps the most comprehensive brazing alternative for HVACR applications. This press-to-connect technology offers a complete solution for both repairs and full installations.

### System Components

RLS provides a comprehensive selection of:  
– Line fittings in various configurations  
– Valves for system control  
– Filter driers for contaminant removal  
– Sight glass assemblies for system monitoring

This diversity makes it possible to complete entire refrigeration projects without lighting a single torch.

### Personal Experience

While I haven’t personally completed full installation projects with RLS, I’ve successfully:  
– Performed numerous system repairs  
– Replaced filter driers in existing systems  
– Completed unfinished installation projects started by others

Each experience reinforced my confidence in the technology. The press connection process requires an initial investment in tools but delivers consistent, reliable results when proper procedures are followed.

### Learning Curve Considerations

RLS does represent a departure from traditional techniques, requiring:  
1. Proper training in the pressing process  
2. Understanding of the system’s specific preparation requirements  
3. Familiarity with the specialized tools  
4. Recognition of appropriate applications

The manufacturer provides extensive training resources to help technicians master these aspects. I strongly recommend reaching out to RLS directly if you’re interested in implementing this technology into your service offerings.

For a visual demonstration of the RLS system, check out this informative video:

When selecting from these brazing alternatives, consider the specific requirements of your job. This comparison table highlights key characteristics of each option:

| Alternative | Initial Cost | Application Type | Learning Curve | Pressure Rating | Best Used For |
| --- | --- | --- | --- | --- | --- |
| Pro Fit Quick Connect | Low-Medium | Repair/Limited Installs | Low | High | Emergency repairs, difficult access areas |
| AC Smart Seal External | Low | Repair Only | Very Low | Medium-High | Small pinhole leaks, emergency repairs |
| FixQuick | Low | Repair Only | Low | High | Corrosion-damaged components, emergency repairs |
| Rapid Locking System | High | Comprehensive Install/Repair | Medium | Very High | Complete installations, system retrofits |

### Cost Considerations

While some alternatives require a higher initial investment (especially RLS with its specialized tools), consider the long-term savings from:  
– Reduced labor time on complex installations  
– Eliminated fire permit requirements  
– Lower insurance costs from reduced fire risk  
– Expanded service capabilities in restricted environments

### Safety Advantages

All these alternatives share significant safety benefits:  
– Elimination of fire hazards  
– Reduced technician exposure to brazing fumes  
– Decreased risk of thermal damage to sensitive components  
– Lower liability risk in sensitive environments

### When to Stick with Brazing

Traditional brazing remains preferable when:  
– Working in well-ventilated areas with no fire restrictions  
– Maximum cost-efficiency is required on simple installations  
– Special high-temperature applications exceed alternative ratings  
– Unusual fitting configurations aren’t available in alternative systems

## Conclusion

The brazing alternatives covered in this article represent just the beginning of the technological evolution in our industry. As these technologies gain broader acceptance and prove their reliability, I predict we’ll see fewer torches lit in the coming years.

Each alternativePro Fit Quick Connect, AC Smart Seal, FixQuick, and the Rapid Locking Systemoffers unique advantages for specific applications. The progressive HVACR technician should understand when each solution makes the most sense from technical, safety, and business perspectives.

My advice: stay informed about emerging technologies and be willing to experiment with new methods. Knowledge remains our industry’s greatest asset, and familiarity with these alternatives expands your problem-solving toolkit.

Embracing new tech like brazing alternatives sets you apart. Ready to elevate your business further? Property.com offers exclusive access for top HVAC pros, providing advanced tools like ‘[Know Before You Go](https://mccreadie.property.com)’ homeowner insights, enhanced SEO presence with a custom subdomain, and AI-powered reputation management. Secure your limited spot in our network and showcase your commitment to quality and innovation. Learn more about Property.com’s early adopter benefits.

Want to learn more about HVAC tips and trends? Check out our [podcast](https://hvacknowitall.com/podcasts) and explore more in-depth [blog articles](https://hvacknowitall.com/blog) for expert advice and industry insights. Stay ahead in HVAC with the latest from HVAC Know It All!

]

},
"description": "Considering starting your own HVACR business? Learn the essential factors for success including technical experience, communication skills, resources, and business sense from an industry expert.",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/should-i-start-my-own-hvacr-business"

--------------------------------------------------

# ID: 3365

## Title: Inverter Compressor Technology: How TOSOT Mini Splits Maximize Indoor Capacity

## Type: blog_post

## Author: Unknown

## Publish Date: 2022-07-27T08:00:05

## Word Count: 814

## Categories: Air Conditioning, Heat Pumps

## Tags: None

## Permalink: https://hvacknowitall.com/blog/the-inverter-compressor

## Description:
## Inverter Compressor Technology: Game-Changing HVAC Innovation

**“The inverter compressor is the greatest invention in the HVAC industry in my lifetime.”**

I’ve made this statement repeatedly in this column and during TOSOT mini-split and APEX training events. This isn’t hyperbole it’s a conclusion backed by tangible evidence that continues to accumulate as the technology evolves.

One particularly remarkable feature of TOSOT multi-zone mini split systems has long intrigued me a capability that initially seemed counterintuitive during my contracting days and remains challenging to explain as a trainer. This feature deserves closer examination to truly appreciate its value in real-world applications.

The feature I’m referring to is the ability to install greater indoor capacity than outdoor capacity in a single system.

When I present this concept during training sessions, I often struggle to complete the explanation because, at first glance, it appears to violate fundamental HVAC principles. However, like many aspects of inverter mini split technology, we need to dig deeper to understand the true innovation at work.

Examining the TOSOT Standard Multi-Zone combinations chart reveals something surprising: 73 of the 123 approved configurations actually have more indoor capacity than outdoor capacity. For HVAC professionals accustomed to conventional systems, this raises an important question: How is this possible?

![AC Ductless Capacity Charts](https://hvacknowitall.com/wp-content/uploads/2023/02/AC-Ductless-Capacity-Charts-1.webp)

While you’re always ultimately limited by the outdoor unit’s maximum capacity, there’s more to the story. When examining the specifications of [TOSOT Standard Multi-Zone outdoor units](https://tosotamerica.com/product/standard-outdoor-multi-zone/), you’ll notice something significant: the 18K, 24K, and 30K outdoor units can actually deliver capacity exceeding their model numbers in both cooling and heating modes.

Furthermore, the 36K and 42K models exceed their nominal capacity specifically in heating mode.

Consider the approved combination of three 9K indoor units (9+9+9) paired with the TM24H4-O outdoor unit. Initially, this appears to be 27K of indoor capacity connected to a 24K outdoor unit a 3K deficit. However, closer inspection of the specifications reveals the TM24H4-O actually delivers up to 33K cooling capacity and 28K heating capacity more than sufficient to handle the combined 27K indoor requirement!

![AC Ductless Capacity Charts](https://hvacknowitall.com/wp-content/uploads/2023/02/AC-Ductless-Capacity-Charts-3.webp)

It’s important to note that not all approved combinations follow this exact pattern. Many TOSOT configurations genuinely represent more indoor capacity than outdoor capacity. In these cases, if all indoor units demand full capacity simultaneously, the system operates within the constraints of the outdoor unit’s maximum capacity, potentially resulting in slight derating of indoor units.

This characteristic exemplifies the versatility of inverter compressor technology as a modulating system. My example of three 9K indoor units with the TM24H4-O outdoor unit demonstrates how this can benefit both contractors and customers. Instead of upsizing to the more expensive TM30H4-O outdoor unit, you can maintain necessary capacity for all weather conditions while keeping equipment costs lower ultimately helping you get the job!

Leveraging advanced tech like inverter systems sets you apart. Property.com helps you capitalize on that edge. Gain exclusive access in your region, impress homeowners with ‘[Know Before You Go](https://mccreadie.property.com)’ insights (like potential energy savings!), and close more deals with flexible financing options. Secure your premium spot and early adopter pricing today.

This principle applies not only to the Standard Multi-Zone units in my example but extends to the UltraHeat Multi-Zone series as well:

![AC Ductless Capacity Charts](https://hvacknowitall.com/wp-content/uploads/2023/02/AC-Ductless-Capacity-Charts-2.webp)

## Final Thoughts: Redefining HVAC Possibilities

Even after years of working with TOSOT products, I continue to discover technical capabilities that challenge conventional HVAC assumptions and provide practical advantages for installations. These revelations continually reignite my enthusiasm for the technology.

The inverter compressor truly represents the greatest invention in the HVAC industry in my lifetime. Its ability to modulate performance, adapt to varying loads, and provide flexible installation options makes previously unthinkable system configurations not just possible but practical and efficient.

For HVAC professionals looking to provide cost-effective solutions without compromising performance, understanding these capacity relationships in inverter-driven systems provides a competitive edge that benefits both contractors and customers alike.

},
"image": "https://hvacknowitall.com/wp-content/uploads/2023/02/AC-Ductless-Capacity-Charts-1.webp",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/the-inverter-compressor/"
},
"mentions": [
},

--------------------------------------------------

# ID: 234

## Title: Thermal Imaging for HVAC: Essential Applications for Modern Technicians

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2022-03-05T16:47:00

## Word Count: 1277

## Categories: Education

## Tags: None

## Permalink: https://hvacknowitall.com/blog/thermal-imaging-for-hvac

## Description:
# Thermal Imaging for HVAC: Essential Applications for Modern Technicians

Thermal imaging has revolutionized how HVAC professionals diagnose problems and verify system performance. Once considered a luxury tool reserved for specialized technicians, thermal cameras have now become accessible to the average HVAC professional thanks to significant price reductions in recent years.

Today’s affordable thermal cameras offer powerful diagnostic capabilities that help identify issues invisible to the naked eye, demonstrate system performance to customers, and verify proper operation across various applications.

This article explores practical uses for thermal cameras in everyday HVAC work, showing how this technology can enhance your troubleshooting capabilities and service quality.

The following video demonstrates additional applications for thermal cameras in HVAC using the [HIKMICRO](https://www.hikmicrotech.com/en/product-c-detail/15) B20:

Loose electrical connections create resistance, which generates heat and increases amperage draw. This excess heat can lead to several significant problems:

- Premature component failure due to prolonged overheating
- Burned wiring insulation that creates fire hazards
- Emergency service calls that could have been prevented
- Shortened equipment lifespan

Before thermal imaging became accessible, technicians had to manually check each connection pointa time-consuming process that often meant disconnecting power multiple times during inspection.

Thermal cameras have transformed this process entirely. Now, technicians can:

1. Perform a quick scan of an energized electrical panel
2. Instantly identify hot spots that indicate loose connections or overloaded circuits
3. Power down only after locating specific problem areas
4. Make targeted repairs to the affected connections

This approach dramatically reduces diagnostic time while improving accuracy. In the past, only specialized electrical contractors with expensive equipment could provide this service. Today, any HVAC technician with a moderately priced thermal camera can perform these inspections during routine maintenance visits.

![blower door testing](https://hvacknowitall.com/wp-content/uploads/2022/03/blower-door-testing.webp)

Thermal cameras excel at identifying energy waste through air leakage detection, particularly when combined with blower door testing.

### How Blower Door Testing Works with Thermal Imaging

Blower door tests create pressure differences between indoor and outdoor environments to reveal air leakage points in the building envelope. When combined with thermal imaging, this technique becomes even more powerful:

1. The blower door fan depressurizes the building, creating negative pressure inside
2. This negative pressure actively pulls outside air through any leaks in the envelope
3. When temperature differences exist between indoor and outdoor air, thermal cameras can visualize these intrusions

For effective thermal detection, you need a sufficient temperature differential (delta T) between indoor and outdoor airideally 15F or greater. For example:

- Indoor temperature: 70F
- Outdoor temperature: 50F
- Delta T: 20F (sufficient for detection)

With these conditions and the building under negative pressure, a thermal camera will clearly show cooler outdoor air infiltrating through compromised windows, door frames, electrical outlets, and other leak points. This visual evidence helps technicians pinpoint exactly where energy-saving improvements are needed.

Just like a thermal camera reveals hidden issues, Property.com uncovers critical homeowner insights before you even arrive. Access permit history, home value, potential savings, and more with our ‘[Know Before You Go](https://mccreadie.property.com)’ tool. Join our exclusive network of certified pros, boost your SEO with a custom subdomain, and manage your reputation effortlessly. Limited spots available per region secure your advantage today. Learn more about Property.com’s premium tools for top HVAC contractors.

Thermal cameras don’t directly “see” air movement, but they can visualize temperature differences that reveal air distribution patterns when conditions are right.

This capability is particularly valuable in commercial spaces where verifying consistent air distribution is crucial for comfort and efficiency. With a properly set up thermal scan, you can:

- Confirm which diffusers and grills are actively supplying conditioned air
- Visualize the “throw” pattern (the distance air travels from the supply outlet)
- Identify areas receiving inadequate air distribution
- Detect unexpected temperature stratification in the space

For best results when visualizing air patterns:

1. Create a significant temperature differential between supply air and room air
2. Capture thermal images shortly after system startup when temperature differences are greatest
3. Take comparative images of different supply outlets under similar conditions

Remember that as supply air mixes with room air, the temperature differential diminishes, making patterns less visible over time. This makes timing important when conducting these evaluations.

This technique provides valuable reference points when balancing systems or troubleshooting comfort complaints in larger commercial installations.

Many HVAC technicians underutilize their thermal cameras by not properly adjusting the emissivity settings for different materials. This single setting can dramatically affect reading accuracy.

### What Is Emissivity?

Emissivity refers to how effectively a surface emits thermal energy compared to a perfect emitter (known as a “blackbody”). It’s expressed as a value between 0 and 1:

- **High emissivity (0.90-0.99)**: Materials that efficiently emit thermal energy, such as non-shiny surfaces, rubber, painted surfaces
- **Low emissivity (0.01-0.60)**: Materials that reflect more thermal energy than they emit, such as polished metals and reflective surfaces

As Brent Lammert from Hikmicro explains: “Thermal energy can be emitted by a target or reflected by it. Emissivity represents the percentage of what thermal energy is reflected versus emitted. The more reflective the surface, the lower the emissivity value it will have.”

Listen to Brent Lammert discuss thermal imaging with me on the HVAC Know It All Podcast.

### Setting Emissivity Correctly

Most thermal cameras offer:

1. **Pre-programmed settings** for common materials (recommended for beginners)
2. **Custom settings** for precise applications (recommended for experienced users)

For custom settings, consult an emissivity table for the specific material you’re measuring before adjusting your camera.

### Pro Tip for Comparing Different Materials

When comparing two surfaces with different textures (and therefore different emissivity values), your readings may be inconsistent. Here’s a professional workaround:

1. Apply a small piece of electrical tape to each surface you want to compare
2. Set your camera’s emissivity to 0.95-0.97 (the emissivity of electrical tape)
3. Measure the temperature of the tape on each surface

This technique creates a consistent measurement baseline, allowing for accurate temperature comparisons between materials that would otherwise be difficult to measure directly.

## Conclusion

Thermal imaging has transformed from a specialized luxury to an essential diagnostic tool for modern HVAC professionals. The applications we’ve coveredelectrical troubleshooting, energy assessments, airflow visualization, and proper emissivity settingsrepresent just a few ways this technology can improve your service efficiency and quality.

To get the most from your thermal camera:

- Read the manufacturer’s documentation thoroughly
- Practice in controlled environments to understand its capabilities and limitations
- Experiment with different settings for various materials and applications
- Use thermal imaging as part of your regular diagnostic process, not just for special cases

As you integrate thermal imaging into your daily workflow, you’ll discover countless applications that save time, improve accuracy, and provide compelling visual evidence to help customers understand system issues.

Boost your HVAC skills and stay ahead of the competition by exploring our comprehensive [blog articles](https://hvacknowitall.com/blog), tuning in to our technician-focused [podcast](https://hvacknowitall.com/podcasts), and subscribing to our YouTube channel for exclusive tips and best practices in HVACR.

},
"image": "https://hvacknowitall.com/wp-content/uploads/2022/03/blower-door-testing.webp",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/thermal-imaging-for-hvac"

--------------------------------------------------

# ID: 204

## Title: The Magic of Refrigerant: How Air-to-Air Heat Pumps Extract Heat from Cold Air

## Type: blog_post

## Author: Gerry Wagner

## Publish Date: 2022-01-16T16:05:00

## Word Count: 1314

## Categories: None

## Tags: None

## Permalink: https://hvacknowitall.com/blog/how-refrigerant-works

## Description:
## **THE MAGIC OF REFRIGERANT**

Mankind discovered fire approximately two million years ago. While I’m experienced in HVAC, I’m not quite that old, so I’ll trust the scientists on this timeline. Shortly after discovering fire, early humans began using it for one of its most practical applications: generating heat.

Water, being abundant and readily available, became the natural medium for transferring this heat. By heating water with fire and moving the wateror the steam it produced upon boilingto areas requiring warmth, our ancestors created the first rudimentary heating systems.

Hydronic heating systems can be traced back to the late 14th century, while steam heat documentation dates to as early as 1784. Consequently, when most of us think about central heating systems, we envision fire and water as the essential elements.

However, modern [**air-to-air heat pump systems**](https://phyxter.ai/blog/how-does-a-heat-pump-work) challenge this traditional thinking. Many homeowners struggle to understand how a system without fire or water can extract heat from outdoor air at temperatures as low as -30C (-22F). The answer lies in what I consider truly magical: the unique properties of refrigerant.

What many end users don’t realize is that air conditioners don’t create coolingthey extract heat from a room. In a cooling scenario, the **evaporator** (the coil in the conditioned room) passes room air over it via a fan. The **refrigerant** flowing inside the coil absorbs heat from the room air and transports it to the outside unit (**condenser**) where the heat is extracted (again via a fan) and dissipated into the outdoor atmosphere.

Now for the magical part: R410A refrigerant boils at an incredibly low temperature of -48.5C (-55.3F). This remarkable property allows it to absorb heat even when outdoor air temperatures plummet to -30C (-22F).

Making sense now? The transfer medium (refrigerant) used in an air-to-air heat pump is where the “magic” happenswithout it, our heating technology would be significantly less advanced.

Air-to-air heat pumps in HEAT mode simply reverse the [**refrigeration cycle**](https://www.hvacknowitall.com/blogs/blog/595767-the-refrigeration-cycle-explained) described earlier. The outdoor unit coil becomes the evaporator, and the indoor unit coil becomes the condenser, releasing the heat extracted from outdoor air into your home.

It’s also crucial to understand that the refrigerant changes state (from liquid to liquid/vapor to gas) as it circulates throughout the system. This phase change process is fundamental to how heat pumps work.

As we learned in elementary science, matter can change state. What’s less commonly explained is that when matter changes state, it produces energy during that processenergy that an air-to-air heat pump harnesses and converts into heat for your home.

The development of the inverter compressorthe “pump” in the air-to-air heat pumptook this technology to another level entirely.

An **inverter compressor** is best described as a modulating compressor, similar to your car’s engine. While homeowners aren’t expected to understand the technical details of compressor operation, most have a good understanding of how automobiles work.

When you push the gas pedal in your car, it accelerates. When you ease off the gas, it slows down. And when you set the cruise control, the car maintains a consistent speed. This is precisely how an inverter compressor works!

When the heating or cooling demand is high, the compressor will run up to 3600 RPMsimilar to conventional compressors. The critical difference is that when the demand decreases, the inverter compressor “eases off the gas,” using less energy while still providing comfort.

When the room temperature reaches the user’s desired setpoint (whether that’s 68F/20C, 70F/21C, or 72F/22C), the compressor enters “cruise control” mode, using just enough energy to maintain that comfortable temperature consistently.

Explaining complex tech like inverter heat pumps? Enhance your credibility and close more deals with Property.com. Our ‘[Know Before You Go](https://mccreadie.property.com)’ tool provides homeowner insights, while our exclusive network and reputation management tools establish you as the trusted expert. Limited spots available per region. Become a Property.com Pro today.

Modern air-to-air heat pumps offer significant efficiency advantages over traditional heating systems. By moving heat rather than generating it, heat pumps can deliver up to 300% efficiencymeaning for each unit of electricity consumed, they provide three units of heating energy. This translates to lower utility bills and reduced environmental impact.

In moderate climates, homeowners can expect energy savings of 30-40% compared to conventional electric resistance heating. Even in colder regions where temperatures regularly drop below freezing, today’s advanced heat pumps maintain impressive efficiency, though they may require auxiliary heat during extreme cold snaps.

The higher initial investment in heat pump technology typically pays for itself through these operational savings, with payback periods ranging from 3-7 years depending on local energy costs and climate conditions.

As we approach the conclusion, I must highlight the latest advancement in inverter compressor technology that adds another level of energy efficiency and low-temperature heating capability to air-to-air heat pumps.

TOSOT has developed what they call the “two-stage enhanced vapor injection compressor.” Now, being the straightforward instructor many of you know from my TOSOT product training events, I’ll be brutally honest: calling a compressor “vapor injection” is somewhat like saying your beer is “fire-brewed.” Of course it isthat’s what brewing entails!

The Stroh Brewery Company clearly had clever marketing that took an industry-standard practice and made it sound unique. Similarly, ALL compressors involve vapor injectionwe never compress liquid refrigerant, as that would cause severe system damage.

What makes the TOSOT system truly special and innovative is the **“two-stage”** portion of its description.

![Two-stage enhanced vapor injection compressor diagram showing refrigerant flow paths and pressure stages](https://hvacknowitall.com/wp-content/uploads/2022/11/2532928_500x0.jpg)

Adding a second “injection” point for refrigerant vapor at two different pressures allows for even greater energy production (in this context, heat). This occurs because energy is produced not only when matter changes state but also when that matter experiences pressure changes. When refrigerant moves between these different pressure zones, it releases additional thermal energy that conventional single-stage systems cannot capture.

## **TRANSLATING TECHNICAL MAGIC TO CUSTOMER VALUE**

HVAC professionals reading this article might be thinking, “Yeah, I knew all this already.” My hope is that this explanation helps you communicate the remarkable attributes of air-to-air heat pumps to your customers in accessible terms.

Technology has advanced tremendously over our long history, and while much of it may seem obvious to professionals, it’s worth taking a moment to appreciate the “magic” that defines our trade. When customers understand the ingenious principles behind heat pump operation, they’re more likely to appreciate the value of investing in this efficient, forward-thinking technology.

The next time a customer asks how a heat pump can possibly extract warmth from freezing air, you’ll have the perfect explanation: it’s not magicit’s refrigerant science, perfected through years of engineering innovation.

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/refrigerant-heat-transfer-in-air-to-air-heat-pumps"
},
"about": [
]

},

"image": "https://hvacknowitall.com/wp-content/uploads/2022/01/heat-pump-control-board-765x1024.webp",

"mainEntityOfPage": {

"@type": "WebPage",

"@id": "https://hvacknowitall.com/heat-pump-reversing-valves"

},

"articleSection": "HVAC",

"keywords": "heat pump, reversing valve, O terminal, B terminal, HVAC"

},
"image": "https://hvacknowitall.com/wp-content/uploads/2022/10/Electronic-Refrigerant-Leak-Detector-1024x683.webp",
"mainEntity": {
"@type": "Thing",
"name": "HVAC Internal Sealant",
"description": "A solution used to seal small refrigerant leaks in HVAC systems from inside the refrigerant circuit."
},
"mentions": [
]

},
"datePublished": "2021-11-01",
"dateModified": "2023-11-01",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/history-of-the-mini-split-air-conditioner"
},
"about": [
],
"mentions": [
]

],
"tool": [
],
"totalTime": "PT30M"

]

--------------------------------------------------

# ID: 127

## Title: Domestic Hot Water Generators in Geothermal Systems: Efficiency &#038; Performance Guide

## Type: blog_post

## Author: Matthew Showers

## Publish Date: 2021-11-14T13:39:00

## Word Count: 939

## Categories: None

## Tags: None

## Permalink: https://hvacknowitall.com/blog/domestic-hot-water-generator

## Description:
As discussed in my previous [article on geothermal heat pump basics](https://www.hvacknowitall.com/blogs/blog/665974-geothermal-heat-pump-basics#.YZEk22DMJPY), geothermal systems offer exceptional efficiency through several innovative features. One particularly valuable component is the Domestic Hot Water Generator (HWG), which harnesses heat from the system’s compressor discharge gas to pre-heat your home’s water supply. This dual-purpose functionality significantly reduces the energy consumption of your water heater while maximizing the overall efficiency of your geothermal investment.

Listen to Matt on the HVAC Know It All Podcast discussing the current state of the industry on this round table episode.

Before the primary refrigerant/water coaxial coil loop, geothermal systems equipped with HWG technology incorporate a secondary heat exchanger specifically for domestic water heating. This heat exchanger contains domestic water that circulates via an internal pump when the HWG function is enabled.

The system works by extracting heat from the compressor’s discharge gasheat that would otherwise be directed entirely to your home’s air or ground loop. This captured heat is transferred to your domestic water supply, which is then pumped into the bottom of your electric water heater or into a separate storage tank if you use a fossil fuel water heater. Rather than heating cold water directly from your main supply, the HWG effectively preheats the water to a setpoint of either 125F or 150F, depending on your configuration settings.

![Heating Cycle R410A showing the domestic hot water generator component in a geothermal system](https://hvacknowitall.com/wp-content/uploads/2021/11/Heating-Cycle-R410A.webp)*Diagram illustrating the refrigerant flow during heating mode with domestic hot water generation in a geothermal system. Image courtesy of [ClimateMaster](https://www.climatemaster.com/).*

The HWG function does influence overall system performance, which is why manufacturers typically conduct performance testing with the HWG disabled. This impact varies significantly between heating and cooling operation modes:

**During Cooling Mode:**  
When your geothermal system runs in cooling mode, it naturally generates heat that must be removed from your home. This heat is typically transferred to the ground loop for rejection. With the HWG enabled, a portion of this heat is diverted to your water supply insteadessentially putting waste heat to productive use without significantly affecting the cooling capacity of your system.

**During Heating Mode:**  
The performance impact is more noticeable in heating mode. Since the system is actively generating heat to warm your home, any heat diverted to water heating represents energy not available for space heating. This creates a slight reduction in heating capacity, though the overall energy efficiency of your home may still improve when considering both space and water heating needs together.

Despite this minor performance reduction during heating mode, many professionalsmyself includedrecommend leaving the HWG enabled year-round for maximum overall energy savings. The benefits of reduced water heating costs typically outweigh the slightly reduced heating capacity, especially in moderate climates.

Converting to a geothermal system with an active HWG can significantly reduce your water heating costs compared to conventional water heating methods. The potential savings vary based on several factors:

- **Electric Water Heaters:** Homes with electric water heaters typically see the most dramatic savings, often reducing water heating energy consumption by 30-50% when an HWG is properly implemented.
- **Gas Water Heaters:** While savings are still substantial with gas water heaters, they’re typically lower than with electric units due to the generally lower operating cost of gas. However, HWG pre-heating can still reduce gas water heating costs by 20-40%.
- **Seasonal Considerations:** During cooling season, the HWG essentially provides “free” water heating by utilizing heat that would otherwise be rejected. During heating season, there’s a small trade-off between space heating and water heating efficiency.

The U.S. Department of Energy estimates that water heating accounts for approximately [20% of a typical home’s energy use](https://www.energy.gov/energysaver/water-heating), making the HWG function a significant contributor to a geothermal system’s overall efficiency and cost-effectiveness.

Working on advanced systems like Geothermal? Elevate your service with Property.com. Access exclusive homeowner insights like permit history and potential savings with our ‘[Know Before You Go](https://mccreadie.property.com)’ tool. Secure your limited spot in our network, boost your SEO with a custom subdomain, and gain Property.com Certification. Join the elite network inquire about early adopter benefits today!

## In Conclusion

Domestic Hot Water Generators represent one of the many ways geothermal systems maximize efficiency by providing multiple benefits from a single installation. By capturing and repurposing heat that would otherwise be wasted or directed elsewhere, HWGs can significantly reduce water heating costs while maintaining comfortable indoor temperatures. Despite the minor performance impacts during heating mode, the overall energy efficiency advantages make HWGs a valuable component of any geothermal system.

## **Tune Into the HVAC Know It All Podcast for Expert Tips and Industry Insights**

Ready to dive deeper into HVAC tips and tricks? Tune in to our [**HVAC Know It All podcast**](https://hvacknowitall.com/podcasts), where we discuss the latest industry trends, answer your burning questions, and share expert advice to keep your home comfortable year-round. Don’t miss outsubscribe now and never miss an episode!

},
"image": "https://hvacknowitall.com/wp-content/uploads/2021/11/Heating-Cycle-R410A.webp",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blogs/blog/hvac-tip-domestic-hot-water-generator-and-geothermal-systems"
},
"keywords": [
"Domestic Hot Water Generator",
"HWG",
"Geothermal Systems",
"HVAC",
"Energy Efficiency",
"Water Heating"
],
"articleSection": "HVAC Technology",
"proficiencyLevel": "Intermediate"

],
"step": [
]

]

],
"tool": [
]

]
},
"proficiencyLevel": "Expert"

--------------------------------------------------

# ID: 380

## Title: Understanding Superheat in HVAC Systems: Expert Insights with Jamie Kitchen

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2021-06-22T06:42:00

## Word Count: 694

## Categories: Air Conditioning

## Tags: None

## Permalink: https://hvacknowitall.com/blog/the-ins-and-outs-of-superheat

## Description:
# Understanding Superheat in HVAC Systems: Expert Insights with Jamie Kitchen

## The Critical Role of Superheat in HVAC Performance

Superheat is one of the most fundamental yet frequently misunderstood concepts in refrigeration and air conditioning. This critical measurementthe temperature of refrigerant vapor above its saturation pointdirectly impacts system efficiency, performance, and longevity.

On this [episode](https://anchor.fm/hvacknowitall/episodes/The-Ins-And-Outs-Of-Superheat-wJamie-Kitchen-e12j829) of the HVAC Know It All Podcast, host Eric Aune takes a comprehensive dive into superheat with Jamie Kitchen, a technical training expert from Danfoss. This conversation breaks down the complex principles of superheat into practical knowledge that every HVAC professional can apply in the field.

[![HVAC Know It All Podcast Episode on Superheat with Jamie Kitchen](https://d14ty28lkqz1hw.cloudfront.net/data/org/15112/media/img/source/edit/2392875_edit.jpg)](https://anchor.fm/hvacknowitall/episodes/The-Ins-And-Outs-Of-Superheat-wJamie-Kitchen-e12j829)

Superheat refers to the additional heat energy absorbed by refrigerant vapor after it has completely evaporated. Measured in degrees, superheat is the difference between the actual temperature of the refrigerant vapor and its saturation temperature at a given pressure.

Understanding and properly measuring superheat is essential for:

- Ensuring compressor protection from liquid refrigerant damage
- Optimizing system efficiency and performance
- Diagnosing system issues and potential problems
- Properly charging refrigeration systems
- Maintaining appropriate evaporator coil operation

This podcast episode explores these concepts in detail, providing both theoretical knowledge and practical applications for field technicians.

In this in-depth conversation with Jamie Kitchen from Danfoss, listeners will gain valuable insights into:

- The fundamental principles behind superheat
- Different methods for accurately measuring superheat
- Common mistakes technicians make when working with superheat
- Troubleshooting systems using superheat readings
- The relationship between superheat and system performance
- Best practices for optimizing superheat in various system types
- How superheat interacts with other critical system parameters

Whether you’re a seasoned professional or new to the field, this episode offers valuable knowledge to enhance your understanding of refrigeration systems.

You’ve mastered technical details like superheat. Now, elevate your business profile with Property.com. Gain exclusive access to homeowner insights with our ‘[Know Before You Go](https://mccreadie.property.com)’ tool, AI-powered reputation management, and premium branding that reflects your expertise. Limited spots available for top HVAC pros in your region. Learn more about becoming a Property.com Certified Pro and unlock early adopter benefits.

Jamie Kitchen is a respected technical training expert at Danfoss, a global leader in advanced technologies for refrigeration, air conditioning, and other industries. With extensive experience in the HVAC field, Jamie brings practical knowledge and technical expertise to complex topics like superheat, making them accessible to technicians at all experience levels.

Danfoss is known for manufacturing high-quality components for refrigeration and air conditioning systems, including expansion valves, compressors, and controllers that help maintain proper superheat in HVAC systems.

Stay updated with the latest HVAC knowledge and industry insights:

- Subscribe to the [HVAC Know It All app](https://bluecollarguru.disciplemedia.com/signup)
- Follow HVAC Know It All on [Instagram](https://www.instagram.com/hvacknowitall/), [Facebook](https://www.facebook.com/hvacknowitall/), [YouTube](https://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ/videos) and [LinkedIn](https://www.linkedin.com/company/hvac-know-it-all-inc/?viewAsMember=true)
- ***LISTEN*** to the [HVAC Know It All Podcast](https://anchor.fm/hvacknowitall)

**Save 8%** on purchases at [TruTech Tools](http://www.trutechtools.com/) with code knowitall (excluding Fluke and Flir products)

[![Testo](https://d14ty28lkqz1hw.cloudfront.net/data/org/15112/media/img/source/edit/1539749_edit.png)](http://www.testo.com/)

## Enhance Your HVAC Skills with Expert Knowledge

Understanding superheat is crucial for any HVAC professional looking to improve diagnostics, system performance, and overall service quality. This podcast episode with Jamie Kitchen provides the technical insights and practical knowledge you need to master this essential concept.

Listen to the full episode to deepen your understanding of superheat and improve your ability to diagnose and optimize HVAC systems in the field. The knowledge you gain will directly translate to better service for your customers and enhanced professional expertise for your career.

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/reputation-marketing-and-online-reviews-to-grow-your-business-w-shawn-hill"
},
"about": [
],
"mentions": [
},
],
"isPartOf": {
"@type": "PodcastEpisode",
"name": "Reputation Marketing and Online Reviews To Grow Your Business w/Shawn Hill",
"url": "https://anchor.fm/hvacknowitall/episodes/Reputation-Marketing-and-Online-Reviews-To-Grow-Your-Business-wShawn-Hill-e124oap",
"partOfSeries": {
"@type": "PodcastSeries",
"name": "HVAC Know It All Podcast"

},
"mainEntity": {
"@type": "ItemList",
"itemListElement": [
]

--------------------------------------------------

# ID: 337

## Title: Reputation Marketing for HVAC Businesses: A Complete Strategy Guide

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2021-05-17T04:22:00

## Word Count: 1933

## Categories: Business Growth

## Tags: None

## Permalink: https://hvacknowitall.com/blog/why-hvac-companies-need-to-focus-on-reputation-marketing

## Description:
# Reputation Marketing for HVAC Businesses: A Complete Strategy Guide

In today’s digital marketplace, your HVAC company’s online reputation is arguably your most powerful marketing asset. Reputation marketingthe strategic use of customer reviews, testimonials, and positive brand mentions in your promotional effortscombines the best elements of brand marketing and reputation management to drive business growth.

When implemented effectively, reputation marketing boosts sales, enhances your brand image, lowers customer acquisition costs, and increases revenue. The power lies in establishing trust with potential customers before they even speak with your sales team, using authentic feedback from satisfied clients as persuasive trust signals.

This comprehensive guide explains what reputation marketing is, why it’s particularly crucial for HVAC businesses, and provides actionable strategies to implement in your marketing plan.

![](https://hvacknowitall.com/wp-content/uploads/2022/11/5f76559d2b99de481384abba_NiceJob-Reputation-Marketing-Get-More-Online-Reviews-Banner-1024x427.jpg)

Reputation marketing is the strategic utilization of your company’s earned reputation as a promotional asset. It involves both acquiring positive brand content and amplifying it through your marketing channels. The assets you’ll leverage include customer reviews, testimonials, online ratings, industry awards, and social media mentions.

Unlike traditional brand marketingwhere you tell consumers about your company’s values and servicesreputation marketing lets your satisfied customers do the talking for you. It showcases what others say about your business rather than what you say about yourself.

This approach differs significantly from reputation management, which focuses on monitoring, responding to, and mitigating negative reviews. While reputation management plays defense, reputation marketing plays offense by proactively collecting positive feedback and strategically featuring it across multiple channels.

### Reputation Marketing vs. Reputation Management

Over the past few years, there has been a noticeable shift from reputation management to reputation marketing because the latter delivers higher business impact. Consider these key differences:

Reputation management influences customer perception by avoiding and responding to negative reviews. It’s reactive and focused on damage control. While handling negative reviews tactfully remains crucial, it’s only part of the equation.

Reputation marketing is proactive and growth-oriented. It involves two main components:

1. **Build your reputation**: Systematically collect positive reviews and testimonials from satisfied customers. Tools like NiceJob’s [reputation marketing software](https://get.nicejob.co/?utm_source=NiceJob&utm_medium=blog&utm_campaign=What%20Is%20Reputation%20Marketing%3F%20The%20Complete%20Guide&__hstc=124093461.9117080f5ad6953e10f207172f7a089a.1617808401616.1619475571221.1619541389776.8&__hssc=124093461.5.1619541389776&__hsfp=404667856) can help automate this process.
2. **Market your reputation**: Strategically display these trust signals across your website, social media, advertising campaigns, and third-party platforms to drive sales.

For HVAC businesses operating in highly competitive local markets, this approach creates a powerful competitive advantage that’s difficult for competitors to replicate.

In the highly competitive HVAC industry, where technical expertise is difficult for consumers to evaluate before purchase, your online reputation serves as a critical decision-making factor for potential customers.

Consider these compelling statistics about the impact of reviews on consumer behavior:

- 97% of customers say reviews influence their buying decisions, with 90% trusting reviews more than anything a salesperson says
- Customers typically read ten reviews before making a purchase decision and consider reviews 12 times more credible than sales copy
- Websites displaying customer reviews see 74% higher contact rates than those without reviews
- Just ten quality customer reviews can increase your search traffic by 15-20%
- Advertisements featuring reviews and user-generated content achieve 300% higher click-through rates while reducing cost-per-click and cost-per-acquisition by 50%

For HVAC contractors, these statistics are particularly significant because:

1. **High-value transactions**: HVAC services often represent significant investments for homeowners, increasing their desire for reassurance
2. **Technical complexity**: Most customers can’t evaluate the technical quality of HVAC work, making them more reliant on others’ experiences
3. **Emergency situations**: When facing urgent HVAC problems, customers need to quickly identify trustworthy providers
4. **Long-term relationships**: Customers seek contractors they can trust for ongoing maintenance and future system replacements

In this environment, simply managing your reputation by responding to negative reviews is no longer sufficient. To truly succeed, you need to actively build, showcase, and leverage your reputation as a central element of your marketing strategy.

Ready to elevate your HVAC business’s reputation and local visibility? [Property.com](https://mccreadie.property.com) offers an exclusive network for top contractors, featuring AI-powered review management, social media tools, and a premium subdomain to boost your SEO. Secure your limited spot, gain Property.com certification, and turn your hard-earned reputation into more business. Explore the Property.com Pro advantage today!

Let’s explore four powerful ways to implement reputation marketing in your HVAC business, with practical examples and implementation tips for each approach.

### 1. Showcase Customer Reviews on Your Website

Your website offers multiple opportunities to highlight positive customer experiences:

![](https://hvacknowitall.com/wp-content/uploads/2022/11/HVAC-11-1024x486.jpg)

**Dedicated Reviews Page**: Create a comprehensive reviews section that aggregates feedback from multiple platforms. This example from Los Angeles-based [SoCal HVAC Specialist Heating & Air Conditioning](https://hvacheatingcooling.com/reviews) automatically embeds reviews from Google, Facebook, Yelp, and other platforms, creating an impressive wall of positive feedback.

**Real-Time Review Widget**: Implement a subtle but noticeable widget that displays recent positive reviews as website visitors browse your site. This serves as a constant reminder of your company’s quality service without being intrusive.

![](https://hvacknowitall.com/wp-content/uploads/2022/11/5f7658f8c578e421c254979a_NiceJob-Engage-for-Reputation-Marketing.png)

**Homepage Review Section**: Feature select reviews prominently on your homepage. One study found that adding a review directly below the hero section improved conversion rates by an impressive 56.2%. This approach from Oregon’s [Bridge City HVAC](https://bchandr.com/) effectively builds trust at a critical decision point in the customer journey.

![](https://hvacknowitall.com/wp-content/uploads/2022/11/Screen-Shot-2021-04-28-at-3.01.37-PM-1024x334.png)

**Implementation Tip**: When selecting reviews to feature prominently, choose those that specifically mention common customer concerns like responsiveness, technical expertise, cleanliness, and fair pricing.

### 2. Integrate Reviews into Your Advertising

Incorporating reputation elements into your paid advertising significantly improves performance metrics:

**Social Media Ads with Testimonials**: Create sponsored posts featuring actual customer testimonials to generate engagement and trust. These ads perform particularly well because they combine social proof with targeted messaging.

![](https://hvacknowitall.com/wp-content/uploads/2022/11/pasted-image-0.png)

**Google Ads with Seller Ratings**: Take advantage of Google’s automated seller ratings extension, which can increase click-through rates by 10%. These display your average review score and review count directly in your advertisements, instantly establishing credibility.

![](https://hvacknowitall.com/wp-content/uploads/2022/11/pasted-image-0-1-1.png)

**Local Services Ads**: Since these ads operate on a pay-per-lead model rather than a bidding system, your review quality and quantity become critical factors in ad placement and performance.

![](https://hvacknowitall.com/wp-content/uploads/2022/11/5f766f6e1a843e04f9c6dcf2_Reputation-Marketing-Local-Services-Ad-1.png)

**Implementation Tip**: Refresh your ad creative regularly with recent reviews to keep content current and highlight seasonal service feedback (e.g., featuring heating system reviews in fall, AC installation reviews in spring).

### 3. Share Reviews on Social Media

Social platforms offer excellent opportunities to amplify positive customer experiences:

**Organic Review Posts**: Regularly share customer reviews as standard social media posts. This maintains regular, positive content without requiring constant creation of new marketing materials.

![](https://hvacknowitall.com/wp-content/uploads/2022/11/HVAC-10.jpg)

**Awards and Recognition**: Share industry awards, community recognition, and certification achievements. These third-party validations provide powerful trust signals.

![](https://hvacknowitall.com/wp-content/uploads/2022/11/HVAC-10-1.jpg)

**Implementation Tip**: Create a quarterly calendar for sharing reviews across your social channels to ensure consistent reputation marketing throughout the year, with increased frequency during your peak seasons.

### 4. Leverage Third-Party Review Platforms

Beyond your own channels, numerous review platforms influence potential customers:

**Claim and Optimize Listings**: Ensure your business is properly represented on Google Business Profile, Facebook, Yelp, BBB, Angi, HomeAdvisor, and industry-specific platforms.

**Respond to All Reviews**: Show potential customers your commitment to service by professionally responding to both positive and negative reviews.

**Implementation Tip**: Create a standardized process for requesting reviews after service completion. The ideal time is within 24-48 hours of job completion, when customer satisfaction is highest.

A medium-sized HVAC contractor in the Midwest implemented a comprehensive reputation marketing strategy with impressive results:

**Challenge**: Despite providing excellent service, the company struggled to stand out in a crowded market and convert website visitors into leads.

**Solution**: They implemented a three-pronged reputation marketing approach:  
1. Systematically requested reviews after each service call  
2. Featured top reviews prominently on their homepage and service pages  
3. Created Google and Facebook ads featuring actual customer testimonials

**Results** (after 6 months):  
– 63% increase in website conversion rate  
– 27% reduction in cost-per-lead  
– 42% increase in service calls from new customers  
– Achieved #1 Google ranking for “reliable HVAC contractor [city name]”

The key insight: By letting satisfied customers tell their story rather than simply promoting service offerings, the company created more authentic connections with potential customers.

Ready to implement reputation marketing in your HVAC business? Use this practical checklist to get started:

### Foundation Building

- [ ] Audit your current online presence across Google, Facebook, Yelp, and industry directories
- [ ] Claim and verify all business listings
- [ ] Create a standardized process for requesting reviews after service completion
- [ ] Train technicians to mention reviews when completing jobs
- [ ] Implement a reputation management platform to track reviews across all sites

### Website Enhancement

- [ ] Add a dedicated reviews page to your website
- [ ] Feature select reviews on your homepage and service pages
- [ ] Implement schema markup for reviews to improve SEO
- [ ] Add a real-time review widget to display fresh feedback
- [ ] Ensure your website is mobile-friendly for customers leaving reviews

### Marketing Integration

- [ ] Incorporate reviews into your Google Ads campaigns
- [ ] Create social media graphics featuring customer testimonials
- [ ] Add review snippets to email newsletters
- [ ] Feature reputation elements in direct mail campaigns
- [ ] Include review information on business cards and leave-behind materials

### Ongoing Management

- [ ] Schedule time weekly to respond to all new reviews (positive and negative)
- [ ] Track review metrics monthly (volume, average rating, sentiment)
- [ ] Regularly update featured reviews to maintain freshness
- [ ] Monitor competitor review strategies
- [ ] Analyze which types of reviews generate the best customer response

## Dominate Your Local HVAC Market with Reputation Marketing

Reputation marketing represents a powerful approach for HVAC companies looking to differentiate themselves in competitive local markets. By systematically collecting positive customer feedback and strategically featuring it across multiple channels, you transform your satisfied customers into a persuasive marketing force.

The most successful HVAC contractors understand that today’s consumers trust peer recommendations far more than traditional advertising claims. By implementing the strategies outlined in this guideshowcasing reviews on your website, incorporating testimonials into advertising, sharing positive feedback on social media, and leveraging third-party review platformsyou create multiple touchpoints where potential customers encounter authentic evidence of your quality service.

Remember that effective reputation marketing requires both acquiring positive reviews and strategically deploying them. The effort invested in building this reputation asset delivers substantial returns through improved conversion rates, enhanced search visibility, and increased customer trust.

For HVAC businesses ready to grow, reputation marketing isn’t just an optionit’s an essential strategy for sustainable success in today’s digital marketplace.

## More Ways to Grow Your HVAC Business

Listen to what an [HVAC community member](https://www.youtube.com/watch?v=f8_XkO2cXJ4&ab_channel=NiceJob) does in efforts to gather more social proof.

NiceJob Blog is in collaboration with [HVAC Know It All](https://nicejob.grsm.io/HVACKnowItAllBlog).

NiceJob is a reputation marketing platform designed to ensure the great work done by small businesses never goes unrecognized, unappreciated or unrewarded. Get 2x more reviews, convert website traffic to leads with NiceJob, and watch the sales roll in.

},
"datePublished": "2023-07-25",
"dateModified": "2023-07-25"

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/indoor-air-monitoring-to-increase-iaq"
},
"keywords": "indoor air quality, IAQ monitoring, HVAC, humidity control, air filtration, MERV ratings, ventilation, HRV, ERV, PM2.5, VOC, CO2, IAQ sensors",
"about": [
],
"image": [
"https://hvacknowitall.com/wp-content/uploads/2021/04/Aprilaire-1830-70-pint-dehumidifier-.webp",
"https://hvacknowitall.com/wp-content/uploads/2021/04/Haven-IAQ.webp"
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/geothermal-heat-pump-basics"
},
"image": {
"@type": "ImageObject",
"url": "https://hvacknowitall.com/wp-content/uploads/2022/11/2338620\_edit-767x1024.jpg",
"width": "767",
"height": "1024"
},
"keywords": "geothermal heat pump, open loop, closed loop, HVAC, heat pump efficiency, geothermal installation"

},
"datePublished": "2020-12-01",
"dateModified": "2023-12-01",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/cracked-heat-exchangers-in-furnaces-what-should-we-do/"
},
"keywords": [
"cracked heat exchanger",
"furnace safety",
"carbon monoxide",
"HVAC troubleshooting",
"heat exchanger inspection"
],
"articleSection": "HVAC Safety",
"proficiencyLevel": "Expert"

},
"image": "https://hvacknowitall.com/wp-content/uploads/2020/12/refrigerant-slider.webp",
"articleSection": "HVAC Education",
"keywords": "refrigeration cycle, HVAC, refrigerant, superheat, subcooling, compressor, condenser, evaporator, metering device",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/refrigeration-cycle-explained"

--------------------------------------------------

# ID: 153

## Title: Preventing Oil Loss in Industrial Refrigeration Screw Compressors: Expert Troubleshooting Guide

## Type: blog_post

## Author: Unknown

## Publish Date: 2020-12-20T14:54:00

## Word Count: 1192

## Categories: Refrigeration

## Tags: None

## Permalink: https://hvacknowitall.com/blog/oil-loss-in-refrigeration-screw-compressors

## Description:
# Preventing Oil Loss in Industrial Refrigeration Screw Compressors: Expert Troubleshooting Guide

During a recent conversation with industry colleagues, I was surprised to hear the widespread belief that “topping off” oil in screw compressors every few months is considered standard maintenance for refrigeration facilities. This perspective prompted me to share my expertise on oil loss in screw compressorsa topic where misconceptions can lead to unnecessary maintenance and potential system inefficiencies.

![Refrigeration screw compressors (2)](https://hvacknowitall.com/wp-content/uploads/2020/12/Refrigeration-screw-compressors-2.webp "Industrial refrigeration screw compressors in a mechanical room")

Throughout my career in industrial refrigeration service and facility operations, I’ve encountered numerous opinions about oil loss and migration. Many technicians and operators believe that regularly replenishing oil charge is simply part of normal maintenance procedures.

In my professional assessment, this is a significant misconception that often stems from practices developed during the “Vilter” or “Fuller” era. These older compressors did indeed bypass considerable amounts of oil annuallyit was, as we say in the field, “the nature of the beast.” However, modern screw compressor technology functions quite differently, and understanding these differences is crucial for proper maintenance.

The industry transition to twin rotary screw compressors marked a significant technological advancement. These larger, more efficient machines came equipped with substantial separators. However, despite the additional training that accompanied these systems (or sometimes the lack thereof, depending on your employer), one critical aspect rarely received adequate attention: oil usage rates and coalescing filter efficiency.

[![HVAC Know It All Podcast](https://hvacknowitall.com/wp-content/uploads/2022/10/HVAC-Know-It-All-Podcast-2-1024x683.webp "HVAC Know It All Podcast - Listen for more expert insights")](https://hvacknowitall.com/podcasts)

The reality is that properly installed coalescing filters operate with remarkable efficiency. I’ve maintained compressors that operated for years without requiring additional oil. According to industry data, high-quality coalescing filters typically pass only a few tablespoons of oil annually, depending on filter specifications.

In my troubleshooting experience, most gradual oil loss issues trace back to one primary cause: incorrect installation of coalescing filters.

![Oil separator example from Bitzer](https://hvacknowitall.com/wp-content/uploads/2020/12/Oil-separator-example-from-Bitzer.webp "Oil separator component from Bitzer refrigeration equipment")

### Gradual Oil Loss Issues

Several factors beyond filter installation can contribute to gradual oil loss:

**1. Oil Return Valve Adjustment**  
Insufficient opening of the oil return valve is a frequent culprit. The amount of oil “smoke” passing between coalescing filters varies with load and velocities. This variation can lead to oil accumulation in the coalescing area of your separator. I’ve encountered this issue multiple timesthe solution is typically a minor adjustment to the oil return valve.

**2. Overfilling During Maintenance**  
Many technicians overfill compressors during oil changes or when topping off. According to Frick’s specifications, the proper operating level should be maintained between the two sight glasses. When adding oil, you should run the level until it just becomes visible in the top sight glass.

This practice prevents oil from spilling into the cavity between the oil separator and the coalescing filter wall. Overfilling can significantly shorten coalescing filter life. Any liquid entering a coalescing filter can damage it or cause a “blow-out,” depending on the quantity. Repeatedly filling to the top sight glass can force oil into the coalescers.

### Specific Oil Loss Scenarios and Solutions

**Sudden Oil Loss Through the Suction Port:**

- **Failed Suction Check Valve**: When the suction check doesn’t hold, the compressor can back-spin. This allows oil to travel up the suction line and discharge into the system.
- *Diagnostic Sign*: Watch for coupling rotating backward
- *Solution*: Repair or replace the check valve
- **Excessive Suction Check Valve By-pass**: If the by-pass line is opened too far, oil loss can occur.
- *Solution*: Adjust the by-pass opening to manufacturer specifications

**Continuous Oil Loss Through the Economizer Port:**

- **Economizer Check Valve Failure**: This commonly causes oil to migrate between compressors.
- *Solution*: Repair the existing check valve or upgrade to a piston-style check valve for better sealing

**Mastering complex systems like screw compressors sets you apart. Ready to elevate your business profile too?** Property.com offers exclusive, invitation-only memberships for top HVAC/R pros. Gain a competitive edge with our ‘[Know Before You Go](https://mccreadie.property.com)’ tool providing critical property insights, boost your SEO with a premium Property.com subdomain, and access advanced client financing options. Secure your limited spot in [Your Region] and lock in early adopter rates. Learn more about joining Property.com’s elite network.

**Continuous Oil Loss Through the Discharge Port:**

- **Coalescing Element Issues**: The most common cause of discharge port oil loss.
- *Diagnosis*: Oil travels to condensers and circulates through the system
- *Potential Problems*:

  - Faulty or worn coalescing elements (solution: replacement)
  - Improperly installed elements (solution: correct installation)
  - Bulkhead gasket leaks (solution: inspect and replace gasket)
- **Oil Quality or Management Problems**:
- Foaming oil being carried out (solution: check for refrigerant contamination)
- Incorrect oil type (solution: replace with manufacturer-recommended oil)
- Mixed oil types (solution: full oil change with correct type)
- Improper liquid injection settings (solution: adjust per specifications)
- Oil level maintained too high (solution: lower to recommended level)

**System Operating Condition Factors:**

- **Pressure-Related Issues**:
- Low differential pressure causing excessive velocity across the separator
- Discharge pressure lower than design parameters, increasing vapor velocity
- Sudden discharge pressure drops causing oil foaming
- **Filter and Return Problems**:
- Liquid carryover or slugging fouling the coalescing filters
- Nonfunctional coalescing oil return due to closed valve or plugged line/valve
- **Modern screw compressors should not require regular oil “top-offs”** if properly maintained.
- **Coalescing filters are extremely efficient when correctly installed** and should only pass minimal oil (tablespoons per year).
- **Maintain proper oil levels** between sight glasses according to manufacturer recommendations.
- **Check valve function is critical** at the suction, economizer, and discharge points to prevent oil migration.
- **System pressure parameters** directly affect oil retention and should be monitored against design specifications.
- **Regular maintenance inspections** should include checking oil return valve positions and coalescing filter condition.

## Conclusion

This article doesn’t cover every possible cause of oil loss in screw compressors, but focuses on common misconceptions about gradual oil loss that I’ve encountered throughout my career. Understanding these issues can prevent unnecessary maintenance and potential system damage.

If you have questions about this information, please [shoot me an email](https://hvacknowitall.com/contact-us). This article reflects my professional opinion based on field experience, research, and training. The additional reference list from Gartner refrigeration provides a comprehensive overview of oil loss issues.

Follow HVAC Know It All on [Instagram](https://www.instagram.com/hvacknowitall/), [Facebook](https://www.facebook.com/hvacknowitall/), [YouTube](https://www.youtube.com/@HVACKnowItAll) and [LinkedIn](https://www.linkedin.com/in/gary-mccreadie-38217a77/) and **LISTEN** to the [HVAC Know It All Podcast](https://hvacknowitall.com/podcasts)

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/industrial-refrigeration-oil-loss-in-refrigeration-screw-compressors"

--------------------------------------------------

# ID: 391

## Title: Troubleshooting York RTU Gas Ignition System Problems: Expert Solutions

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2020-11-29T08:06:00

## Word Count: 1354

## Categories: Troubleshooting, Heating Systems

## Tags: None

## Permalink: https://hvacknowitall.com/blog/troubleshooting-gas-fired-ignition-problems

## Description:
## Troubleshooting Complex Gas Ignition Systems

Looking for in-depth knowledge on burner repairs? The troubleshooting process described in this article is also covered in our detailed podcast episode below:

[![HVAC Know It All Podcast Episode on High Limit Switch and Spark Ignitor Troubleshooting](https://hvacknowitall.com/wp-content/uploads/2022/11/2225668_edit-2-1024x1024.jpg)](https://podcasters.spotify.com/pod/show/hvacknowitall/episodes/High-Limit-Switch-and-Spark-Ignitor-Troubleshooting-en7if5/a-a3kglre)

This real-world troubleshooting tip emerged from a challenging burner repair. During routine preventative maintenance, we discovered that a York Rooftop Unit (RTU) had a first-stage burner that intermittently failed to sense flame and engage the main fire.

### How Direct Spark Ignition Should Work

These RTUs use a direct spark ignition system that follows a specific sequence:

1. A spark is generated at the ignitor
2. The pilot valve within the gas valve opens
3. Gas flows across a pilot tube
4. The flame sensor (mounted at the opposite end of the tube) detects when the pilot flame reaches it
5. Flame rectification occurs, which “proves” the flame exists
6. The ignition control then signals the gas valve to engage the main fire

### What Is Flame Rectification?

Flame rectification is the process that allows the control board to confirm a flame is present. Think of it as an electrical bridge – the flame acts as a diode, allowing a small DC current to flow in only one direction between the sensor and ground. This creates a measurable microamp signal that the control board interprets as proof of flame.

To learn more about **flame rectification** and how to check flame signals, visit our [detailed article on the topic](https://hvacknowitall.com/blog/flame-rectification-how-to-check-a-flame-signal).

### Common Failure Points

In my experience, pilot tubes are a frequent source of problems. They can become:  
– Blocked with debris  
– Corroded internally  
– Damaged from heat exposure  
– Misaligned during previous service

When the pilot tube is compromised, proper gas distribution is restricted. If the flame sensor can’t detect a good flame, the main burner will never fire – a critical safeguard that prevents potentially dangerous operation.

### Critical Environment Considerations

This particular RTU wasn’t just heating any space – it was responsible for the northeast corner of a pharmaceutical warehouse. This critical environment is monitored with sensitive temperature sensors, and even minor temperature fluctuations could compromise stored products worth thousands or even millions of dollars.

![Flame Rectification Process](https://hvacknowitall.com/wp-content/uploads/2020/11/Flame-Rectification-1024x768.jpg)

When working on gas-fired ignition systems, safety must be your top priority. Always follow these critical procedures:

1. **Turn off all power sources** to the equipment before beginning work
2. **Shut off the gas supply** completely at the appropriate valve
3. **Test for gas leaks** using approved methods when work is complete
4. **Ensure proper ventilation** in the work area to prevent gas buildup
5. **Follow manufacturer specifications** for all replacement parts
6. **Reference ANSI Z21 standards** for gas appliance safety requirements
7. **Use proper personal protective equipment** including gloves and safety glasses
8. **Never bypass safety devices** except temporarily for diagnostic testing
9. **Verify proper operation** of all safety controls after repair

Remember, gas ignition systems incorporate multiple safety features for good reason. Improper repairs can lead to dangerous conditions including fire, explosion, or carbon monoxide exposure.

### Component Replacement Strategy

For this repair, I completely removed the burner assembly along with several critical components:  
– Pilot tube  
– Flame sensor  
– Spark ignitor  
– Rollout switch  
– Ignition module

My standard practice is to replace these components as a set. When a pilot tube requires replacement, the flame sensor and ignitor should always be replaced simultaneously. These components work as an integrated system, and replacing only one part often leads to callbacks.

### The Importance of Rollout Switches

I’ve learned through experience to always replace the rollout switch during any significant heating repair. Here’s why: rollout switches can develop internal faults that don’t appear during basic continuity testing with a multimeter. I’ve encountered numerous situations where:

1. The burner wouldn’t fire
2. The rollout switch tested fine with a meter
3. Temporarily bypassing the switch allowed the burner to fire
4. Installing a new switch permanently resolved the issue

This indicates that the switch can appear electrically functional while still causing intermittent problems.

### Preventative Replacement in Critical Environments

In this pharmaceutical warehouse application, I also replaced the ignition control module. While not obviously faulty, this represented inexpensive insurance against future failures in such a critical environment.

The consequences of a heating failure in this facility would be severe:  
– Product quarantine procedures  
– Quality assurance investigations  
– Regulatory documentation requirements  
– Possible loss of temperature-sensitive inventory

The cost of these replacement parts is minimal compared to the potential business impact of a system failure.

> [View this post on Instagram](https://www.instagram.com/p/CIHPxE8HNR7/?utm_source=ig_embed&utm_campaign=loading)
>
> [A post shared by Gary McCreadie HVAC/R Tech/Business Owner (@hvacknowitall1)](https://www.instagram.com/p/CIHPxE8HNR7/?utm_source=ig_embed&utm_campaign=loading)

### When the Fix Creates New Problems

After completing the initial repair and testing the system, I encountered a new issue: no spark generation. I traced this to a defect in the new spark ignitor – it had separated inside the heat shrink.

After installing a second new ignitor, I still observed problems. The spark seemed weaker than normal. This required more detailed investigation.

### Diagnostic Testing Process

I removed the ignitor assembly from the burner bracket to isolate the problem. Here’s my testing procedure:

1. Hold the ignitor with insulated pliers
2. Position the rod close to a ground source
3. Observe the spark strength and consistency

The initial test showed a strong spark in the standard position. However, when I slightly tilted the assembly, moving a corner toward ground, I observed a small, weak spark where there shouldn’t be any.

### Root Cause Analysis

This behavior indicated a fundamental problem: the ignition rod should be fully insulated in its ceramic case, with the spark only occurring at the designated point. The unwanted secondary spark meant that when mounted in the assembly, the spark energy was dissipating rather than concentrating at the correct location.

### Innovative Solution

As a field test, I used electrical tape to fully insulate the ignitor bracket. After reinstallation, the spark immediately sounded stronger, and both the pilot and main burner fired consistently on every attempt.

This troubleshooting process demonstrates how even brand new replacement parts can have defects, and why thorough testing is essential in critical applications.

You can watch the entire repair process in the video below.

Facing complex HVAC repairs in critical environments? Elevate your business with Property.com. Our exclusive network connects you with premium opportunities and provides tools like ‘[Know Before You Go](https://mccreadie.property.com)’ for homeowner insights (permit history, home value). Boost your credibility with Property.com certification and enhanced SEO. Limited spots available per region secure your advantage today.

## Expand Your HVAC Troubleshooting Knowledge

This York RTU ignition system repair highlights several critical lessons for HVAC professionals:

1. Always inspect and test the entire ignition system as an integrated unit
2. Replace companion components when servicing gas ignition systems
3. Consider the operating environment when making repair decisions
4. Test new components thoroughly before considering a job complete
5. Think creatively when standard solutions don’t resolve the issue

For more detailed HVAC troubleshooting insights and technical discussions, tune into our [podcast](https://hvacknowitall.com/podcasts). We regularly cover complex repair scenarios and share field-tested solutions from our decades of experience.

Looking to expand your knowledge base? Explore our comprehensive collection of [technical blog articles](https://hvacknowitall.com/blog) for expert tips and the latest industry updates. Stay informed and ahead of the curve with HVAC Know It All!

},
"datePublished": "",
"image": "https://hvacknowitall.com/wp-content/uploads/2020/11/Flame-Rectification-1024x768.jpg",
"articleSection": "HVAC Repair",
"keywords": "York RTU, direct spark ignition, flame rectification, pilot tube, gas ignition troubleshooting, HVAC repair",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/troubleshooting-gas-fired-ignition-problems"

--------------------------------------------------

# ID: 316

## Title: Installing Service Valves on Self-Contained Reach-In Coolers and Freezers: Step-by-Step Guide

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2020-11-12T15:54:00

## Word Count: 1054

## Categories: Refrigeration, Components

## Tags: None

## Permalink: https://hvacknowitall.com/blog/installing-service-valves-for-self-contained-reach-in-coolers-and-freezers

## Description:
## Introduction to Service Valves in Reach-In Coolers and Freezers

Many small, self-contained reach-in coolers and freezers lack service access valves that would otherwise facilitate system testing, evacuation, and refrigerant recovery. While this design choice creates challenges during troubleshooting and maintenance, it serves an important purpose: fewer potential leak points means greater system integrity over time. Nevertheless, when a refrigeration technician encounters performance issues with these systems, having a reliable method to gain system access becomes essential for proper diagnosis and repair.

When you encounter a commercial refrigeration appliance that’s failing to maintain proper temperature, the root cause may involve refrigerant issues such as leaks, restrictions, or incorrect charge levels. Without service ports to connect gauges or recovery equipment, your diagnostic capabilities are severely limited. In these situations, you’ll need to safely add access fittings to properly assess and service the system.

Working smarter means having the right information. Property.com Pros gain an edge with our exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool, revealing homeowner details like permit history and potential upgrade savings *before* the service call. Elevate your credibility with Property.com certification and join a premium network with limited spots per trade. Secure your exclusive advantage today.

[Yellow Jacket](https://yellowjacket.com/product/refrigerant-recovery-pliers/) manufactures specialized refrigerant recovery pliers that provide temporary access to sealed refrigeration systems. These innovative pliers feature a precision piercing needle with a rubber seat on one jaw and a 1/4” service valve on the opposing side, creating an instant service port without permanent system modification.

To use this tool effectively:

1. Select an appropriate location on the system piping for access
2. Adjust the pinch depth on the pliers according to the pipe diameter
3. Position the pliers perpendicular to the pipe with the needle aligned with your target point
4. Firmly grip the pliers to pierce the line and create a sealed connection
5. Connect your gauge set or recovery equipment to the integrated service valve

For complete system assessment, use two sets of pliersone on the high-pressure side and another on the low-pressure side. After diagnosing the issue, you must **[recover the refrigerant](https://www.hvacknowitall.com/blogs/blog/187768-refrigerant-recovery)** before installing permanent access valves.

![Refrigerant Recovery Pliers](https://hvacknowitall.com/wp-content/uploads/2020/11/Refrigerant-Recovery-Pliers.webp)

Before proceeding with any refrigerant-related procedures, remember that EPA regulations require proper certification for handling refrigerants. Always observe these critical safety protocols:

- Wear appropriate personal protective equipment, including safety glasses and gloves
- Work in well-ventilated areas to prevent refrigerant gas accumulation
- Use only tools and equipment rated for the pressures and refrigerant types in the system
- Never release refrigerant into the atmosphererecovery is mandatory and legally required
- Be aware that liquid refrigerant can cause frostbite on contact with skin
- Keep recovery cylinders within their weight limits and certification dates

Failure to follow proper procedures can result in injury, equipment damage, and potential legal penalties. Always adhere to local regulations and industry best practices when handling refrigerants.

For small self-contained refrigeration units that typically contain only a few ounces of refrigerant, a simplified recovery process is often sufficient without requiring a full recovery machine setup. Here’s a streamlined method:

1. Prepare an empty, approved recovery cylinder rated for the specific refrigerant type
2. Connect a vacuum-rated hose between the cylinder and a vacuum pump
3. Evacuate the recovery cylinder to a deep vacuum (below 500 microns ideally)
4. Use a micron gauge on the tank to verify the vacuum level
5. Once evacuated, close the cylinder valve and disconnect from the vacuum pump
6. Connect the evacuated cylinder to the system via the temporary access valve
7. Open the cylinder valve carefully

The substantial pressure differential between the evacuated tank and the pressurized system will typically pull the entire refrigerant charge into the recovery cylinder without additional equipment. This passive recovery method works effectively for most small systems while maintaining compliance with EPA refrigerant handling requirements.

![Refrigerant Recovery](https://hvacknowitall.com/wp-content/uploads/2020/11/Refrigerant-Recovery.webp)

After recovering the refrigerant, you’ll need to install permanent service valves to facilitate future maintenance. This process involves:

1. Selecting appropriately sized Schrader-type access valves compatible with the system
2. Identifying optimal installation points on both high and low pressure lines
3. Cutting the lines at the selected points using a tube cutter
4. Installing the service valves using proper brazing or soldering techniques
5. Ensuring leak-free connections with electronic leak detection or bubble testing
6. Evacuating the system to remove moisture and non-condensables
7. Recharging the system with the proper refrigerant type and quantity

Permanent access valves will simplify future diagnostics, refrigerant recovery, and system evacuation procedures, saving significant time during subsequent service calls.

## Conclusion

Properly installing service valves in self-contained reach-in coolers and freezers transforms challenging service situations into straightforward maintenance procedures. By understanding how to gain temporary access with specialized tools and then installing permanent service ports, HVAC technicians can effectively diagnose, recover refrigerant, and service these systems while maintaining regulatory compliance. These techniques ensure your commercial refrigeration equipment remains serviceable throughout its operational life.

If you found this technical guide valuable, be sure to check out the **[HVAC Know It All Podcast](https://hvacknowitall.com/podcasts)** for more expert tips, industry insights, and in-depth discussions on all things HVAC and refrigeration. Tune in now to continue building your technical knowledge and troubleshooting skills!

],
"step": [
],
"estimatedCost": {
"@type": "MonetaryAmount",
"currency": "USD",
"value": "50-100"

--------------------------------------------------

# ID: 111

## Title: Advanced HVAC Evacuation Techniques: The Science of Effective Pull Down

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2020-11-07T13:16:00

## Word Count: 2023

## Categories: Air Conditioning

## Tags: None

## Permalink: https://hvacknowitall.com/blog/the-science-of-evacuation-and-on-site-pull-down

## Description:
## Advanced HVAC Evacuation Techniques: The Science of Effective Pull Down

The evacuation process is critical in HVAC maintenance and installation, removing air, moisture, and contaminants that can compromise system performance and longevity. Over the years, evacuation methods have evolved significantly, driven by changes in refrigerants, oils, and equipment technology.

While basic evacuation principles remain constant, achieving efficient and effective resultsparticularly on larger commercial systemsrequires specialized knowledge and techniques. This article examines the science behind AC evacuation and shares real-world strategies from a challenging compressor replacement on a McQuay air-cooled chiller.

![Three compressors on McQuay air-cooled chiller](https://hvacknowitall.com/wp-content/uploads/2023/04/3-compressors-on-McQuay-air-cooled-chiller.webp)

The approach to removing contaminants from refrigeration systems has transformed dramatically over decades. Historically, technicians would purge refrigerant through systems to flush out air, moisture, and other unwanted elementsa practice now recognized as environmentally harmful and inefficient.

The introduction of POE (Polyolester) oil has significantly changed evacuation requirements. Unlike traditional mineral oil, POE is hygroscopic, meaning it actively absorbs moisture from the air. This property creates additional challenges, as systems with POE require more thorough evacuation to remove all moisture that may have been absorbed by the oil.

Today’s advanced evacuation techniques focus on creating deep vacuums efficiently while minimizing environmental impact and maximizing system performance.

Our case study involves a failed compressor in a trio configuration (three compressors piped in parallel on a single circuit) on a McQuay air-cooled chiller. The R22 system contained a mixture of mineral oil and POE oil, with POE introduced from a previous compressor replacement.

After installing the new compressor, which came pre-charged with POE oil, we performed a nitrogen pressure test that successfully held pressure over a 24-hour period, confirming the system’s mechanical integrity.

At this stage, a thorough [evacuation](https://hvacknowitall.com/blog/evacuation-procedure) was essential to remove air, moisture, and other contaminants before recharging with refrigerant. The mixed oil situation added complexity, as POE’s moisture-absorption properties required extra attention to moisture removal.

Standard evacuation setups using manifold gauges and standard charging hoses create significant restrictions that slow down the process. To achieve faster, more effective evacuation, consider these equipment upgrades:

### Eliminate Restrictions

Many technicians rely on manifold gauges for evacuation, but this introduces multiple potential leak points and flow restrictions. The small diameter of standard 1/4” charging hoses severely limits evacuation speed.

### Large-Diameter Hoses

Using vacuum-rated hoses with larger diameters dramatically improves evacuation efficiency. Common options include:  
– 3/8” vacuum hoses  
– 1/2” vacuum hoses  
– 3/4” TruBlu hoses (from Accutools)

The larger the diameter, the faster the evacuation, as demonstrated in this comparison video:

### Schrader Core Removal

Removing Schrader valve cores eliminates another significant restriction point. Core removal tools include a stem for removing the core, a ball valve for system isolation, and sometimes an auxiliary tee for additional connections.

The isolation valve serves multiple purposes:  
– Allows decay/rise testing without disconnecting from the vacuum pump  
– Enables core removal and installation under system pressure  
– Permits isolation of sections during troubleshooting

This video demonstrates a Schrader core removal tool in action:

### Direct Pump Connection

Connect vacuum-rated hoses directly from the system to your vacuum pump, bypassing manifold gauges entirely. Most modern vacuum pumps feature multiple port sizes to accommodate different diameter hoses.

### Micron Gauge Placement

Position your micron gauge on the system side (not the pump side) to accurately monitor evacuation progress. Keep the gauge upright to prevent system contaminants from entering the sensitive instrument.

After completing the pressure test, follow these steps for an effective evacuation:

1. **Verify vacuum pump condition** – Ensure your vacuum pump oil is fresh and uncontaminated. Change the oil if necessary. Perform an ultimate vacuum test by connecting your micron gauge directly to the pump and confirming it reaches the nameplate vacuum rating.
2. **Install core removal tools** – Attach core removal assemblies to system access ports and remove the Schrader valve cores.
3. **Connect evacuation hoses** – Attach large-diameter vacuum-rated hoses between the core removal tools and vacuum pump ports.
4. **Position micron gauge** – Install a micron gauge on the system side, not the pump side, to accurately monitor evacuation progress. Keep the gauge upright to prevent contamination.
5. **Start evacuation** – Turn on the vacuum pump and open the ball valves on the core removal tools.
6. **Monitor progress** – Track the micron level as it decreases. The target is typically 500 microns or below, though many experts now recommend even lower levels for optimal system performance.
7. **Perform decay test** – Once you reach your target vacuum level, close the ball valves on the core tools and monitor for pressure rise on the micron gauge:
8. A rapid rise indicates a system leak
9. A slow, gradual rise that eventually flattens suggests moisture or other contaminants still present in the system, requiring further evacuation
10. **Begin charging** – After a successful decay test, introduce refrigerant to create slight positive pressure in the system.
11. **Remove evacuation setup** – Detach the micron gauge, reinstall Schrader cores using the core removal tools, and disconnect the evacuation equipment.
12. **Complete the charging process** – Add the remaining refrigerant charge according to system specifications.

Field conditions often present complications that require adaptations to standard evacuation procedures. Returning to our McQuay chiller case study, we encountered several challenges that extended the evacuation process.

### Initial Evacuation Attempt

Despite using the optimized setup described above, after 20 hours of continuous evacuation, the system had only reached just under 1000 micronsstill above our target threshold of 500 microns.

### Cold Weather Complications

A significant factor in this slow progress was the overnight ambient temperature dropping below freezing. Cold conditions can dramatically slow evacuation as:  
– Moisture inside the system can freeze into ice droplets  
– Frozen moisture must undergo sublimation (changing directly from solid to gas)  
– The sublimation process is slower than normal evaporation

### Adaptive Strategy

To overcome these challenges, we implemented a three-part solution:

1. **Nitrogen sweeping** – We performed a nitrogen sweep, purging the system with dry nitrogen to help dislodge moisture and contaminants.
2. **Fresh vacuum pump oil** – We changed the vacuum pump oil to ensure maximum efficiency in moisture removal.
3. **System heating** – We activated both the receiver and evaporator bundle heaters to raise internal system temperatures, which helps:
4. Prevent moisture freezing
5. Accelerate vaporization of existing moisture
6. Improve overall evacuation efficiency

After implementing these adjustments, we restarted the evacuation process. The system reached 2000 microns, at which point we performed two additional nitrogen sweeps for thorough contaminant removal.

### Extended Evacuation

The vacuum pump ran for an additional 48 hours with the heaters operating. Upon returning to the site, we found the system had achieved 335 micronswell below our target threshold and indicating a successful evacuation.

For a detailed walkthrough of this challenging evacuation process, watch this video:

Tackling complex jobs like chiller evacuations requires the right tools and intelligence. Property.com equips elite contractors with exclusive advantages, including the ‘[Know Before You Go](https://mccreadie.property.com)’ tool providing homeowner permit history and property details before you arrive. Elevate your business with Property.com certification, enhanced SEO, and access to a premium network. Limited spots available per trade/region. Secure your exclusive status today.

System requirements vary significantly based on refrigerant types and oil combinations. Understanding these differences improves evacuation efficiency and system performance.

### R22 Systems with Mixed Oils

As in our case study, systems originally designed for R22 with mineral oil that later received POE oil present unique challenges:  
– Mineral oil and POE oil mixtures can trap moisture differently than either oil alone  
– These systems may require longer evacuation times and multiple nitrogen sweeps  
– Higher vacuum levels (lower micron readings) are often necessary

### HFC/HFO Systems with POE Oil

Modern systems using HFC refrigerants (R410A, R407C) or HFO refrigerants (R1234yf, R1234ze) exclusively use POE oil, which:  
– Requires thorough evacuation due to POE’s hygroscopic properties  
– May benefit from vacuum levels below 250 microns for optimal moisture removal  
– Should receive extra attention during humid conditions when the system has been open

### Critical Charge Systems

Small systems with critical refrigerant charges (like residential mini-splits) demand:  
– Extremely thorough evacuation (often below 200 microns)  
– Triple evacuation techniques for better results  
– Particular attention to connection quality and tool calibration

Your vacuum pump’s condition directly affects evacuation efficiency. Beyond regular oil changes, comprehensive maintenance includes:

### Seals and Gaskets

- Inspect rubber seals and gaskets regularly for cracks or deterioration
- Replace damaged seals immediately to maintain proper vacuum levels
- Apply vacuum pump oil to gaskets before reassembly to ensure proper sealing

### Gas Ballast Function

- Understand your pump’s gas ballast valve functionit helps expel moisture during operation
- Open the gas ballast when evacuating systems with high moisture content
- Close the ballast toward the end of evacuation to reach ultimate vacuum levels

### Motor and Mechanical Components

- Listen for unusual noises indicating bearing wear or motor issues
- Check belt tension on belt-driven models
- Ensure cooling fins remain clean for proper thermal management

### Storage Practices

- Seal all pump openings when not in use to prevent contamination
- Store pumps in clean, dry environments
- Run the pump briefly before storage with the gas ballast open to remove moisture

## Summary and Best Practices

Effective evacuation is both science and art, requiring proper equipment, technique, and adaptation to field conditions. While smaller, newer systems typically evacuate quickly, larger and older systemsespecially those with mixed oils or complex pipingdemand greater patience and attention.

The keys to successful evacuation include:

- Eliminating restrictions with large-diameter hoses and removing Schrader cores
- Properly positioning micron gauges to accurately monitor system conditions
- Performing decay tests to verify system integrity and cleanliness
- Adapting techniques for challenging conditions like cold weather
- Understanding the specific requirements of different refrigerant and oil combinations
- Maintaining vacuum equipment in optimal condition

For especially challenging systems, techniques like nitrogen sweeping and applying controlled heat can dramatically improve results, though these measures aren’t necessary for routine evacuations of well-maintained systems.

Remember to remove your micron gauge before introducing significant refrigerant pressure to prevent damage to this sensitive instrument.

For more technical tips, demonstrations, and troubleshooting guidance, visit [The HVAC Know It All YouTube channel](https://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber) or listen to [The HVAC Know It All podcast](https://hvacknowitall.com/podcasts) on your favorite podcast platform.

],
"step": [
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/alternative-refrigerants-for-the-hvac-industry"
},
"about": [
]

],
"keywords": [
"converged systems",
"HVAC",
"mini-split",
"heat pump",
"Carrier",
"Daikin",
"interface kit",
"energy efficiency"
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"url": "https://hvacknowitall.com/stop-turning-wrenches-grow-business"
},
"about": [
],
"mentions": [
]

},
"video": [
],
"about": {
"@type": "Thing",
"name": "HVAC Repair"
},
"articleSection": "Troubleshooting",
"keywords": "Carrier RTU, transformer troubleshooting, HVAC repair, high voltage transformer, 575V transformer, commercial HVAC, rooftop unit"

--------------------------------------------------

# ID: 529

## Title: TESTO 440 AIR FLOW &#038; IAQ KIT: Complete Professional HVAC Testing Solution Review

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2019-12-29T12:09:00

## Word Count: 1044

## Categories: None

## Tags: None

## Permalink: https://hvacknowitall.com/blog/trutech-tools-testo-440-air-flow-testing

## Description:
In early 2018, Testo introduced their comprehensive 440 air flow testing and measurement kit, a professional solution designed to streamline HVAC diagnostics and air quality assessment. This versatile system stands out with its fully Bluetooth-enabled probe options, eliminating cable clutter and enhancing mobility during testing. The intelligent design features interchangeable probe attachments that work with both cable and Bluetooth handles, offering technicians exceptional flexibility while reducing equipment bulk and storage requirements. Testo’s quick-release system makes swapping between probe types remarkably fast and intuitive, significantly reducing setup time between different measurement tasks.

## [RECEIVE PREFERRED TESTO PRICING AT TRU TECH TOOLS](https://docs.google.com/forms/d/e/1FAIpQLSeOC8oQB97trj6XKDWRylM2ILFlnVjYG1GnTT2lRWT8-K4weQ/viewform)

The Testo 440 combines advanced measurement technology with user-friendly operation, making it suitable for both routine HVAC maintenance and specialized air quality assessment. The system’s modular design centers around a handheld unit that processes and displays readings from various probe attachments.

Key advantages include:

- Bluetooth connectivity across the probe lineup for wireless operation
- Universal handle compatibility with all probe attachments
- Quick-connect system for rapid probe changes
- Clear, intuitive interface with guided measurement menus
- Compact design for improved portability and storage

![](https://d14ty28lkqz1hw.cloudfront.net/data/org/15112/media/img/source/edit/1689680_edit.jpg)

The Testo 440 offers comprehensive testing capabilities that comply with industry standards. In accordance with EN ISO 7730 and ASHRAE 55, the unit features specialized menus for:

- Volume flow measurement
- Degree of turbulence assessment
- K factor calculations
- Heating and cooling output evaluation
- Mold risk detection

These capabilities allow technicians to perform standards-compliant testing efficiently. The full menu overview is available in [this detailed PDF](https://static-int.testo.com/media/4f/6b/b1a9bd9b099b/testo-440-Menue-Overview-EN.pdf), which provides a complete breakdown of the system’s measurement capabilities and testing protocols.

The Testo 440 supports an extensive range of probe options to address virtually any air measurement need. The [complete probe lineup](https://static-int.testo.com/media/de/06/5de12109af18/testo-440-Inlay-EN.pdf) includes specialized attachments for various applications, from standard vane anemometers to sophisticated IAQ assessment tools.

### Mold Detection Capabilities

One standout feature is the mold detection menu, which provides HVAC contractors with a competitive edge in the growing indoor air quality market. By offering professional mold risk assessment, contractors can expand their service offerings beyond traditional HVAC work. This capability helps identify potential problem areas before visible mold appears, allowing for preventative measures that can save property owners significant remediation costs.

Leverage advanced tools like the Testo 440 to stand out? Elevate your HVAC business further with Property.com. Gain exclusive access to homeowner insights with our ‘[Know Before You Go](https://mccreadie.property.com)’ tool, boost your SEO with a premium subdomain, and manage your reputation effortlessly. Limited spots available per region. Become a certified Property.com Pro and secure early adopter benefits today.

### CO2 Monitoring

The 323 Air Quality Probe expands the system’s capabilities to include carbon dioxide (CO2) measurement, an often overlooked but critical IAQ parameter. Elevated CO2 levels (1000ppm and above) can cause occupant discomfort including fatigue, headaches, and reduced concentration. More information about CO2’s impact on indoor air quality can be found in my [HVAC Tip article on IAQ and carbon dioxide](https://www.hvacknowitall.com/blogs/blog/225210-hvac-tip---iaq-and-carbon-dioxide).

For HVAC professionals, the Testo 440 represents more than just a measurement toolit’s a potential business differentiator. By offering specialized services like:

- Comprehensive air balancing for improved comfort
- Mold risk assessment for health-conscious clients
- Advanced IAQ testing including CO2 monitoring
- Standards-compliant HVAC system evaluation

Contractors can establish themselves as air quality experts, potentially commanding premium rates for specialized assessment services. The system’s professional appearance and precise measurements also help build client confidence and trust.

The Testo 440 is particularly valuable for:

- HVAC commissioning specialists who need accurate air balancing capabilities
- IAQ consultants requiring comprehensive air quality assessment tools
- Mechanical contractors handling diverse HVAC installation projects
- Service technicians diagnosing complex comfort issues
- Building performance analysts evaluating HVAC system efficiency

While the system represents a significant investment, professionals who regularly perform air diagnostics will find the time savings and expanded capabilities justify the cost.

**Q: Can I use my existing Testo probes with the 440 system?**  
A: The 440 uses a new connector system, so older Testo probes are not directly compatible without adapters.

**Q: How long do the Bluetooth probes operate on a battery charge?**  
A: Most Bluetooth probes provide 8-10 hours of continuous operation on a full charge.

**Q: Can multiple measurements be logged simultaneously?**  
A: Yes, the 440 can record multiple parameters simultaneously when using the appropriate probes.

**Q: Is the system suitable for duct leakage testing?**  
A: While excellent for air flow measurement, specific duct leakage testing requires additional equipment or Testo’s specialized duct testing systems.

The Testo 440 represents a significant advancement in portable air flow and IAQ testing technology. Its modular design, Bluetooth connectivity, and comprehensive measurement capabilities make it a valuable addition to any HVAC professional’s toolkit. Whether performing basic air balance procedures or advanced indoor air quality assessments, the system delivers professional-grade results with remarkable efficiency.

Check out the link to my [YouTube](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber) channel for more tips, tricks, and troubleshooting videos and check out the The HVAC Know It All podcast [here](http://anchor.fm/hvacknowitall) or on your favourite podcast app. Also visit [Trutechtools.com](https://www.trutechtools.com/) to save 8% off your purchase using promo code “knowitall” at check out. Happy HVACing…

--------------------------------------------------

# ID: 95

## Title: Adaptive vs Fixed Expansion Valves: HVAC Metering Device Guide

## Type: blog_post

## Author: Jamie Kitchen

## Publish Date: 2019-12-20T12:47:00

## Word Count: 1934

## Categories: Components, Air Conditioning

## Tags: None

## Permalink: https://hvacknowitall.com/blog/adaptive-vs-fixed-expansion-valves

## Description:
## Understanding Expansion Valves in HVAC Systems

Expansion valves are critical metering devices in refrigeration and air conditioning systems, designed to precisely inject refrigerant into the evaporator at conditions that enable optimal heat absorption. These components create the pressure drop necessary to convert high-pressure liquid refrigerant to a lower-pressure, lower-temperature mixture that can effectively absorb heat in the evaporator.

Professional HVAC technicians know that proper expansion valve selection and operation significantly impacts system efficiency, capacity, and compressor longevity. These valves are sized to match the calculated load on the system evaporator under standardized conditions, ensuring balanced system performance.

While the HVAC industry uses various expansion valve designsfrom simple orifices and manual hand valves to sophisticated electronic variantsthey all fall into two fundamental categories: fixed and adaptive. Understanding the differences between these categories is essential for proper system design, installation, and troubleshooting.

Fixed orifice expansion valves are simple devices with a non-adjustable opening that cannot actively adapt refrigerant flow to match changing evaporator heat loads. While the amount of refrigerant they inject does vary with pressure differential, this variation isn’t purposefully aligned with changing heat loads.

The most common fixed orifice devices include pistons and capillary tubes. Pistons are essentially precision-drilled metal inserts held in a distributor attached to the evaporator inlet. **Image 1** shows a piston (B) and its accompanying distributor. The orifice size and pressure differential across the piston determine refrigerant flow volume.

![fixed expansion valve breakdown](https://hvacknowitall.com/wp-content/uploads/2019/12/fixed-expansion-valve-breakdown.webp)

When sizing fixed expansion devices, manufacturers use “standard conditions”predetermined values for evaporator and condensing pressures, superheat, and subcooling. For example, ARI A/C CT 130F specifies a 45F evaporator temperature, 130F condensing temperature, 20F useful superheat, and 15F subcooling. These standardized conditions allow manufacturers to match components based on capacity for proper system integration.

Since the pressure differential between condensing and evaporator pressures governs flow through a piston orifice, changing conditions directly impact refrigerant flow. This explains why evaporator superheat values vary with outdoor temperatures. On charging charts for piston-equipped air conditioning systems, you’ll notice that superheat target values increase as outdoor temperatures decrease.

During hot, low-humidity days, evaporator superheat can drop to single digits. Coupled with a dirty condenser or poor airflow, this condition can lead to compressor flooding. Conversely, on cooler, rainy days, higher superheat may result in inadequate dehumidification.

### Common Fixed Expansion Valve Issues

Fixed expansion valves typically experience these failure modes:

1. **Clogging or Restriction**: Debris, oil, or contaminants can partially or completely block the piston or capillary tube, restricting refrigerant flow and causing high superheat, reduced capacity, and poor cooling.
2. **Sizing Issues**: An incorrectly sized fixed orifice can’t be adjusted in the field. Oversized pistons or shorter-than-specified capillary tubes lead to evaporator flooding and compressor damage, while undersized components cause starved evaporators and efficiency loss.
3. **System Mismatch**: Fixed expansion devices perform optimally only within a narrow range of operating conditions. When ambient temperatures or loads deviate significantly from design parameters, system performance suffers noticeably.
4. **Dislodged Pistons**: Improper installation or pressure surges can dislodge piston orifices from their seats, causing erratic refrigerant flow and unpredictable superheat readings.

Capillary tubeslong, narrow-diameter tubingoffer minimal adaptability to condenser pressure changes. In systems with critical charge, increasing condensing pressure reduces subcooling, causing refrigerant to flash to vapor earlier in the capillary tube. Since vapor occupies more volume than liquid, this phenomenon restricts flow through the tube. Nevertheless, capillary tubes still perform best with stable high and low-side pressures.

Proper capillary tube sizing involves selecting the recommended diameter and precisely cutting it to the specified length based on the calculated load. Incorrect sizing invariably leads to improper refrigerant flow and system performance issues.

Listen to Jamie Kitchen and Gary McCreadie discuss superheat as it pertains to adaptive vs. fixed metering devices and subscribe to the [HVAC Know It All Podcast.](https://anchor.fm/hvacknowitall)

Unlike fixed metering devices, adaptive expansion valves actively respond to changing evaporator loads by modulating refrigerant flow. This dynamic adjustment capability makes them ideal for applications with variable load conditions or wide ambient temperature ranges.

The most common adaptive valve is the thermal expansion valve (TXV). This mechanical device uses pressure signals from a sensing bulb at the evaporator outlet and from the evaporator itself to regulate refrigerant flow. As shown in **Image 2**, these pressure signals create opposing forces across a diaphragm in the TXV’s power element.

The key forces at work in a TXV include:  
– **Opening Force**: Pressure from the sensing bulb applied to the top of the diaphragm  
– **Closing Forces**: Evaporator pressure and superheat spring pressure applied to the bottom of the diaphragm

![TXV Diagram](https://hvacknowitall.com/wp-content/uploads/2019/12/TXV-Diagram.webp)

#### How TXVs Respond to Changing Loads

When evaporator load increases, refrigerant boils off sooner in the evaporator circuit, resulting in higher superheat at the outlet. This heats the sensing bulb, increasing its pressure. This pressure transmits through the connecting capillary tube to the TXV power head and onto the diaphragm’s upper surface.

As this opening force overcomes the combined closing forces of the evaporator pressure and superheat spring, the valve opens wider. The resulting increase in refrigerant flow reduces outlet superheat, creating a self-regulating feedback system.

The superheat spring ensures a minimum superheat level to protect the compressor from liquid flood-back. Adjusting the superheat setting changes the spring force applied. However, technicians should avoid adjusting TXV superheat settings until ruling out other potential issues, as improper adjustments can complicate straightforward repairs.

For multi-circuit evaporators, distributors (see **Image 1**) create significant pressure drops between the TXV outlet and evaporator outlet. To compensate, these applications require external equalized TXVs, which sample pressure from the evaporator outlet after all pressure drops have occurred. This pressure feeds to the underside of the TXV diaphragm through a connection tube (see **Image 3**).

Without external equalization, the temperature equivalent of the pressure drop would be added to the required superheat, causing the TXV to underfeed the evaporator. While you can use an external equalized TXV when unnecessary, never use an internal equalized TXV when external equalization is required.

![external equalized TXV](https://hvacknowitall.com/wp-content/uploads/2019/12/external-equalized-TXV.webp)

### TXV Troubleshooting Guide

When diagnosing TXV issues, monitor these key indicators:

1. **High Superheat, Low Suction Pressure**: Typically indicates a restricted or underfeeding TXV. Check for:
2. Plugged inlet screen
3. Moisture or contaminants in the valve
4. Loss of sensing bulb charge
5. Incorrectly mounted sensing bulb
6. Improperly adjusted superheat setting
7. **Low Superheat, High Suction Pressure**: Suggests an overfeeding TXV. Inspect for:
8. Sensing bulb improperly located or insulated
9. Damaged power head
10. Debris preventing valve from closing
11. Incorrectly adjusted superheat setting
12. **Hunting (Oscillating Superheat)**: Points to an unstable TXV operation. Examine:
13. System refrigerant charge
14. TXV oversizing
15. Poor sensing bulb contact or location
16. Excessive pressure drop across the distributor

Electronic expansion valves (EEVs) represent the most sophisticated metering device technology, combining a valve body with a motor or solenoid and a programmable controller. These systems use pressure and temperature sensors to calculate evaporator saturation temperature and superheat, then precisely adjust valve position accordingly.

EEVs offer unprecedented flexibility across applications from low-temperature freezers to comfort cooling. While many EEVs maintain a fixed superheat value optimized for specific operating conditions, advanced models continuously minimize superheat while maintaining stability, maximizing energy efficiency (see **Image 4**).

![external equalized TXV](https://hvacknowitall.com/wp-content/uploads/2019/12/external-equalized-TXV.webp)

EEVs come in two primary designs:

1. **Stepper Motor Valves**: These valves use incremental motor steps to precisely position the valve opening. The stepper motor rotates in calculated incrementsclockwise to close and counterclockwise to openbased on controller signals. Technicians can program opening/closing speeds and set minimum/maximum opening ranges for optimized performance. (**Image 5**)
2. **Pulse Width Modulated (PWM) Valves**: These robust solenoid valves operate either fully open or fully closed. The controller rapidly cycles the valve, with the ratio of open-to-closed time determining effective refrigerant flow. While offering excellent oil return, PWM valves should be installed away from other line components to prevent liquid hammer phenomena.

![Stepper Motor EEV](https://hvacknowitall.com/wp-content/uploads/2019/12/Stepper-Motor-EEV.webp)

### Energy Efficiency Comparison: TXV vs. EEV

The primary efficiency advantage of EEVs over TXVs lies in their ability to maintain lower stable superheat values:

- **TXVs** typically maintain 8-12F superheat for stable operation
- **EEVs** can safely operate with 5-8F superheat

This 3-7F reduction in superheat translates to approximately 2-5% improvement in system efficiency because:

1. Lower superheat means more effective evaporator surface area dedicated to the boiling process instead of superheating vapor
2. Higher suction gas density entering the compressor improves compression efficiency
3. More precise control during part-load conditions minimizes compressor cycling

For a typical commercial refrigeration system, this efficiency gain can reduce annual energy consumption by 400-700 kWh per compressor horsepowersignificant savings that often justify the higher initial cost of EEV technology.

Diagnosing expansion valve issues requires precision. What if you had homeowner insights *before* you arrived? Property.com offers exclusive members access to the ‘[Know Before You Go](https://mccreadie.property.com)’ tool, providing permit history, home value, and potential upgrade savings. Elevate your service calls and stand out with Property.com certification. Limited spots available per region secure your advantage today.

## Conclusion

Fixed metering devices excel in consistent operating conditions where evaporator loads remain relatively stable. Their simplicity makes them cost-effective for many applications, but they require careful selection to prevent compressor flooding or evaporator starvation when conditions vary.

Adaptive metering devices offer superior flexibility by dynamically matching refrigerant flow to changing loads and ambient conditions. TXVs provide excellent control, throttling down to 50% of rated capacity while capable of delivering up to 30% above rated capacity when needed. EEVs take this adaptability further, controlling loads down to 20% of rated capacity or less while offering greater energy efficiency through precise superheat management.

The selection between fixed and adaptive expansion valves should consider application requirements, operating condition variability, efficiency goals, and budget constraints. For systems experiencing wide load fluctuations or operating in variable ambient conditions, the performance benefits of adaptive valves typically justify their higher initial cost through improved efficiency, reliability, and compressor protection.

## Learn More with HVAC Knowitall

Elevate your HVAC expertise and outshine your peers by delving into our informative [blog articles](https://hvacknowitall.com/blog), listening to our [industry-specific podcast](https://hvacknowitall.com/podcasts), and subscribe to our [YouTube channel](https://www.youtube.com/@HVACKnowItAll), where we share valuable insights tailored specifically for HVAC technicians seeking to enhance their business and provide exceptional service.

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/adaptive-vs-fixed-expansion-valves"
},
"datePublished": "2023-09-26",
"dateModified": "2023-09-26",
"image": {
"@type": "ImageObject",
"url": "https://hvacknowitall.com/wp-content/uploads/2019/12/TXV-Diagram.webp",
"width": "800",
"height": "600"
},
"keywords": "expansion valve, HVAC, TXV, EEV, metering device, superheat, subcooling, refrigeration",
"specialty": "HVAC Systems",
"about": [
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/hvac-solenoid-valve-sizing"
},
"articleSection": "HVAC Components",
"keywords": "HVAC, solenoid valve, valve sizing, refrigeration, air conditioning, Sporlan"

],
"tool": [
]

]

--------------------------------------------------

# ID: 29

## Title: Make Up Air Units: Function, Maintenance &#038; Efficiency Guide

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2019-02-17T15:33:00

## Word Count: 1443

## Categories: None

## Tags: None

## Permalink: https://hvacknowitall.com/blog/make-up-air-units-explained

## Description:
## **Understanding Make Up Air Units in Building Systems**

Make-up air units (MUAs) are essential components in modern building ventilation systems, particularly in multi-residential buildings like condominiums. Typically located at the top of buildingseither in mechanical rooms or on rooftopsthese systems serve a critical function that’s reflected in their name: they “make up” or replace air that’s exhausted from the building.

When kitchen hoods, bathroom fans, and dryer vents remove air from a building, MUA units work to replenish this air, maintaining proper airflow balance throughout the structure. Without adequate make-up air, buildings can experience numerous issues affecting comfort, air quality, and even structural integrity.

The building ventilation and the MUA system must work together to maintain proper building pressure. If there is too much MUA, noise complaints can become common. On the other hand, too little MUA can lead to complaints about smells in the hallways.

The MUA system is essential for pressurizing hallways, which helps to keep odors, such as cooking smells, localized to individual suites. This prevents the spread of odors and ensures a more comfortable living environment for all residents.

One aspect often overlooked with MUA systems is the [air balancing process](https://hvacknowitall.com/blog/hvac-air-balancing-procedure). Over the years, it’s not uncommon for tenants to adjust hallway diffusers, which can negatively impact the overall system. The system should be checked and rebalanced regularly to ensure that each floor receives the proper amount of air.

Airflow is measured in Cubic Feet per Minute (CFM). The total CFM of the MUA system is recorded and compared to the nameplate rating. Balancing and adjusting every hallway grill on each floor is carried out and recorded to ensure the proper airflow is delivered throughout the building.

Most MUA systems are designed to temper air during winter months, preventing uncomfortably cold air from being delivered to hallways. Some systems also provide cooling capabilities during summer. A frequent concern from residents is that hallway temperatures don’t match their unit temperatures.

It’s important to understand that hallways and living spaces have different temperature requirements:

- **Hallways**: 20C (68F) is generally sufficient for these transitional spaces
- **Living units**: Typically maintained at 23C (74F) for optimal comfort

This temperature difference is intentional and energy-efficient. Unlike residential furnaces that recirculate and heat already-warm return air (typically around 20C), MUA systems constantly heat incoming outdoor air, which in winter can be as cold as -10C or lower. The energy demand to heat this cold outside air to comfortable temperatures is substantial, making it impractical and wasteful to maintain hallway temperatures at the same level as living spaces.

I cannot stress enough the importance of regular preventative maintenance for MUA systems. MUA filters often need to be changed every month. If you only have bi-monthly inspections, then every two months is adequate. MUA belts, motors, and components also need regular inspection.

In particular, the inlet dampers on many MUA units tend to get neglected and should be lubricated twice a year. Like any gas-fired appliance, the major componentsburners, ventor motors, heat exchangers, etc.should be thoroughly inspected during an annual inspection, which should ideally be scheduled in the summer.

In the past decade, Variable Frequency Drives ([VFDs](https://www.danfoss.com/en-us/about-danfoss/our-businesses/drives/what-is-a-variable-frequency-drive/)) have become increasingly common in HVAC applications. These devices control motor or pump operation, allowing systems to run at reduced speeds when full capacity isn’t needed. For MUA units, this capability offers significant energy-saving benefits.

**How VFDs Work in MUA Applications:**

- A VFD adjusts the motor speed based on time-of-day requirements
- During high-demand periods (mornings and evenings), the system runs at higher capacity
- During low-demand periods (midday and overnight), the system automatically reduces airflow
- Less airflow means less air needs heating, reducing energy consumption

The energy savings are particularly notable in cold weather, when heating demands are highest. A properly configured VFD system typically pays for itself within 2-3 years through reduced energy costs.

However, there are practical limits to how much airflow can be reduced. Building codes, occupancy requirements, and equipment specifications all create minimum thresholds that must be maintained. Always consult with a qualified HVAC professional before implementing VFD controls on your MUA system.

Mastering complex systems like MUAs sets you apart. Property.com empowers elite HVAC professionals with exclusive advantages: gain homeowner insights with our ‘[Know Before You Go](https://mccreadie.property.com)’ tool for smarter service, boost your SEO with a premium subdomain, and manage your reputation effortlessly. Limited spots per trade/region. Elevate your business become a certified Property.com Pro today.

Make-up air units come in several configurations, each with specific applications and maintenance considerations:

### **Direct-Fired MUA Systems**

Direct-fired units pass air directly through a gas flame, providing highly efficient heating. These systems:  
– Achieve 100% thermal efficiency  
– Deliver rapid temperature rise  
– Require careful combustion management to prevent introducing contaminants  
– Need regular burner inspection and cleaning

### **Indirect-Fired MUA Systems**

Indirect-fired units use a heat exchanger that separates combustion products from the supply air. These systems:  
– Offer cleaner air delivery (no combustion products in airstream)  
– Typically operate at 80-85% efficiency  
– Require regular heat exchanger inspection for cracks or corrosion  
– Need more frequent filter maintenance

### **Electric MUA Systems**

Electric systems use resistance heating elements rather than combustion. These systems:  
– Provide clean operation with no combustion products  
– Are simpler mechanically with fewer maintenance points  
– Typically have higher operating costs than gas systems  
– Require periodic inspection of heating elements and contactors

Each system type has specific maintenance requirements that should be incorporated into your preventative maintenance program.

Even well-maintained make-up air units can experience operational issues. Here are some common problems and basic troubleshooting steps:

### **Insufficient Airflow**

**Symptoms:** Poor hallway pressurization, odor migration between units, or doors difficult to open/close.

**Troubleshooting Steps:**  
1. Check and replace clogged filters  
2. Inspect fan belts for proper tension and wear  
3. Verify damper positions and operation  
4. Confirm VFD settings (if equipped)  
5. Check for obstructions at outdoor air intake

### **Temperature Control Issues**

**Symptoms:** Inconsistent hallway temperatures, overheating, or insufficient heating.

**Troubleshooting Steps:**  
1. Verify thermostat operation and calibration  
2. Check gas pressure at manifold (for gas units)  
3. Inspect heating elements (for electric units)  
4. Confirm proper burner operation and flame pattern  
5. Check discharge temperature sensor calibration

### **Excessive Noise**

**Symptoms:** Unusual vibrations, rattling, or air noise complaints.

**Troubleshooting Steps:**  
1. Check for loose components or panels  
2. Inspect fan wheel for dirt accumulation or damage  
3. Verify proper belt alignment  
4. Check motor bearings and mounts  
5. Inspect ductwork for disconnections or damage

### **System Won’t Start**

**Symptoms:** Unit fails to operate when called for.

**Troubleshooting Steps:**  
1. Verify power supply and check for tripped breakers  
2. Check safety controls (high limit, airflow switch)  
3. Inspect control circuit fuses  
4. Confirm proper operation of control board  
5. Check for alarm conditions on VFD display (if equipped)

For persistent issues, consult with a qualified HVAC technician who specializes in commercial ventilation systems.

- **Regular Maintenance is Critical**: Monthly filter changes and bi-annual inspection of dampers and key components ensure proper operation
- **Proper Air Balancing**: Have professional air balancing performed whenever significant changes are made to the building or after tenant modifications to diffusers
- **Temperature Expectations**: Hallway temperatures should be maintained around 20C (68F), not at the same temperature as living spaces
- **Energy Efficiency**: Consider VFD installation to reduce energy costs while maintaining proper building pressurization
- **Preventative Approach**: Address small issues before they become major problems through regular system inspection

## **Conclusion**

Make-up air units are essential yet often overlooked components in multi-residential buildings. Their proper operation affects building pressure, air quality, odor control, and energy efficiency. By understanding how these systems work and implementing regular maintenance practices, building managers can ensure optimal performance while minimizing operating costs.

Check out the video tour below featuring an example of a direct-fired make-up air system to see these principles in action:

For more HVAC insights, visit my [YouTube](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber) channel or listen to The HVAC Know It All [podcast here](http://anchor.fm/hvacknowitall) or on your favorite podcast app.

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/make-up-air-units-explained"

--------------------------------------------------

# ID: 194

## Title: HVAC Guide: How to Properly Check Manifold Gas Pressure for Optimal Performance

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2018-12-26T15:55:00

## Word Count: 1161

## Categories: Components

## Tags: None

## Permalink: https://hvacknowitall.com/blog/checking-manifold-gas-pressure

## Description:
## Checking Manifold Gas Pressure: A Critical HVAC Maintenance Procedure

Testing the manifold pressure on gas-fired appliances is one of the most crucial yet often overlooked maintenance procedures in HVAC service. This essential diagnostic test ensures your furnaces, boilers, and rooftop units operate at optimal efficiency and safety levels.

When performed correctly during routine maintenance, service calls, or system startups, proper manifold pressure verification can:

- Prevent premature heat exchanger failure
- Optimize fuel efficiency and performance
- Ensure safe operation of gas appliances
- Extend equipment lifespan
- Reduce callback service requests

This guide will walk you through the process of accurately testing manifold gas pressure, along with demonstrating how to verify negative heat exchanger pressure for pressure switch operation.

Manifold pressure refers to the gas pressure measured at the outlet of the gas valve before it reaches the burners. This pressure directly affects how much gas flows to the burners, which determines the heat output of the appliance.

Gas-fired appliances are designed to operate within specific manifold pressure ranges, typically measured in inches of water column (inWC) or water column (WC). The manufacturer specifications determine the correct pressure settings for optimal performance:

- Natural gas appliances typically operate between 3.2” and 3.8” WC
- Propane appliances usually require between 10” and 11” WC

**Important:** Always consult the manufacturer’s specifications on the unit’s rating plate or installation manual for the correct manifold pressure values specific to your equipment.

Improper manifold pressure settings can lead to numerous performance issues and potential equipment damage. Recognizing these symptoms can help diagnose pressure-related problems:

### Under-fired Appliances (Low Manifold Pressure)

- Insufficient heating output
- Delayed ignition
- Flame lifting from burners
- Frequent cycling
- Poor combustion
- Higher than normal CO levels

### Over-fired Appliances (High Manifold Pressure)

- Excessive heat
- Flame impingement on heat exchanger
- Premature heat exchanger failure
- Sooting
- Higher than normal fuel consumption
- Loud operation or rumbling
- Increased NOx emissions

Correctly setting manifold pressure according to manufacturer specifications helps avoid these issues and ensures optimal appliance performance.

To properly test manifold gas pressure, you’ll need the following equipment:

1. **Manometer** – Either digital or analog (U-tube) for measuring gas pressure
2. **Manifold pressure test port adapters** – For connecting to test ports
3. **Small adjustable wrench** – For accessing and adjusting the gas valve
4. **Screwdrivers** – Both flathead and Phillips for removing covers and making adjustments
5. **Soap solution** – For leak testing after completing the procedure

For testing negative pressure in the heat exchanger, you’ll also need:  
– **Pressure switch testing hose kit**  
– **Digital micromanometer** (for precise readings)

Always ensure your test equipment is properly calibrated for accurate readings.

Follow these steps to safely and accurately test manifold gas pressure on your HVAC equipment:

### Safety Precautions

1. **Turn off power** to the unit before beginning work
2. **Identify gas shutoff valve** location in case of emergency
3. **Ensure proper ventilation** in the work area
4. **Never bypass safety controls** during testing

### Testing Procedure

1. Locate the manifold pressure test port on the gas valve
2. Remove the test port screw/plug (typically 1/8” pipe plug)
3. Connect your manometer to the test port using appropriate hose/fitting
4. Zero your manometer per manufacturer instructions
5. Restore power to the unit and initiate a call for heat
6. Once main burners are operating, observe and record the manifold pressure
7. Compare reading to manufacturer specifications on the rating plate or in documentation
8. If adjustment is needed, locate the adjustment screw on the gas valve (often beneath a cover screw)
9. Make small adjustments and recheck pressure until correct reading is achieved
10. Turn off the unit, remove the manometer, and replace the test port plug
11. Check for gas leaks using soap solution at the test port
12. Return the unit to normal operation

### Checking Heat Exchanger Negative Pressure

1. Locate the pressure switch
2. Disconnect the hose from the pressure switch
3. Connect your manometer to the pressure switch tube
4. Initiate a call for heat and observe the negative pressure reading
5. Verify the reading exceeds the pressure switch rating to ensure proper operation

The video below demonstrates these procedures in detail.

The following video provides a detailed walkthrough of checking manifold gas pressure along with bonus footage showing how to verify negative heat exchanger pressure for pressure switch operation:

Precision matters, from manifold pressure checks to client insights. Property.com equips elite contractors with the ‘[Know Before You Go](https://mccreadie.property.com)’ tool, providing homeowner permit history, home value, and potential savings data *before* you arrive. Elevate your service and stand out. Secure your exclusive, invitation-only spot in your region today and lock in early adopter rates. Visit Property.com to learn more.

## Conclusion

Proper manifold pressure testing is a fundamental skill that separates average technicians from true HVAC professionals. By regularly verifying and correctly setting manifold pressure on gas-fired equipment, you ensure optimal performance, extend equipment lifespan, and provide superior service to your customers.

Remember to always consult manufacturer specifications for correct pressure settings and follow all safety protocols when working with gas appliances.

Elevate your HVAC expertise and outshine your peers by delving into our informative [blog articles](https://hvacknowitall.com/blog), listening to our [industry-specific podcast](https://hvacknowitall.com/podcasts), and subscribe to our [YouTube channel](https://www.youtube.com/@HVACKnowItAll), where we share valuable insights tailored specifically for HVAC technicians seeking to enhance their business and provide exceptional service.

],
"step": [
]

],
"tool": [
]

],
"totalTime": "P10Y",
"about": {
"@type": "Occupation",
"name": "HVAC Technician",
"description": "Professional who installs, maintains, and repairs heating, ventilation, air conditioning, and refrigeration systems.",
"occupationalCategory": "47-2152.00"

--------------------------------------------------

# ID: 261

## Title: HVAC MAINTENANCE: WHY AND WHEN TO REPLACE REFRIGERANT HOSE SEALS

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2018-11-24T18:27:00

## Word Count: 637

## Categories: None

## Tags: None

## Permalink: https://hvacknowitall.com/blog/replace-refrigerant-hose-seals

## Description:
## The Importance of Hose Seal Maintenance

To some HVAC technicians, replacing hose seals or gaskets is actually a foreign concept. But hose maintenance isn’t just good practiceit’s essential for successful service and installation work. When hose seals become compressed or broken, they can cause leaks during testing or evacuation procedures and may even restrict refrigerant flow in some cases. Understanding when and how to replace these critical components can prevent callbacks and ensure system integrity.

The frequency of seal replacement depends largely on use and how you handle your equipment. Over-tightening connections is the leading cause of premature seal failure, so apply appropriate torque when connecting hoses.

Inspect your seals before each use, looking for these signs that indicate replacement is needed:

- Visible compression or flattening
- Cracks or breaks in the seal material
- Hardening or loss of elasticity
- Discoloration or deterioration
- Previous leak issues during pressure testing

If seals appear damaged or compressed, it’s time to replace them before they compromise your work quality.

The [Yellow Jacket Gasket Remover](http://yellowjacket.com/product/gasket-remover-tool/) Tool is designed specifically for professional seal maintenance. This multi-functional tool serves as:

- A precision pick for removing old gaskets without damaging fittings
- A built-in Schrader core tool
- A convenient storage compartment for extra seals

![](https://hvacknowitall.com/wp-content/uploads/2022/11/1674411_edit.jpg)

For optimal seal performance and longevity, I recommend using [Nylog Blue](http://www.refrigtech.com/nylog-blue/) during assembly. This specialized lubricant helps keep the seal and hose connection properly lubricated, extending seal life and improving leak resistance.

Just like maintaining your tools prevents costly callbacks, Property.com helps you prevent wasted trips. Our exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool provides homeowner insights, permit history, and potential savings, so you arrive prepared. Secure your spot in our limited-access network for top HVAC pros and elevate your business. Learn more about Property.com certification.

The video below shows the Yellow Jacket tool in action using Nylog Blue as an assembly lubricant. This demonstration highlights the proper technique for removing old seals and installing new ones without damaging your equipment.

Even with regular maintenance, you might encounter seal-related problems in the field:

- For persistent leaks: Verify you’re using the correct seal size and type for your specific fittings
- For difficult seal removal: Apply a small amount of lubricant to loosen stubborn seals
- For premature wear: Review your connection technique to prevent over-tightening

## Keep Your Tools in Top Condition

Proper hose seal maintenance might seem like a small detail, but it significantly impacts your efficiency and reputation as an HVAC professional. By regularly inspecting and replacing seals with quality tools, you’ll prevent costly callbacks and ensure accurate system charging and testing.

Check out my [YouTube](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber) channel for more tips, tricks, and troubleshooting videos and listen to The HVAC Know It All podcast [here](http://anchor.fm/hvacknowitall) or on your favorite podcast app. Happy HVACing!

],
"step": [
]

--------------------------------------------------

# ID: 471

## Title: HVAC Tip: The Critical Role of CO2 in Indoor Air Quality Assessment

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2018-11-24T10:24:00

## Word Count: 1137

## Categories: Indoor Air Quality

## Tags: None

## Permalink: https://hvacknowitall.com/blog/iaq-and-carbon-dioxide

## Description:
## The Forgotten Element in Indoor Air Quality: Carbon Dioxide

When discussing Indoor Air Quality (IAQ), HVAC technicians typically focus on filtration systems, temperature control, humidity management, and air purification methods. These are indeed vital components of a healthy indoor environment. However, there’s one critical element that’s frequently overlooked in IAQ assessments: carbon dioxide (CO2) levels.

High concentrations of CO2 indoors can cause occupants to experience headaches, fatigue, decreased cognitive function, and general discomforteven when all other IAQ parameters appear optimal. Understanding and monitoring CO2 levels is essential for ensuring truly comprehensive indoor air quality and occupant comfort.

Carbon dioxide is naturally present in our atmosphere, but indoor concentrations can quickly rise above outdoor levelsparticularly in poorly ventilated, densely occupied spaces. Understanding what constitutes safe versus problematic CO2 levels is crucial for proper IAQ assessment.

| CO2 Concentration | Effects and Guidelines |
| --- | --- |
| 350-450 ppm | Normal outdoor air level |
|  **SAFETY FIRST:** Always wear appropriate PPE including gloves and safety glasses when handling refrigerant. Follow EPA regulations regarding refrigerant handling and recovery to protect yourself and the environment.

You should always familiarize yourself with the equipment you are working with by reviewing the manufacturer’s documentation. Below, I’ve included simple diagrams of how to connect the required equipment and step-by-step guides for both methods.

### **When to Use Each Method:**

| **Recovery Method** | **Best Used When** | **Advantages** | **Limitations** |
| --- | --- | --- | --- |
| Direct Recovery | Small systems ( [View this post on Instagram](https://www.instagram.com/p/CG2caV7LGMD/?utm_source=ig_embed&utm_campaign=loading)
>
> [A post shared by Gary McCreadie HVAC/R Tech/Business Owner (@hvacknowitall1)](https://www.instagram.com/p/CG2caV7LGMD/?utm_source=ig_embed&utm_campaign=loading)

This will be your faster option if the system has 15 or more pounds of refrigerant. The more refrigerant the system holds, the more time you’ll save.

\*\* PRO TIP:\*\* Using an inline sight glass during push-pull recovery will allow you to visually determine when the liquid flow has stopped.

![Diagram showing the push/pull refrigerant recovery process with connections between system, recovery machine, and cylinder](https://hvacknowitall.com/wp-content/uploads/2018/05/Refrigerant-Recovery-Process.png)

1. Start with all valves closed (recovery cylinder, recovery machine, manifold, hoses.)
2. Setup hoses as shown in the diagram.
3. ZERO/TARE the refrigerant scale.
4. Set the recovery machine to recover.
5. **PURGE THE HOSES OF AIR:** This process differs slightly from direct recovery  
   a. Open the liquid line service valve or core tool  
   b. Loosen and unseat the hose connected to the liquid port on the recovery tank  
   c. Allow refrigerant to briefly flow, purging air from the line  
   d. Retighten the connection once refrigerant is present  
   e. Repeat the same process for the vapor line service valve and hose
6. Turn on the recovery machine.
7. When liquid recovery is complete (visible in sight glass if installed), switch to Direct Vapor Recovery method to finish.

| **Problem** | **Possible Causes** | **Solution** |
| --- | --- | --- |
| Slow recovery rate | Restrictions in hoses/fittings | Remove valve cores, use larger diameter hoses |
|  | High recovery cylinder temperature | Cool cylinder with fan or water |
|  | Dirty system | Add inline filter drier |
| Recovery machine shuts off | High head pressure | Cool recovery cylinder, check for restrictions |
|  | Internal overload protection | Allow machine to cool, check manufacturer guidelines |
| Scales reading incorrectly | Not zeroed properly | Re-zero scales with empty cylinder |
|  | Wind interference | Shield scale from wind |

### **Valve Core Removal Tools**

```
If you were only going to change one thing  this is it!  If you're stuck pulling through valve cores, get two of these.  They'll even help speed up your evacuation.
```

### **Recovery Cylinder**

```
Make sure the cylinder is clean and has been evacuated to 500 microns or less.  And NEVER fill beyond 80%. This allows for the expansion of the refrigerant.   
If it's practical, use a larger cylinder; this will make the recovery go quicker.
```

### **Hoses**

```
Avoid hoses with "anti-blowback" or "low loss" style fittings.   
Standard hoses are "  using larger diameter hoses will get you faster recovery. They're often marketed as "heavy duty," "charging," or "vacuum" hoses.  
Use hoses that are as short as possible.
```

Just like speeding up recovery saves time on the job, Property.com helps you work smarter. Our exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool provides homeowner insights like permit history and home value, so you arrive prepared. Plus, boost your credibility with a Property.com certified profile and connect with referrals. Limited spots available per trade/region. Learn more about joining our premium network.

### **Temperature**

```
Cool down the recovery cylinder this will drop the pressure of the recovery cylinder.    
With many recovery machines, you can use the fan to draw air over the recovery tank.  
Water will work even better, but you'll need water flow.

Cool down the refrigerant!  This one tends to be your best bet if you're dealing with large volumes of refrigerant  there are heat exchangers available just for this purpose.
```

### **Filter It!**

```
If you suspect the system refrigerant to be dirty, use an inline filter drier at the inlet to the recovery machine.
```

## **Conclusion**

Proper refrigerant recovery is both a regulatory requirement and a professional responsibility. The EPA requires technicians to minimize refrigerant emissions, and using the correct techniques ensures you comply with regulations while working efficiently.

With methods ranging from simple adjustments to specialized equipment, you have multiple options to speed up recovery across different applications. Try implementing these techniques on your next job and see how they impact your efficiency.

Remember to always prioritize safety, follow EPA guidelines for handling refrigerants, and refer to your specific recovery machine’s manual for manufacturer-recommended procedures.

],
"tool": [
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/refrigerant-pump-down-explained"
},
"keywords": "refrigerant pump down, HVAC, recycling pump down, non-recycling pump down, low pressure switch, solenoid valve, compressor protection, refrigeration system"

],
"tool": [
]

]

],
"step": [
]

]

--------------------------------------------------

# ID: 123

## Title: HVAC Guide: How To Safely Test a Run Capacitor Under Load

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2018-03-30T13:32:00

## Word Count: 784

## Categories: Air Conditioning, Troubleshooting

## Tags: None

## Permalink: https://hvacknowitall.com/blog/checking-run-capacitors-under-load

## Description:
## How To Safely Test a Run Capacitor Under Load

Testing run capacitors under load is an alternative diagnostic method that can be performed without powering down the HVAC system. While testing capacitors with the power off remains the recommended approach for safety, there are specific situations where testing under load becomes necessarysuch as when servicing critical environments or when system shutdown isn’t possible during control setup procedures.

This guide explains the proper technique for accurately measuring a run capacitor’s performance while the system remains operational, allowing you to verify capacitor health without interrupting service.

Testing capacitors with the power off should always be your first choice. From a safety perspective, working in a de-energized electrical cabinet significantly reduces shock and arc flash hazards compared to reaching into live electrical components.

However, certain circumstances may require testing while the system continues to run:

- When the HVAC system serves critical environments (hospitals, data centers, etc.)
- During system control setup procedures when shutdown isn’t feasible
- When troubleshooting intermittent issues that only appear during operation

If you must test under load, use insulated tools, wear appropriate PPE, and maintain heightened awareness of electrical safety practices throughout the procedure.

Follow these precise steps to accurately test a run capacitor while the system is operating:

1. **Measure Start Winding Amperage**
2. Set your clamp meter to the amps function
3. Carefully clamp around the motor start winding wire connected to the capacitor
4. Record the amperage reading
5. **Measure Back EMF Voltage**
6. Switch your meter to the volts setting
7. Measure voltage across the capacitor terminals
8. This reading represents the motor’s back electromotive force ([EMF](https://openpress.usask.ca/physics155/chapter/6-1-electromotive-force/))
9. Record this voltage reading
10. **Calculate Microfarad Value**
11. Apply the following formula to determine the capacitor’s actual microfarad value under load:  
    `Capacitor F = (Start Winding Amps 2650) Back EMF Voltage`
12. **Evaluate Results**
13. Compare your calculated value to the capacitor’s rated microfarad value
14. Check if your result falls within the manufacturer’s specified tolerance range (typically 5-6%)
15. If within range, the capacitor is functioning properly
16. If outside this range, the capacitor likely needs replacement

You might wonder about the origin of the 2650 constant used in the formula. This value is derived from electrical principles relating to AC circuits and capacitive reactance.

The constant 2650 incorporates:  
– The standard 60Hz frequency of North American electrical systems  
– The mathematical relationship between capacitive reactance and capacitance  
– Conversion factors to yield results in microfarads (F)

This calculation method provides a reliable field test for capacitor performance without requiring specialized capacitor testing equipment.

For a visual walkthrough of this testing procedure, watch the demonstration below:

Efficient troubleshooting starts before you arrive. Property.com’s exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool gives certified Pros critical homeowner insights like permit history and potential upgrade needs, helping you diagnose issues faster. Join our premium network limited spots available per trade and region. Secure your advantage today.

## For More HVAC Tips and Tutorials

Check out my [YouTube channel](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber) for additional troubleshooting videos, technical tips, and HVAC guides. You can also tune into [The HVAC Know It All podcast](https://hvacknowitall.com/podcasts) on your favorite podcast app for more industry insights and professional discussions.

Happy HVACing!

],
"tool": [
],
"supply": [
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/college-or-trade-school-hvac-career"
},
"about": [
},
]

--------------------------------------------------

# ID: 322

## Title: Understanding Heat in HVAC: Sensible vs. Latent Heat Explained

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2018-03-10T16:04:00

## Word Count: 1083

## Categories: Air Conditioning

## Tags: None

## Permalink: https://hvacknowitall.com/blog/the-hot-and-cold-of-it-vol-2

## Description:
## Understanding Heat in HVAC Systems

In the world of HVAC and refrigeration, we don’t add coldwe remove heat! While many people use terms like “hot” and “cold” to describe comfort, HVAC professionals understand that heat is a form of energy that can be measured, transferred, and controlled. Understanding the different types of heat and how they behave is fundamental to mastering refrigeration and air conditioning systems.

Heat energy can take many forms. Mechanical energy is expressed as horsepower, electrical energy as watts, and thermal energyour focus todayis measured in British Thermal Units (BTUs). Before we dive into the practical applications of heat in HVAC systems, let’s explore where this critical unit of measurement came from and how different types of heat impact our work every day.

The British Thermal Unit has an interesting history dating back to the mid-1800s. It was developed by Thomas Tredgold, an English railroad engineer who also worked in heating and ventilation. In his book “The Warming and Ventilating of Public Buildings,” Tredgold wrote:

“In order to compare the effects of different kinds of fuel, some convenient measure of effect should be adopted: not only for the purpose of lessening the trouble of calculation, but also to render it more clear and intelligible. I shall, therefore, without regarding the measures of effect employed by others, adopt one of my own, which I have found useful in this and other inquiries of a similar nature. I take as the measure of the effect of a fuel, the quantity, in pounds avoirdupois (a system of weights based on 16 ounces or 7000 grains), which will raise the temperature of a cubic foot of water one degree of Fahrenheit’s scale.”

This early definition evolved into the modern BTU: “the amount of energy needed to change the temperature of one pound of water one degree Fahrenheit.” This precise definition gives HVAC technicians a consistent way to measure and calculate heat transfer in our systems.

Sensible heat is exactly what its name suggestsheat that can be sensed or measured with a thermometer. It represents a change in temperature with no change in state. The thermometer registers the intensity of BTUs present.

Here’s a practical example: You bring home your favorite beverage at room temperature (70F) and place it in your refrigerator (35F). The beverage gives up its heat to the cooler air inside the fridge, causing its temperature to drop. This is a fundamental principle in thermodynamicsheat energy naturally flows from higher temperature (higher energy) to lower temperature (lower energy).

In air conditioning systems, sensible heat changes occur across components like the evaporator coil. When warm air passes over the cold evaporator, sensible heat transfers from the air to the refrigerant, lowering the air temperature without changing its moisture content.

The term “latent” comes from Latin, meaning “hidden.” Unlike sensible heat, latent heat cannot be measured with a thermometeryet it plays a crucial role in HVAC systems. Latent heat is the energy involved when a substance changes state (solid/liquid/vapor) while maintaining the same temperature.

Consider boiling water: As you heat water to 212F (at sea level), the temperature remains constant at 212F even as you continue to add heat. This additional energy doesn’t raise the temperature but instead converts the liquid water to water vapor. Similarly, when ice melts, it remains at 32F until all the ice has converted to liquid, despite absorbing heat from its surroundings.

You can verify this yourself with a simple experiment: Mix crushed ice with distilled water and measure the temperature. It will remain steady at 32F until all the ice melts. This principle is so reliable that it’s commonly used to calibrate digital thermometers.

In air conditioning, we’re controlling four key factors: temperature, humidity, indoor air quality, and air circulation. Temperature control involves managing sensible heat, while humidity control tackles latent heat. The capacity of an air conditioner depends on its ability to remove both sensible and latent heat gained within a conditioned space.

Within the [refrigeration cycle](https://www.hvacknowitall.com/blogs/blog/595767-the-refrigeration-cycle-explained), both types of heat transfer occur. For example, when refrigerant enters the evaporator as a low-temperature, low-pressure boiling liquid, it absorbs heat from the surrounding air. This causes the liquid refrigerant to vaporizea latent heat exchange, as the refrigerant changes state while its temperature remains constant. Once all the liquid has vaporized, continued heat absorption causes the vapor’s temperature to risea sensible heat exchange. Both processes represent BTUs being added to the refrigerant.

You’ve mastered the fundamentals of heat transfer. Ready to elevate your established HVAC business? Property.com offers an exclusive, invitation-only network for top-tier contractors. Gain a competitive edge with our ‘[Know Before You Go](https://mccreadie.property.com)’ homeowner insights, boost your online authority with a custom Property.com subdomain, and streamline your reputation management. Limited spots per trade and region. Secure your exclusive status and early adopter benefits today. Learn more about becoming a Property.com Certified Pro.

## Mastering Heat Management in HVAC

For HVAC professionals, a comprehensive understanding of heatboth sensible and latentis essential to our work. Every comfort issue we solve, every system we design, and every efficiency we improve relies on our ability to properly manage heat transfer. By mastering these fundamental concepts, we build the foundation for excellence in all aspects of heating, ventilation, air conditioning, and refrigeration.

Check out the [HVAC Know It All YouTube channel](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber) for more tips, tricks, and troubleshooting videos, and tune into [The HVAC Know It All podcast](http://anchor.fm/hvacknowitall) available on your favorite podcast platform. Happy HVACing!

]

},
"datePublished": "2023-11-05",
"dateModified": "2023-11-05",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/checking-switches-contactors-continuity"
},
"about": {
"@type": "Thing",
"name": "HVAC maintenance and troubleshooting"
},
"keywords": "HVAC, continuity testing, switches, contactors, electrical troubleshooting, blown fuses, disconnect switch, ohm readings"

]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/hvacing-like-a-boss"
},
"about": [
],
"mentions": {
"@type": "Person",
"name": "Joshua Thompson",
"description": "Moderator for My HVAC Hub Facebook group"

--------------------------------------------------

# ID: 85

## Title: HVAC Safety: Essential Nitrogen Tank Handling and Pressure Regulation Guidelines

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2018-02-16T12:30:00

## Word Count: 869

## Categories: Refrigerants, Air Conditioning, Heat Pumps, Troubleshooting

## Tags: None

## Permalink: https://hvacknowitall.com/blog/nitrogen-tank-and-gauge-precautions

## Description:
## Watch Out For That Nitrogen Tank Pressure!

Nitrogen tanks are essential tools in many HVAC procedures, but they contain gas compressed to approximately 2200-2400 PSIa pressure level capable of causing catastrophic damage to equipment and severe injury to technicians if mishandled. The extreme force contained in these cylinders demands proper respect and safety protocols. The following guidelines cover essential safety practices when working with these potentially dangerous high-pressure cylinders.

Before attaching your nitrogen regulator to any cylinder, inspect the threads of the regulator and cylinder valve to ensure they are not stripped or damaged. Damaged threads can lead to dangerous gas leaks or even cause the regulator to become a high-velocity projectile if it detaches under pressure.

Always make sure you back out the regulator handle all the way (turn counterclockwise until loose) before attachment. This prevents sudden pressure surges when you open the cylinder valve, which could damage sensitive equipment or create unsafe conditions.

After securely fastening the regulator to the cylinder, take a critical safety precaution: before opening the cylinder valve, turn and direct the regulator away from yourself and others.

If the regulator becomes a projectile due to improper attachment or damaged threads, you do not want to be standing in front of it. Always position yourself to the side when opening a cylinder valve for the first time after attachment.

Open the cylinder valve slowly to allow pressure to build gradually in the regulator. This controlled approach helps prevent regulator damage and maintains safety.

Several types of nitrogen regulators are used in HVAC applications:

1. **Single-stage regulators** – Reduce cylinder pressure to working pressure in one step. These are commonly used for basic HVAC testing procedures.
2. **Two-stage regulators** – Reduce pressure in two steps for more precise control, which is ideal for sensitive equipment or testing.
3. **Flow meters with regulators** – Include built-in measurement for controlled flow rates during procedures like system purging.

Regardless of regulator type, all require the same safety precautions. Always use regulators specifically designed for nitrogen and rated for the full cylinder pressure of at least 3000 PSI.

While carrying nitrogen cylinders from job to job in your vehicle, ensure they are strapped down and secured tightly and the regulator is removed while in transit. Unsecured cylinders can become dangerous projectiles during sudden stops or accidents.

Additional transportation safety measures include:

1. Secure cylinders in an upright position using straps or chains to prevent tipping or rolling
2. Store cylinders in well-ventilated areas away from heat sources
3. Use a cylinder cart with a safety chain when moving tanks around job sites
4. Never transport cylinders in the passenger compartment of a vehicle

The Occupational Safety and Health Administration (OSHA) has [specific guidelines for compressed gas cylinder handling and storage](https://www.osha.gov/compressed-gas-cylinders/safety-handling) that all technicians should follow.

These precautions should be thought of and employed when working with any compressed gas cylinder, not just nitrogen. Similar safety protocols apply to refrigerant tanks, oxygen, acetylene, and propane cylinders commonly used in HVAC work.

Check out this Myth Busters Video and see what a compressed tank of gas is capable of doing when compromised:

Safety first, professionalism always. Just like handling nitrogen requires care, building a standout HVAC business requires the right tools and credibility. Property.com offers certified pros exclusive access to homeowner insights with ‘[Know Before You Go](https://mccreadie.property.com)’, enhanced SEO through a custom subdomain, and complete reputation management. Secure your premium spot in our limited network and elevate your business beyond the competition. Learn more about Property.com Certification.

## **Finally**

Check out the link to my [YouTube](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber) channel for more tips, tricks, and troubleshooting videos, and check out The HVAC Know It All [podcast here](https://hvacknowitall.com/podcasts) or on your favorite podcast app.

Happy HVACing…

],
"tool": [
]

],
"tool": [
]

},
},
},
},
},
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/dont-be-scared-its-only-hvac"
},
"image": "https://hvacknowitall.com/wp-content/uploads/2022/11/1558650\_edit.png",
"keywords": "HVAC mistakes, HVAC learning, HVAC confidence, HVAC technician development, HVAC troubleshooting",
"mentions": [
]

},
"mainEntity": {
"@type": "Person",
"name": "Julia Ballantyne",
"jobTitle": "HVAC Technician",
"worksFor": {
"@type": "Organization",
"name": "Display Fixtures Refrigeration"
},
"memberOf": [
]
},
"about": [
],
"mentions": [
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/hvac-tip-carbon-tracking-explained"
},
"keywords": [
"carbon tracking",
"HVAC troubleshooting",
"contactor",
"electrical shorts",
"preventative maintenance",
"megohmmeter testing"
],
"articleSection": "HVAC Troubleshooting",
"proficiencyLevel": "Expert"

},
"hasPart": [
]

},

"datePublished": "2023",

"articleSection": "HVAC",

"keywords": "hot gas bypass valve, HVAC, refrigeration, compressor short cycling, evaporator freezing, capacity control"

},
"image": "https://hvacknowitall.com/wp-content/uploads/2017/12/carbon-monoxide-danger-sign-1024x683.webp",
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/carbon-monoxide-testing-and-co-action-limits"
},
"keywords": "carbon monoxide testing, CO action limits, HVAC safety, carbon monoxide safety, HVAC testing equipment"

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": ""

--------------------------------------------------

# ID: 508

## Title: A Christmas On Call: The HVAC Technician&#8217;s Holiday Reality

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2017-12-21T11:28:00

## Word Count: 604

## Categories: Career in the Trades

## Tags: None

## Permalink: https://hvacknowitall.com/blog/a-christmas-on-call

## Description:
# A Christmas On Call: The HVAC Technician’s Holiday Reality

While families gather around the fireplace during the holidays, HVAC technicians often find themselves on rooftops and in basements, responding to emergency service calls. This poem captures the raw reality of sacrificing precious family time to ensure others stay warm during Christmas. Any technician who has worked through the holidays will recognize these feelings – from frustration to the heartwarming reminder of why we do what we do.

Tis the holiday season, great time of year  
Except I’m on call, can’t have eggnog and rum or even a beer

Turkey is in the oven with home made stuffing  
Too bad I’m on a roof with a fucking flame snuffing

Owner rings up with a string of new calls   
While the laughter of children echos through his halls

Arrive to the customer, their home is warm and cozy  
“Oh did I forget to cancel?”…You sure fucking did homie…Then asshole asks if he still owes me

I love Christmas and being on call  
As much as I love razor nicks while shaving my balls

Six o clock, calls are all done  
Maybe I’ll make it back home to join in on some fun

Pull up to the drive, time to get tipsy  
Till my neighbour runs over…”my heats not working, are you busy?”

Fuck you neighbour, fuck you boss  
Eat my shit Santa and fuck you Jack Frost

Wait, what’s this…a note on the door

Note…

Thank you dad for working hard, you are the best  
You take care of us all year and do it better than the rest

We kept a plate warm, it’s in the oven…we know how much you love mom’s home made stuffing  
There are gifts for you still under tree with your favourite slippers to help warm up your feet.

We love you Dad, hugs and kisses  
You’re always at the top of our Christmas wish list

Anger slowly diminishes….I just remembered why I still love Christmas

Working hard through the holidays? [Property.com](https://mccreadie.property.com) helps established HVAC pros build a stronger business with less hassle. Our exclusive network, reputation management tools, and homeowner insights give you an edge, letting you focus on what matters. Secure your spot in our invitation-only network and gain the recognition you deserve. Learn more about Property.com Pro.

Merry Christmas to all my hard working techs out there. You deserve recognition for all you do. A toast to you and your family…Happy HVACing!

For those new to the trade who might face their first holiday on call, check out our [Tips for HVAC Apprentices](https://hvacknowitall.com/tips-for-hvac-apprentices) post.

Looking for more industry insights? Listen to these recommended podcasts: [Don’t Be Scared It’s Only HVAC](https://hvacknowitall.com/podcast-dont-be-scared-its-only-hvac) and [Factors To Consider When Choosing Employment](https://hvacknowitall.com/podcast-factors-to-consider-when-choosing-employment).

The holidays can be demanding for those in the skilled trades, but moments like finding that note remind us why we do what we do. To everyone balancing service calls with family traditions – your work matters, your sacrifices are seen, and your skills keep communities comfortable during the most wonderful time of the year.

},

"mainEntityOfPage": {

"@type": "WebPage",

"@id": "https://hvacknowitall.com/blog/five-minutes-to-be-a-better-tech"

--------------------------------------------------

# ID: 421

## Title: PROTECTING HVAC TOOLS AND ELECTRICAL COMPONENTS WITH SILICONE GREASE

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2017-12-16T09:02:00

## Word Count: 656

## Categories: Tools and Equipment

## Tags: None

## Permalink: https://hvacknowitall.com/blog/lubricate-your-tools-to-prevent-corrosion

## Description:
## Preventing Economizer Control Board Corrosion

Economizer control boards installed in outdoor air streams face a significant challenge: accelerated corrosion due to constant exposure to changing weather conditions. This corrosion leads to premature failure, requiring frequent and costly replacements. In my field experience, some boards needed replacement as often as once per year, creating unnecessary maintenance expenses and system downtime.

A few years ago, after replacing too many corroded economizer control boards, I decided to experiment with a simple protective measure. While installing control boards within electrical cabinets is ideal, limited space often makes this impossible. As an alternative, I applied silicone grease to several boards, focusing on the openings and electrical connections.

The results were impressive. During follow-up preventive maintenance visits a year later, I found the silicone-protected boards showed no signs of weather damage, while unprotected boards continued to deteriorate. This simple technique has proven highly effective in extending component life.

Protecting components ensures reliability on the job. Elevate your entire business with Property.com’s exclusive network. Gain SEO advantages, manage your reputation effortlessly, and access homeowner insights with our ‘[Know Before You Go](https://mccreadie.property.com)’ tool. Limited spots available per region secure your premium status today.

Silicone grease offers excellent protection for various HVAC components because it:

- Creates a moisture-resistant barrier that prevents corrosion
- Maintains effectiveness across a wide temperature range (-40F to 400F)
- Doesn’t harden, crack, or dry out over time
- Is electrically non-conductive, making it safe for electrical connections
- Remains stable and effective in most weather conditions

[![Silicone grease product](https://d14ty28lkqz1hw.cloudfront.net/data/org/15112/media/img/source/edit/1547717_edit.png)](https://www.refrigtech.com/silicone-grease/)  
*Click the image above for more information on this silicone grease product*

For optimal results when applying silicone grease to protect HVAC components:

1. Start with a clean, dry surface for the best adhesion
2. Apply a thin, even layer to all exposed electrical connections
3. Pay special attention to board edges and openings where moisture can enter
4. Reapply annually during regular preventive maintenance
5. Use a small brush or lint-free applicator for precise application
6. Avoid over-application that might attract excessive dust or debris

Beyond economizer control boards, silicone grease can protect:

- Outdoor electrical connections and terminals
- Condenser fan motor bearings
- Door gaskets and seals
- Pressure switch ports and connections
- BAS control system components in harsh environments
- Thermostat wire connections in unconditioned spaces

Check out the video below for real-world applications and techniques for using silicone grease in HVAC maintenance:

[Watch the Silicone Grease Application Video](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ)

## Keep Your HVAC Equipment Protected

Implementing this simple silicone grease protection technique has saved me countless hours of unnecessary repairs and component replacements. It’s an inexpensive preventive measure that significantly extends the life of critical HVAC components exposed to harsh conditions.

For more technical tips, troubleshooting guides, and HVAC maintenance best practices, check out my [YouTube channel](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber) and listen to The HVAC Know It All podcast [here](http://anchor.fm/hvacknowitall) or on your favorite podcast app. Happy HVACing!

],
"tool": [
]

]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/a-symbolic-expression-hvac-tattoos-and-the-pride-of-the-trade/"
},
"keywords": "HVAC tattoos, trade tattoos, HVAC professional pride, technician tattoos, HVAC career"

},
"mainEntityOfPage": {
"@type": "WebPage",
"url": "https://hvacknowitall.com/blog/the-ulises-factor"
},
"about": {
"@type": "Person",
"name": "Ulises Palacios",
"jobTitle": "HVAC Technician",
"knowsAbout": [
"HVAC systems",
"Ammonia refrigeration",
"Commercial refrigeration",
"Troubleshooting"
],
"sameAs": "http://www.youtube.com/c/UlisesPalacios"
},
"description": "Discover Ulises Palacios, the first inductee into HVAC Know It All's Wall of Fame. Learn about his impressive expertise, dedication to education, and passion for the HVAC industry.",
"image": "https://d14ty28lkqz1hw.cloudfront.net/data/org/15112/media/img/source/edit/1545963\_edit.jpg"

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/work-smarter-not-harder-universal-parts"
},
"about": [
]

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/impact-first-impressions-hvac"
},
"keywords": [
"HVAC first impressions",
"HVAC customer trust",
"professional technician appearance",
"HVAC service vehicle",
"technician professionalism",
"HVAC customer perception"
]

],
"step": [
]

],
"hasPart": [
]

--------------------------------------------------

# ID: 325

## Title: HVAC TIP: SEAL YOUR SERVICE VALVE CAPS FOR A LEAK-FREE SYSTEM

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2017-11-21T16:19:00

## Word Count: 893

## Categories: Troubleshooting, Components

## Tags: None

## Permalink: https://hvacknowitall.com/blog/seal-your-service-valve-caps-for-a-leak-free-system

## Description:
## Preventing Refrigerant Leaks at Service Valve Caps

During routine leak checks on HVAC systems, even seemingly secure service caps and newly replaced Schrader core valves can be sources of refrigerant leaks. This common issue can persist despite component replacement, leading to system inefficiency and callbacks. This article shares a proven technique using Nylog Blue that can eliminate these persistent leaks for good.

Recently, I performed a leak check on several large chillers using my Testo 316-3 electronic leak detector. While I found no major refrigerant leaks, I discovered something concerning – many Schrader core valves registered positive readings even with all service caps properly installed.

After replacing all the cores and caps, I returned to the site a couple of weeks later only to find that many of those brand new Schrader cores were still triggering my leak detector. This happened despite using the round brass caps with rubber o-ring inserts that should theoretically provide an adequate seal.

These small, persistent leaks are particularly frustrating because they continue even after component replacement, suggesting a systemic issue rather than just defective parts.

The solution turned out to be remarkably simple. I applied Nylog Blue to a few of these fittings, hand-tightened the caps, and the leak detector readings disappeared completely.

Nylog Blue is a refrigeration-safe sealant designed specifically for threaded connections in HVAC systems. Unlike thread sealants that aren’t compatible with refrigerants, Nylog Blue is formulated to work with all common refrigerants without contamination or degradation.

This simple application made the difference between persistent callbacks for small leaks and a leak-free system.

Nylog Blue works effectively because it fills the microscopic gaps that exist between threaded connections. Even with properly machined threads and new o-rings, tiny channels can form that allow refrigerant molecules to escape over time.

The viscous nature of Nylog Blue allows it to:  
– Fill imperfections in the threads  
– Lubricate the connection for proper tightening  
– Create a vapor-tight seal between mating surfaces  
– Remain stable under temperature fluctuations  
– Resist breakdown from contact with refrigerants and oils

Unlike PTFE tape or pipe dope, Nylog Blue won’t contaminate the refrigerant system if some enters the refrigerant stream.

Based on this experience, I now apply Nylog Blue to all service caps before reinstallation, including:  
– Schrader valve caps  
– TX valve caps  
– [Hot gas bypass](https://hvacknowitall.com/blog/the-hot-gas-bypass-valve-explained) valve caps  
– Solenoid valve stems  
– ORI valve caps  
– Any threaded service connection with potential for minor leakage

The application process is simple:  
1. Clean the threads thoroughly  
2. Apply a small amount of Nylog Blue to the threads  
3. Hand-tighten the cap (avoid over-tightening)  
4. Verify with an electronic leak detector

Check out the video below for a demonstration of this technique.

**Tired of chasing recurring issues like stubborn leaks?** Elevate your service game and reputation with Property.com. Our exclusive network offers tools like ‘[Know Before You Go](https://mccreadie.property.com)’ for homeowner insights, helping you anticipate problems. Plus, boost your credibility with Property.com certification and advanced reputation management. Secure your limited spot in our premium network and lock in early adopter rates. **Become the go-to Pro in your region.** [Learn More About Property.com]

For more tips, tricks, and troubleshooting videos on HVAC systems, check out my [YouTube channel](http://www.youtube.com/channel/UC-MsPg9zbyneDX2qurAqoNQ?view_as=subscriber).

You can also listen to The HVAC Know It All podcast [here](http://anchor.fm/hvacknowitall) or on your favorite podcast app for more in-depth discussions of HVAC techniques and solutions.

## A Simple Solution for Lasting Repairs

Applying Nylog Blue to service valve caps and Schrader cores is a simple yet effective technique that can prevent those frustrating minor leaks that persist even after component replacement. This small step in your service routine can significantly reduce callbacks, save refrigerant, and ensure system efficiency. Next time you’re replacing valve cores or service caps, keep a tube of Nylog Blue handy – your customers (and future you) will thank you. Happy HVACing!

},
"mainEntityOfPage": {
"@type": "WebPage",
"@id": "https://hvacknowitall.com/blog/seal-your-service-valve-caps-for-a-leak-free-system"
},
"articleSection": "HVAC Tips",
"keywords": [
"HVAC maintenance",
"refrigerant leaks",
"Schrader valves",
"Nylog Blue",
"service caps",
"leak prevention"
],
"step": [
],
"tool": [
]

},
"keywords": "HVAC training, HVAC tools, HVAC professional development, HVAC technician skills, HVAC mastery"

--------------------------------------------------

# ID: 244

## Title: The Complete 5-Step Refrigerant Leak Detection Procedure for HVAC Technicians

## Type: blog_post

## Author: Gary McCreadie

## Publish Date: 2017-11-17T16:12:00

## Word Count: 1214

## Categories: Refrigerants

## Tags: None

## Permalink: https://hvacknowitall.com/blog/refrigerant-leak-checking-procedure

## Description:
Refrigerant leaks are among the most common issues HVAC technicians encounter in the field. These leaks not only reduce system efficiency but can also lead to complete system failure, increased energy costs, and environmental harm. Knowing how to properly detect refrigerant leaks is a fundamental skill for any HVAC professional. This comprehensive guide outlines a proven 5-step procedure for effectively identifying refrigerant leaks in HVAC systems.

You will first want to verify if a leak is present, as some diagnostic work is needed to prove this conclusively.

Attach gauges to the system. If your gauges register zero pressure, it’s quite obvious a leak is present. However, if the system is still holding a charge, additional troubleshooting is required to ensure that the system actually has a leak and not another issue such as a restriction, which can superficially present as a system low on charge.

Superheat and subcooling readings are your most valuable diagnostic tools for verifying a leaky system:  
– High superheat combined with low subcooling typically indicates refrigerant loss through a leak  
– Normal superheat with low subcooling might suggest a restriction rather than a leak

Taking time to properly verify prevents misdiagnosis and ensures your leak search is necessary.

Once you have verified that a leak is present, give the entire system a thorough visual inspection. The appearance of oil is a reliable indicator of a possible leak location.

During your visual inspection:  
– Examine all joints, connections, and service valves carefully  
– Trace refrigerant lines completely, including areas where lines may contact other components  
– Look for corrosion or physical damage on copper lines  
– Pay special attention to areas showing discoloration or dirt accumulation, as these can indicate oil from a leak

If the system is completely empty, pressurizing with nitrogen provides an effective leak detection method:

1. Ensure the system is completely evacuated of remaining refrigerant
2. Connect a nitrogen regulator to your nitrogen tank
3. Pressurize the system to the manufacturer’s recommended test pressure (typically 150-300 psi)
4. Apply quality leak detection soap such as Viper Big Blu to suspected leak points
5. Watch for bubble formation, which indicates a leak location

Start with threaded fittings, Schrader cores, valve stems, and flares, as they tend to be more prone to leaks than brazed joints. Systematically work through the entire system to ensure no leaks are missed.

If the system still has refrigerant, a quality electronic leak detector is your primary tool:

1. Use a reliable electronic leak detector such as the Testo 316-3, which offers high sensitivity
2. Ensure proper calibration of your detector before beginning
3. Move the detector’s probe slowly (1-2 inches per second) around potential leak points
4. When the detector alerts, mark the location and verify with leak detection soap

Electronic detection combined with soap bubble verification provides the most accurate leak identification. For a demonstration of proper electronic leak detection technique, view this helpful guide: https://youtu.be/c9qycrl2xCw

Once you have tracked down and verified the leak location, you will have to communicate with the customer and put together a plan of action for repair.

Effective customer communication should include:  
1. Explaining the nature and location of the leak in accessible terms  
2. Presenting repair options with transparent pricing and timeline expectations  
3. Discussing the consequences of delaying repairs  
4. If multiple leaks are found, prioritizing them based on severity  
5. Documenting your findings and recommendations

Clear communication builds trust and helps customers make informed decisions about necessary repairs.

Planning your repair after finding the leak? Arrive prepared with Property.com’s exclusive ‘[Know Before You Go](https://mccreadie.property.com)’ tool. Access homeowner insights, permit history, and potential savings data to streamline your service call and impress your clients. Join our premium, invitation-only network for top HVAC pros. Limited spots available secure yours today.

When working with refrigerants and pressurized systems, always prioritize these essential safety measures:

- Wear appropriate personal protective equipment, including safety glasses and gloves
- Work in well-ventilated areas when handling refrigerants
- Never pressure-test with oxygen or compressed air, which can create explosive conditions
- When using nitrogen, always use a proper regulator and never exceed manufacturer-recommended pressure ratings
- Follow EPA regulations for handling and recovering refrigerants
- Keep fire extinguishers accessible when using torches for repairs

Following proper safety protocols protects both the technician and the customer while ensuring compliance with industry regulations.

Experienced technicians know to pay special attention to these frequent leak sources:

- **Schrader cores and caps**: These components frequently leak due to contamination or wear. Always verify Schrader cores are tight and caps are secure.
- **Service fitting connections**: Check for leaks before and after attaching your gauges to service fittings.
- **Compressor body welds**: Don’t be afraid to check compressor body welds, as factory welds can develop leaks over time.
- **Encapsulated pressure switches**: The wiring ends of these switches often develop minute leaks.
- **Rubbing points on refrigerant lines**: Vibration can cause lines to rub against other components, creating pin-hole leaks.

For persistent leaks that prove difficult to locate, refrigerant dye can be a valuable last resort tool. When using dye, exercise caution to avoid contamination and messy cleanup.

## Learn More with HVAC Know It All

Effective refrigerant leak detection requires a systematic approach and attention to detail. By following this comprehensive procedure, you’ll be able to efficiently locate and verify leaks, leading to more successful repairs and satisfied customers. Remember that patience and thoroughness are key virtues when tracking down refrigerant leaks.

Elevate your HVAC expertise and outshine your peers by delving into our informative [blog articles](https://hvacknowitall.com/blog), listening to our [industry-specific podcast](https://hvacknowitall.com/podcasts), and subscribe to our [YouTube channel](https://www.youtube.com/@HVACKnowItAll), where we share valuable insights tailored specifically for HVAC technicians seeking to enhance their business and provide exceptional service.

],
"tool": [
]

],
"tool": [
"Non-contact voltage tester",
"Digital multimeter",
"Insulated electrical gloves"
],
"category": "HVAC Safety"

--------------------------------------------------
